EAp2 requires that 50% (by power rating) of new equipment and appliances purchase for the LEED-CI scope of work be Energy Star labeled. Projects that go beyond the 50% requirement can achieve up to four additional points under EAc1.4 by specifying 70%, 77%, 84%, or 90% Energy Star equipment.
Completing the rated powerRated power is the nameplate power on a piece of equipment. It represents the capacity of the unit and is the maximum that it will draw. listing for each appliance and piece of equipment is the most time-consuming part of this credit. The LEED documentation requires not just checking a box to confirm that equipment is Energy Star; you will also need to assign a rated power to each model of appliance, computer, monitors, etc., which sometimes requires pulling the specification sheet or looking on the device’s nameplate.
In the past GBCI has allowed a shortcut: you could use standard rated power values from Table 2 in the LEED Reference Guide, but LEEDuser has found that this is no longer allowed.
Rated power is not the amount of power a piece of equipment will actually use, but simply the “nameplate power.” It represents the capacity of the unit and is the maximum that it will draw. The actual power used by equipment or appliances is often less than half the rated power. Rated power is what you have to use for the calculations for this credit.
Calculations for achieving this credit have to include all of the following, provided they are available in an Energy Star labeled model and are in your project's scope of work to purchase or install new:
If an entire product type is not Energy Star labeled, that equipment is excluded from your calculations. Conversely, equipment outside the four categories that is Energy Star labeled must be included in your calculations. HVAC, lighting, and building envelope products are excluded from calculations for this credit.
Any categories added to the Energy Star list as the program grows may be used in the project team’s calculation. You can check out the Energy Star website for updates to product categories.
When LEED 2009 was released in June 2009, the LEED Reference Guide described this credit as referring to all equipment used on the project, whether new or existing. However, as clarified in the April 2010 LEED addenda from USGBC, the credit is only applicable to equipment installed or purchased new for the scope of work covered by the LEED-CI project. This clarification, which also applies to EAp2 means that project teams have neither an incentive or a disincentive to replace older equipment. Teams may choose to purchase newer, more efficient equipment, or preserve older equipment that still has useful life.
Projects still may include used equipment in their credit documentation, but if they do, they must include all the older equipment being used, not just some of it.
For all questions related to qualifying Energy Star equipment, please refer to the Energy Star website products section.
Details for each qualifying product are given in specifications on the Energy Star website under each product category. If your equipment type is not eligible for Energy Star, you should be able to exclude it from your calculations. However, make sure the product type is actually not eligible if you are excluding it from the calculations. If there just aren’t enough models on the market yet, but the product is eligible, you have to include it in your calculations.
First identify which appliances and equipment are eligible for an Energy Star rating in your project. Check the Energy Star website for up-to-date listings of products and appliances that are available as Energy Star-labeled and create a project-specific list of these items. At minimum, the equipment list will include office equipment such as computers, fax machines, printers, scanners, multi-function devices, and monitors, as well as appliances such as refrigerators, dishwashers, washers and dryers, etc. (See the LEED Reference Guide EAc1.4, Table 2 for the minimum category of appliances to be included.)
Your list has to include only equipment that is installed new or purchased within the LEED-CI project scope; existing equipment may be excluded (note that this is a change from the original 2009 release of the rating system—see the Bird's Eye View for more detail).
HVAC, lighting, and building envelope products are excluded from calculations for this credit.
There are new equipment types earning the Energy Star label on a regular basis. Any equipment type that fits into the LEED categories for equipment addressed by the credit should be included in credit calculations.
Be sure to refer to the Energy Star website on a regular basis as the website is updated several times a year.
Add the rated power of all equipment and the rated power of Energy Star labeled equipment for your project to your equipment list. The rated power is usually imprinted on the equipment (in watts or kilowatts, i.e., kW) or you can use the standard values in the LEED Reference Guide, EAc1.4 Table 2 for equipment and appliances listed there.
The rated power can also be derived from listed ratings in volts and amps, which you multiply to obtain watts. Use the equation Watts = Amps x Volts.
Sum the two columns and calculate the percentage of rated power that comes from Energy Star labeled equipment. It has to be at least 50% of total project equipment rated power to achieve the prerequisite, and 70%, 77%, 84%, and 90% for 1-4 points.
If an Energy Star product is purchased as a replacement for older, less efficient equipment, you can assign it the higher rated power of the original product for the purposes of your calculation. Doing that gives these replacement products more weight in the calculations. The replacement must be purchased between project registration and when the project is submitted for certification.
Identify and prioritize the equipment with the highest rated power, because those are the items that will help you most. Your credit calculations will be based on the rated power of the equipment, not the number of individual Energy Star labeled machines. For example, the rated power of a copier is much higher than a laptop. If you buy only one of each, an Energy Star labeled copier will contribute more to the overall Energy Star labeled power percentage.
Performing your calculations early on will tell you if the project owner needs to specify more Energy Star labeled equipment for the new spaces.
In most product categories there is a wide range of Energy Star labeled products to choose from. Energy Star sets a minimum performance level, but some options are more efficient than others. As much as possible, choose the most efficient equipment. If doing that means getting equipment with a lower power rating, use the power rating from the LEED Reference Guide or from older equipment you are replacing to avoid being penalized in the credit calculation.
If used equipment was labeled Energy Star at the time it was purchased, but is not in the current list anymore, it can be listed as an Energy Star product. However, all new products purchased at the time of construction should be Energy Star labeled.
Most Energy Star office computers and equipment carry little or no cost premium, and bring operational cost savings.
Involve the facilities manager, operations personnel or procurement staff in conversations about energy-efficient equipment. They should be able to provide a list of specified and existing equipment to help with your calculations.
You can get a bonus by claiming the original power consumption of the piece of equipment that is being upgraded to more efficient Energy Star equipment.
It is no longer required to track existing reused equipment. Refer to the following LEED Addendum posted on 4/16/10. “Only new appliances and equipment purchased as part of the scope of work for the project need to be included in the credit for EA Credit 1.4. Equipment and appliances must meet the Energy Star criteria current at the time of purchase. Any items that are purchased after the item's category has become ENERGY STAR eligible must meet the Energy Star rating. Any items already covered by the ENERGY STAR program that are purchased after new criteria have been issued must meet the new criteria. Items purchased before the category is ENERGY STAR eligible do not need to meet the ENERGY STAR rating; similarly, items purchased before new criteria are issued do not need to meet the new criteria.”
Energy Star labels are not permanent, and Energy Star criteria get stricter over time. If your piece of equipment no longer has an Energy Star label, but you can prove that it did when you bought it, you can still count it.
Make sure to update your Energy Star list with all known appliances and equipment included in the project, with associated rated power for each and indicate whether it is Energy Star labeled. Sum the rated power of your equipment list, including Energy Star labeled equipment.
Not all products need to be Energy Star labeled to get the credit, you just need to reach your chosen threshold of Energy Star labeled equipment for your project: 70%, 77%, 84%, or 90% for 1-4 points.
Check the Energy Star website to update your list of appliances and equipment that must be Energy Star labeled to make sure that all have been accounted for.
To meet the next point threshold, identify power-hungry appliances that are in need of replacement within the next year, like copiers, printers, and refrigerators and target them for replacement or efficiency upgrade before project completion.
Note that Energy Star rates the power usage of “sleep,” “standby,” and “hibernate” modes for computers, which may be lower than the computer’s power rating. Use the rated power for the active mode and be consistent in your documentation.
Establish an Energy Star purchasing policy for all future equipment. Although a purchasing policy is not required to earn this credit, it can help ensure that the project continues efforts to achieve cost-effective energy conservation.
Once the construction documents are complete, update your equipment list to track any changes and confirm that specified equipment is included in final construction documents.
Complete your documentation on LEED Online. List each piece of equipment, with its rated power, and indicate if it is Energy Star labeled. The calculator built in to LEED Online automatically sums up the eligible wattage to confirm compliance and points achieved. If you prefer, you can upload your list, as long as it is in spreadsheet form and calculates the Energy Star labeled power percentage properly.
Purchase new equipment and appliances that are Energy Star labeled, to the greatest extent possible.
See the Operations and Maintenance section of the Reference Guide or LEED-EBOM for guidance on continued purchasing and replacement of Energy Star equipment after initial project specification. Work this guidance into procurement policies for future purchases.
Excerpted from LEED 2009 for Commercial Interiors
To achieve increasing levels of energy conservation beyond the prerequisite standard to reduce environmental and economic impacts associated with excessive energy use.
For all ENERGY STAR® eligible equipment and appliances installed as part of the tenant’s scope of work, achieve one of the following percentages (by rated powerRated power is the nameplate power on a piece of equipment. It represents the capacity of the unit and is the maximum that it will draw.). Equipment that meets the same requirements as ENERGY STAR® qualified products but does not bear the ENERGY STAR® label is acceptable. Projects outside the U.S. may use a local equivalent to ENERGY STAR®.
This requirement applies to appliances, office equipment, electronics, and commercial food service equipment. Excluded are HVAC, lighting, and building envelope products.
Select energy-efficient equipment and appliances, as qualified by the EPA’s ENERGY STAR Program (http://www.energystar.gov).
This website lists all the equipment and appliances that are labeled Energy Star. Each category has a downloadable list of labeled products, updated every few months.
ENERGY STAR is a government-industry partnership managed by the U.S. Environmental Protection Agency and the U.S. Department of Energy. The program’s website offers energy management strategies, benchmarking software tools for buildings, product procurement guidelines, and lists of ENERGY STAR–qualified products and buildings.
This website links to EIA’s Commercial Building Energy Consumption Survey.
This ongoing project explores the effects of computers and other information technology on resource use.
To earn and document this credit, you'll need to track down product data, including rated powerRated power is the nameplate power on a piece of equipment. It represents the capacity of the unit and is the maximum that it will draw., from cut sheets like the example shown here. You can also use Energy Guide labels like the example given to confirm that a product has earned the Energy Star label, and confirm the rated power of the equipment or appliance.
Use this calculator to track and log the percentage of your project's equipment that qualifies for Energy Star. Note: this calculator lists typical equipment for an office and may a model, but not a suitable tool, for other project types.
Documentation for this credit can be part of a Design Phase submittal.
The following links take you to the public, informational versions of the dynamic LEED Online forms for each CI-2009 EA credit. You'll need to fill out the live versions of these forms on LEED
Online for each credit you hope to earn.
Version 4 forms (newest):
Version 3 forms:
These links are posted by LEEDuser with USGBC's permission. USGBC has certain usage restrictions for these forms; for more information, visit LEED Online and click "Sample Forms Download."
Complete documentation for achievement of EAc1.4 on a LEED-CI 2009 project.
It is of my best understanding that the UPSs are included as "eligible equipment" for both EAp2 and EAc1.4 as stated on the LEED for Commercial Interiors v2009 Reference Guide since they fall under the Office Equipment Category - Uninterruptible Power Supplies.
Our project's conditions demand several UPSs of 160KW and connected to a 480V rated output voltage. There are no UPSs certified ENERGY STAR in the market, based on the following link:
We are analyzing different alternatives to find other UPS equiment that meet the requirement (reducing the Wattage on the equipment, thus adding the amount of units needed to satisfy the project's demands), but we were wondering if there is scope for a solution such as an excemption to the UPS certified equipment for the aforementioned conditions to meet the requirements of the EAp2 and EAc1.4
Thank you in advance for your help.
Our view is that UPS' are not included under this credit. Unless this has been superseeded the LEED-CI ACP Supplementary Guide (LEED Ref_IDC_ACP_0.pdf) there is a table which lists the Energy Star categories, excluding UPS systems.
Logically EAc1.4 seeks to reduce internal heat gains from user equipment. Your 160 kW UPS is likely to be 95%+ efficient, meaning less than 5% or 8 kW is heat load when the UPS is operating at full load.
If LEED wants to include UPS systems it would need to be based on power conversion loss 8kW not on power throughput 160 kW, else W/ft2 would be several multiples of the typical office power figures(see CI Guide p179).
Thank you for your rapid response. We have found this LEED InterpretationLEED Interpretations are official answers to technical inquiries about implementing LEED on a project. They help people understand how their projects can meet LEED requirements and provide clarity on existing options. LEED Interpretations are to be used by any project certifying under an applicable rating system. All project teams are required to adhere to all LEED Interpretations posted before their registration date. This also applies to other addenda. Adherence to rulings posted after a project registers is optional, but strongly encouraged. LEED Interpretations are published in a searchable database at usgbc.org. (10044) at usgbg.org Data Base:
Equipment that is not classified by Energy Star does not need to be included in the calculation; however, equipment that is classified by Energy Star, but an Energy Star certified version was not chosen, should be included in the calculation as non-Energy Star. Applicable internationally.
Since UPSs are considered under the "Office Equipment" category of ENERGY STAR products and based on previous LEED CI projects we have worked with, UPS were accepted as ENERGY STAR eligible equipment.
In addition, I just checked that Marcus Sheffer posted this answer to a related question on this very same web page:
"UPS falls under office equipment within Energy Star and the Reference Guide and Rating System documents clearly state that all Energy Star eligible equipment is included within EAp2 and EAc1.4."
We have already found equipment with the Watts and Volts that we need that meet the ENERGY STAR criteria, but I just want to make sure I need to include it on the list. Ours is a very large project and the reviewer may notice that a UPS is included and may ask for its addition on the template of this credit.
Thank you in advance for your help!
Good you find the solution.
Whilst USGBC/GBCI rules on any interpretations, we find it illogical to include the UPS nameplate power rating in the counting towards EAp2/EAc1.4 compliance.
A large UPS complying with Energy Star 'swamps' all other equipment in the project so you probably get most of the points!
For illustration, a 160 kW UPS supplying 150 kW of Energy Star listed equipment, but which is not complying with ES, fulfills the 50% requirement, yet only accounts for less than 5% of the total equipment load. If the UPS is excluded, or only the rated losses are included, then it is necessary that the connected equipment complies to meet at least 80 kW of total load. QED?
I agree John. The rated powerRated power is the nameplate power on a piece of equipment. It represents the capacity of the unit and is the maximum that it will draw. for a UPS includes all of the stuff attached to it. I am not sure on how to break out just the power used by the UPS. Anyone have any thoughts?
Hi Marcus. Looking at Energy Star's 'UPS Key Product Criteria' it could be the 'average loading-adjusted efficiency' (which is based on 25 to 100% load profiles), which accounts for UPS performance at part load, but is dependent on the type of UPS. If 95% efficient then 5% of the power rating is included in the calculation.
We feel it is for USGBC/GBCI to rule on this so that projects do not either exclude the UPS from the calculation or achieve compliance based on the nameplate rating.
For one of our overseas project we needed appliances that were 50 Hz; 220-240V. We did not find any Energy Star Products for this specific voltage but made sure that we use “A” energy rated products. Is there any documentation that I can submit to earn this credit?
I think that there has been a number of posts in the forum related to demonstrating equivalency between Energy Star and other standards, you should attempt to do so. Focus on energy use.
You didn't say which appliance categorty, but....IF it is commercial kitchen equipment, most manufacturers will have 50 cycle spec sheets available. Those, combined with the LEED Prescriptive information on Fisher Nickel's website which has the standards per appliance, should help. This page would have the most up to date Energy Star Standard information. There are a few recent categories and some updates.
Thanks Marcus & Suzanne.
Also, Suzanne do microwaves have a similar rating; did not find it.
We are busy with a fitness centre project and looking to confirm which appliances/equipment we typically would have to include in this credit.
Standard and necessary equipment - in addition to some office equipment - is gym equipment (treadmills etc) and hair-dryers and similar appliances that are owned and supplied by the fitness centre.
Would anyone have experience on a project of this nature and can assist which equipment we will typically have to include?
No, fitness equipment is not eligible for Energy Star rating, neither are hair dryers. Vending machines however are eligible. The best place to look is the energystar.gov website where you can see the categories of appliances that are eligible.
We are sourcing local equivalent of Energy-Star qualified products in Hong Kong and have found most products are certified by HK Energy Label. Could anyone please tell me what the mechanism is to prove 'HK Energy Label' is the local equivalent of 'Energy-Star label'? Was it that if a certain product with HK Energy Label fulfills all the requirements in the corresponding Energy-Star qualified product type, such product can be considered as local equivalent of E/S qualified product?
However, if it is on a product-by-product basis, it will be complicated and time-consuming to compare every product with E/S requirements. Is there any quick ways to do so like 'HK Energy Label Grade 1' = 'Energy Star rated'?
Unless USGBC or GBCI have provided further information there is no blanket equivalance for HK Energy Label v ES Label. The LEED REFERENCE GUIDE FOR GREEN INTERIOR DESIGN AND CONSTRUCTION WITH GLOBAL ALTERNATIVE COMPLIANCE PATHS 2009 p30 provides guidance on demonstrating equivalence, on a appliance basis. So no quick way only to compare ES appliance and HK EL appliance labels.
You can obtain the ES calculation method and HK EL calculation method from the respective websites.
Fridge-freezers are fairly easy to compare but I have not had the need to compare for other appliances.
See Fishnick.com for the prescriptive measures listing and it may yield standards that match up with the standards for HK, particularly if the ASTMVoluntary standards development organization which creates source technical standards for materials, products, systems, and services test methods used are the same. Link below may help because you can compare these baselines/prescriptive measures to manufacturer specifications for your HK EL products. This was the basis for the listing in the reference guide. www.fishnick.com/.../LEED_suggested_baselines_and_presriptive_measures _FSTC_2011_06_03.xlsx
This link may also have what you are looking for. http://www.itc.gov.hk/en/quality/hkas/about.htm, because there are links to standards, which hopefully are for the products you seek.
Thank you for your advice! Now I can confirm with my client that there is no quick way to compare ES appliance and HK EL appliance labels. We might have to consider the cost benefit of continuously pursuing on this credit.
Thank you again for your great help!
Thank you for your advice! The integrated information in the excel will definitely save me a lot of time! We will proceed to compare HK EL products and the standards in the prescriptive measures list right away.
Thank you again for your kindly help!
I think the fishnick link is broken. I am getting a File not Found error. Could you please send it again?
To reach the Prescriptive Measures file, www.fishnick.com. In the search bar on the upper right, type in "prescriptive" and it will take you directly to the download. Glad to help!
In order to compare an appliance that is not ENERGY STAR and to prove it is as efficient as ENERGY STAR appliances, do we compare its rated powerRated power is the nameplate power on a piece of equipment. It represents the capacity of the unit and is the maximum that it will draw. to the ones listed under the 'Prescriptive efficiency' column in the spreadsheet?
Is equipment that is powered by gas (such as gas cookers, fryers, ovens) to be included in the list as well or should we just include electrical equipment?
Yes, there is such a thing as gas-powered equipment that is also Energy Star. Please feel free to use this link which will take you to a really great spreadsheet that shows all of the baselines/prescriptives as well as what the basis of the standard is. I never leave home without it. And don't forget to consider induction (ranges) as an alternative to gas because then, you have the added bonus of lower cfm requirement & less energy usage for make up air.
We are working on an office project outside the US and recommending the client install desk lamps as task lighting to increase controllability of lighting and reduce ceiling lighting energy loads. It is mentioned that lighting is not generally included in the energy star calculations but we're wondering if desk lamps are considered plug loads and be should included in the energy star office appliance percentage?
Also does anyone know how to go about proving equivalency between an international energy efficiency system, such as the Hong Kong energy efficiency label, and Energy Star certification?
Task lights are lighting and not included in the ES calculations.
I think equivalency at the project level would have to be demonstrated on a product by product basis not necessarily for the entire program.
EPA has an international list of their recognized international bodies. It can be accessed here. Good luck!
Hi Marcus/Suzanne, thank you so much for your helpful advice which has done a great help to my project!
We are going to purchase a new Energy Star-Labeled TV for the office. We can find TVs available as Energy Star-qualified in the categories shown in the Energy Star website. However, the Energy Star program of Japan only approves the equipment related to PCs such as computers, monitors, printers and like that. It seems that TVs are outside the scope of the target products in Japan.
We are not sure whether or not we can include it in the calculation under such conditions. Even if choosing to purchase a Energy Star one, are we not able to earn points under EAc1.4 (as well as EAp2), not complying with the local regulation?
Thank you in advance.
Good question. While I'm a commercial kitchen equipment person not TV, the way I've seen it work is regardless of whether E/S is recognized or to what degree, in another country, the 'intent' is to meet or exceed the Energy Star published baselines for the appliance. The E/S standards do have power consumption limits based on various modes of operation, so it seems to me that a TV that meets/exceeds should count in the rated powerRated power is the nameplate power on a piece of equipment. It represents the capacity of the unit and is the maximum that it will draw. calcs. Here is a link to the Version 6.0 DRAFT version, and underneath info on Ver. 4 & 5. Noticed that there is also a "most efficient" distinction coming around too. Hope it helps.
Thank you very much for giving us helpful advice. I am sorry if my understanding is wrong, but is it acceptable to choose energy efficient products (not Energy Star labeled ones) as long as they meet or exceed the Energy Star published baselines and prove to be equivalent to the baselines or more?
Thank you in advance again.
I have two questions regarding the inclusion of UPS in the 'Energy Star' calculation for EAc1.4 in LEED v2009.
Q1. To Include UPS or not for Energy Star calculation?
I understand that ENERGY STAR rated appliances purchased prior to the publication of the current ‘criteria’ and complying with the previous criteria can meet the intent and requirements of LEED-CI EAc1.4… and that all equipment purchased after the new ‘criteria’ have been issued need to meet the new specification.
For example, Refrigerator was a ‘category’ in Energy Star when LEEDv2009 was released… and new ‘criteria’ has been published in Energy Star.
However, my question is regarding the language on p180 that states… "Any new ‘categories’ added to the Energy Star list in future may (not MUST) be used in the project team’s calculation’.
Since UPS was NOT a ‘category’ listed in Energy Star when LEEDv2009 was released... I would assume that the project team can choose to include the UPS or not based on the guidance given in the sentence above.
Is that correct?
Note, we've NOT included UPS in recent submissions and have never been queried in the Review!?
Q2. What is the ‘Rated Power’ for a UPS?
Notwithstanding the above... IF it is required to include the UPS in the Energy Star calculation... then what is the correct 'Rated Power' for inclusion in the LEED Online table?
The UPS mostly stands idle... but (potentially) has a huge 'Output Rated Power' say 200,000 Watts for a short period of time from the battery back-up power… while the maximum power drawn by the UPS is a much lower number... say 2,000 Watts!
My understanding is that we would use the maximum 'draw power' of the UPS rather than the maximum 'power output' of the UPS for input to the Energy Star calculation.
Is that correct?
Thanks in advance... Any advice is much appreciated.
Q1: I think that "category" is not referring to a specific product. UPS is a product under the Office Equipment category so I do not think the sentence you quote applies. The Reference Guide clearly states on page 180 as well that "The credit applies to all installed equipment and appliances listed by the Energy Star program."
In these situations the general practice is to require project teams to follow the guidance in place when the project was registered. So if your project was registered before this product was included in ES then I would say you do not have to include it. Also note that previous reviews do not establish precedence.
Q2: That would make sense to me.
Are CPU's also need to qualify Energy Star rating? In my case, monitors have Energy Star label.
Yes computers are Energy Star rated.
Hi Marcus, in your above response, by computers do you mean monitors and CPUs have to separately Energy Star rated?
Yes they are rated separately.
Do domestic hot water heaters fall into this category? They aren't listed in the reference manual, nor can I find mention of them on this site. Energy Star does have a bunch of rated models, but only for gas or propane. The few electric models they have rated are only 50 gallons or larger. Can hot water heaters be excluded from these calcs altogether, and furthermore do they belong in calcs for EAc1.3 instead?
This credit specifically excludes hot water heaters because they fall under "regulated," even though there is an Energy Star rating and most Energy Star appliances are 'process.' The key with Energy Star is not to look for the actual listing but the STANDARD, then compare the standard against what you are specifying. Does that help? Here's a link to the standard. http://www.energystar.gov/index.cfm?c=water_heat.pr_crit_water_heaters
If the answer is "yes, they are excluded," then yes, thank you!
I do see the distinction between regulated and process load in table 1, but it wasn't clear to me elsewhere in the section where the distinction was made, and the only CIRCredit Interpretation Ruling. Used by design team members experiencing difficulties in the application of a LEED prerequisite or credit to a project. Typically, difficulties arise when specific issues are not directly addressed by LEED information/guide I could find on the topic was from way back in 2009 before water heaters were even rated in Energy Star. Do you have a source for this answer? Thanks!
What is the difference between regulated loads within offices and unregulated process loads ?
Regulated loads are ones covered by 90.1 (envelope, lighting, motors, HVAC, hot water, etc.). Unregulated process loads are items not covered by 90.1.
Of note, under LEED V4, process loads have more impact in all tracks as opposed to only Retail/Hospitality/ID&C. Simplest way to help clients understand this is that the "process" is case-specific and normally doesn't run 24/7, like commercial cooking & warewashing equipment, as well as office equipment. But if the building was a frozen food warehouse, process loads would likely be the largest impact on the project. However, in the case of commercial ware washing, water usage of that piece can affect the (regulated) hot water heater sizing since it has to supply incoming water at usually 110 degrees & up. Here is a link to the specifics about hot water heaters and Energy Star standards.
Would anyone know if production lighting (for video conferencing spaces) would have to be included under this credit (EAc1.4 - OEP equipment and appliances)? Or should it be considered under the lighting credits? They would only be used sporadically.
Under the lighting credits. It's possible that this type of lighting would be exempt from the lighting power density calculations. See section 184.108.40.206 Interior Lighting Power in ASHRAE 90.1-2007.
Has anyone ever used local equivalents instead of the Energy Star rating?
ID#1492 states that we can use local equivalents.
The EU energy rating is the local standard here whereby equipments are rated by A++, A+, A, B, C ... How can we determine which rating would GBCI deem equivalent to Energy Star?
I don't know, but perhaps this might help: Energy Star aims to capture about 20% of the market in a certain product area. If more than 50% of the market starts to be compliant with Energy Star, the program raises the bar. Perhaps this rough benchmark of the Energy Star mission, along with specifications on specific equipment that you are looking at, could be helpful.
Hi, in relation to the point discussed above I have a query. We are doing a project in India and most of the products available there are BEE Star Rated, an energy efficiency rating standard implemented by the Indian government. Wanted to know how can BEE star rating be compared with the Energy Star rating and how to document these products?
I would create a table that contains the Energy Star, BEE Star and actual kWhA kilowatt-hour is a unit of work or energy, measured as 1 kilowatt (1,000 watts) of power expended for 1 hour. One kWh is equivalent to 3,412 Btu./year value for each applicable item to enable a comparison. I would also reach out to the BEE Star folks to see if they could help you with a comparison.
Consortium for Energy Efficiency has Energy Star & standards information. PLEASE keep in mind that for some products, PART of Energy Star pertains to water usage too, since you are paying to heat or cool water with some appliances. Therefore, you may find what you need here:
You didn't say what the product category is, but if it is commercial kitchen equipment, Kim Erickson is a wonderful resource there. Also if commercial kitchen equipment, go to fishnick.com and look for the .xls LEED Prescriptive Measures. Hope it helps.
We are choosing a dishwasher and a refrigerator for a project in Europe. This equipment uses the EU rating A,A+,etc.. According to the reply of Marc it is sufficient to compare kwhA kilowatt-hour is a unit of work or energy, measured as 1 kilowatt (1,000 watts) of power expended for 1 hour. One kWh is equivalent to 3,412 Btu./year, something we could do. But when I look at the ACPs it says a comparison is required using modified energy factor, water factor, product capacity, Energy Factor, Stanby Power, volume of water per cycle, energy use per year, Energy Efficiency ratio and Testing protocols. That seems a lot and not feasible. On the other hand in LEED V4, you need to compare the info that is on the Energy Star website. For refrigerators this is kwh/year. In the end we are not sure how to go about this. Anyone any experience with including the European certification to comply? Also, we have difficulty finding European models of refrigerators and dishwashers with Energy Star label since they only need to comply with the EU energy rating.
Some of these factors only apply to certain appliances so you would need to include them if it applies. For example the only ones that apply to a refrigerator are capacity (you would obviously not compare a very large one to a very small one) and energy use per year. So for a refrigerator and many other appliance all you really do is compare equivalent product's kWhA kilowatt-hour is a unit of work or energy, measured as 1 kilowatt (1,000 watts) of power expended for 1 hour. One kWh is equivalent to 3,412 Btu./year.
More of the factors you list apply to the dishwasher because it also uses water. Some of them only apply to HVAC equipment. Some only to water heaters. In the ACP they are not asking you to compare all of these for each appliance, just the ones that apply.
Thank you Marcus, that is very useful information. For the refrigerator we will compare size and kwhA kilowatt-hour is a unit of work or energy, measured as 1 kilowatt (1,000 watts) of power expended for 1 hour. One kWh is equivalent to 3,412 Btu./year which is also what the Energy Star website lists. Not sure if they will ask about the testing protocol to determine that consumption. I can imagine that the Energy Star testing protocol is not exactly the same as the European one. For the dishwasher we will look at energy and water consumption.
Dishwasher Energy Star Standards are based on IDLE energy plus water consumption per RACK, if a rack machine. NO E/S for flights. Sorting is done at the unload side for door/conveyor machines. Run time/day for permanent ware--take proposed #meals per peak meal period you are designing to, piece(dish) count per guest, and divide by 14, which will estimate #racks to be done. Don't forget trays and plate covers, plus utensils. A hospital would run a machine 10-12 hours/day and up, and casinos, 24 hours. Flatware (silverware) is 100 pieces/rack, run twice. Glassware is a toss up, as racks are made from 16-49 glasses. Then, divide (rated racks/hour x 70%) for the machine you've chosen by racks into total racks expected. Meiko is based in Germany and could potentially be of assistance. Machine will be idle during part of the dish run while workers scrap & load. At this time, booster heat is not considered in Energy Star, nor the credit. I have similar formulas for ice maker run time too. Good luck!
Hi, Would you clarify if routers and switches should be included in the list?
My understanding is no. The best place to check is on the Energy Star.gov website under Business and Commercial products. If you click on the category and then on the small hyperlink "For Partners" you get the definition document. Make sure you scroll all the way down to Item 2 to see what is excluded before you examine the Item 1 definitions. Sometimes lots is actually excluded.
Good morning Susan,
F.Y.I. The small network equipment category was added under the "For Your Home" tab with an effective date on September 3, 2013. The small network equipment category includes routers, switches and other equipment. I am not sure if this is applicable to commercial project but thought I would share what I found. See link below for additional information:
We are compiling the equipment for a multi-floor office renovation. Dow e need to include A/V Equipment? Including ceiling speakers, projectors, projection screens, microphones, etc?
We've done several projects with AV equipment. Per the Energy Star programming document for AV, the display elements are the focus of the eligible equipment, i.e., the monitors and TVs. And of course any CPUs that are running things.
Explicity excluded are projectors, battery powered portables, video conferencing, wireless microphones, and whole house audio or video and media servers.
Just a brief addition to Michelle's note- BKSK be sure the AV consultant/vendor is aware that the ENERGY STAR evaluation (and specs to include ENERGY STAR whenever possible) applies to the following in addition to displays (TV screens):
MP3 speaker docks
Blu-ray Disc players
Does anyone know what the rated powerRated power is the nameplate power on a piece of equipment. It represents the capacity of the unit and is the maximum that it will draw. is for vending machines?
Check out the Energy Star website to download the spreadsheet to find the model # and corresponding rated powerRated power is the nameplate power on a piece of equipment. It represents the capacity of the unit and is the maximum that it will draw.
A great spreadsheet to have on hand is this one, which is the LEED Prescriptive Baselines for water and energy because it shows qualifying equipment with standards other than Energy Star. As commercial kitchen equipment plays a more important role, it has gotten a lot bigger. LEED for Retail has an excerpt from this and Richard Young at Fisher Nickel is on the committee.
For context, the ENERGY STAR website indicates that this category currently only applies to new and rebuilt refrigerated beverage machines. So, exclude food/snack machines from your evaluation.
Generally the rated powerRated power is the nameplate power on a piece of equipment. It represents the capacity of the unit and is the maximum that it will draw. is considered the maximum electrical/energy "draw" an equipment item can use. You'll need to locate the specific vending machines data...either a cutsheet or perhaps webpage listing technical data- if the specified unit's wattage isn't listed, you can determine it using the following: (watts = amps x volts). Be sure the use the voltage specified for the electrical design....or you could use the highest allowable voltage configuration listed on the equipment cutsheet as a "worst case".
Where in the 2009 CI LEED reference guide does it state that only NEW Energy Star appliances are to be included in the calculations? I see you all note that new equpment only is what is supposed to be included in the paragraph above and in comments, but I seem to be missing it in the LEED reference guide.
For example ... I have a client who is relocating all of their printers, monitors, laptops and desktops. Therefore the only new equipment are appliances and TVs. So all I would include are the appliances and TVs?
Please confirm. I just want to make sure I am understanding correctly.
Yes, Energy Star only applies to "new" and "eligible" pieces of equipment. Relocated equipment is excluded, so yes only include TVs and appliances and makes sure you explain in Special Circumstances that the office equipment is relocated.
Look at the 4/16/2010 addendum to see where this is stated. It's very difficult to keep up with all the ever changing requirements. You'll need to watch quarterly addenda in addition to CIRs and on-line credit forms to capture all the nuances. Unfortunately, you cannot rely on the reference manual to contain everything anymore. It's a continuing lament.
Thank you so much! This is exaclty what I needed and was searching everywhere for. Looks like I need to catch up on my addenda ...
We run into this all the time with commercial kitchen equipment. Schools take very good care of their equipment, as an example, so there's potentially a lot of "existing, relocate'. But the consequences real world can be wicked if the actuals are far from the models. And they could be with dishwashers and ice makers because the water and energy has dropped so drastically. Utilities often give rebates on both so an energy audit factoring that in might be prudent. Then, use the template to calculate.
I hate to be dense but ours is a small office remodel, and there are only three pieces of equipment bought FOR the remodel a refrigerator, a TV, and a dishwasher all energy star compliant therefore we are 100% compliant four points! & an EP! - but that hardly seems right. What am I missing?
I say FOR the remodel, because it's been going on for a year and some new PC's have been bought that would have been needed anyway; I could include them I guess, but it doesn't change the strange total compliance.
Yes, it is what you buy, not what you use. But if I recall correctly, if the PC's used are within a year old, they count. Don't forget copiers, printers, monitors, routers, servers, various phone systems, & modems. Since smaller offices often use "residential" products, the "oh yeah" list can be found here, & USGBC statement below that, which is good since while there are Energy Star light strips, air conditioners, etc., they don't apply here. Hope it helps!
I am trying to determine if we need to include " No-break (UPS - Uninterruptible Power Supplies) " in our Energy Star documentation for this credit.
Hi Vitorio- Any luck on this?
I thought I recalled an GBCI issued addenda that stated new categories were to be included in the same general categories already required for evaluation (Office equipment, food service, etc) but cannot locate it....may be falsely remembering that. UPS and Enterprise servers are both new categories under "Computers" in the ENERGY STAR website, which is part of a broad classification of "Office Equipment" so I would expect they need to be included in LEED calcs. They can represent a LOT of wattage so best to catch them and ensure they are ENERGY STAR rated in the planning/specifications stages of a project.
Senior Sustainability Manager
EAp2 requires that 50% of the total eligible power rating be from Energy Star appliances. EAc1.4 grants points for going beyond 70%.
If a project is pursuing the energy modeling compliance path, then you can benefit from the reduced plug loads associated with Energy Star labeled products.
Do you know which LEED credits have the most LEED Interpretations and addenda, and which have none? The Missing Manual does. Check here first to see where you need to update yourself, and share the link with your team.
LEEDuser members get it free >
LEEDuser is produced by BuildingGreen, Inc., with YR&G authoring most of the original content. LEEDuser enjoys ongoing collaboration with USGBC. Read more about our team
Copyright 2014 – BuildingGreen, Inc.