USGBC's membership approved an update to LEED 2009 effective April 8, 2016. The update only affects LEED 2009 projects registered on or after that date.
Project teams will be required to earn a minimum of four points in EAc1, effectively making EAp2 more stringent. The referenced energy standard and modeling requirements are not changed. Buildings falling under the proposed change can use the same methodologies and referenced standards, but will need to earn additional points in order to achieve certification.
The intent of the change is to bring LEED 2009 energy requirements more up to date, as LEED 2009 continues to be the predominant LEED rating system, even though the more up-to-date LEED v4 has also become available.
This prerequisite is a big one, not only because it’s required for all projects, but also because it feeds directly into EAc1: Optimize Energy Performance, where about a fifth of the total available points in LEED are at stake. Master these minimum requirements, and you can use the same compliance path as in EAp2 to earning points.
You won’t earn the prerequisite by accident, though. Although “energy efficiency” is on everyone’s lips, the mandatory and performance-based requirements for EAp2 go beyond code compliance in most places. That said, there is nothing to stop you from meeting the requirements with a reasonable amount of effort, and the environmental benefits as well as the operational cost savings are significant.
Most projects start by choosing which of the three available compliance paths to follow. We’ll look at them each in turn.
Option 1 alone gives you access to all of the points available through EAc1, and offers the most flexibility in giving you credit for innovative designs.
First, you need to meet the mandatory requirements of ASHRAE 90.1-2007 for all major components, including the envelope, HVAC, lighting, and domestic hot water. ASHRAE 90.1 has had some changes and new mandatory requirements since the 2004 version, which was referenced on previous LEED systems, so be sure to review the standard carefully.
Energy efficiency is an area where it behooves project teams to start early and work together to maximize savings. Playing catch-up later on can be costly.Second, you need to demonstrate a 10% savings (5% for existing buildings) for your designed building compared with a baseline case meeting the minimum requirements of ASHRAE 90.1 (or Title 24-2005, Part 6 for California projects). You do this by creating a computer model following rules described in Appendix G of ASHRAE 90.1.
Computer modeling offers the following key advantages:
Your building type may not have a choice—you may have to follow this path, because both Options 2 and 3 are prescriptive compliance paths that are only available to specific building types and sizes.
However, if your building type and size allow, and you don’t want to embark on the complex process of computer modeling, which also requires expert assistance from a modeler or from a member of the mechanical engineer’s team, the prescriptive compliance paths are a good way to earn the prerequisite simply by following a checklist.
Passive design strategies such as shading to reduce solar heat gain are the most cost-effective ways to improve energy performance.Note, however, that when you get to EAc1, there are a lot fewer points on the table for the prescriptive paths, and that you have to follow each prescriptive requirement. These paths also require more collaboration and focus early on in design than you might think. The design team must work together to integrate all of the prescriptive requirements, and Option 3 even requires documentation of certain design processes.
The Advanced Energy Design Guides are published by ASHRAE for office, warehouse, and retail projects less than 20,000 ft2—so if you don’t fall into one of those categories, you’re not eligible for this path.
These guides outline strategies to reduce energy use by 30% from 2001 levels, or an amount equivalent to approximately 10%–14% reduction from ASHRAE 90.1-2007. If you choose this compliance path, become familiar with the list of prescriptive requirements and commit to meeting all of them.
The Core Performance Guide path is a good option if all of the following are true:
Comply with all requirements within Sections 1 and 2 of the guide. If you choose this path, become familiar with the list of prescriptive requirements and commit to meeting them. Also note that it’s not just a list of prescriptive requirements, but a prescribed process for achieving energy efficiency goals. You must demonstrate that you considered a couple of alternate designs, for example, and that certain team meetings were held.
Energy efficiency offers a clear combination of environmental benefit and benefit to the owner through reduced operational expenses, and potentially reduced first costs, if you’re able to reduce the size and complexity of your HVAC system with a more efficient envelope.
High-tech HVAC systems, and onsite renewable energy generation are often signature components of green buildings, but consider these strategies more “icing” on the cake, rather than a place to start. Start with building orientation and passive design features first. Also look at envelope design, such as energy-efficient windows, walls and roof, before looking at HVAC and plug loads. A poorly designed envelope with a high-tech HVAC system is not, on the whole, efficient or cost-effective.
Projects connected to district energy systems will not be able to utilize the system efficiencies of the base plant to demonstrate compliance with the prerequisite. They can plan on benefiting from these systems under EAc1, however.
Focusing on energy efficiency and renewable energy generation can seem to add costs to a project, but there are a variety of utility-provided, as well as state, and federal incentives available to offset those premiums. (See Resources.)
Ideally if the software you are using cannot model a technology directly then seek a published workaround related to your software. If you can't find a published workaround then model it as you think it should be modeled and explain how you have modeled it in the preliminary LEED submission.
No, not if it is part of the LEED project. However, there is an exemption for existing building envelopes in Appendix G that allow you to model the existing condition in the baseline so you do not pay a penalty.
No, not for an existing building.
You must model accurately. Since you don't have enough savings in the building energy, find savings in the process. Either you will be able to demonstrate that compared to a conventional baseline the process being installed into the factory is demonstrably better than "similar newly constructed facilities," allowing you to claim some savings, or the owner needs to install some energy-saving measures into the process to get the project the rest of the way there. Either option can be difficult, but not impossible.
Account for process load reductions through the exceptional calculation method. A baseline must be established based on standard practice for the process in your location. Any claim of energy savings needs a thorough narrative explaining the baseline and the strategy for energy savings along with an explanation of how the savings were calculated.
It is common to have a 80%–90% process load in a manufacturing facility. The 25% default in LEED is based on office buildings. If you think your load is lower than 25%, it is recommended that you explain why in a short narrative. It is also recommended to briefly explain it if your load is 25% exactly, since that level commonly reveals that the process loads were not accurately represented.
The energy savings are based on the whole building energy use—building and process. LEED does not stipulate exactly where they come from.
For LEED 2009 you'll need touse 90.1-2007. There were some significant changes in 90.1-2010—too many to account for in your LEED review, and your project would also have a much harder time demonstrating the same percentage energy savings.
Yes according to LEED, although it is not recommended as a best practice, and it is usually more cost-effective to invest in energy savings in the building.
You can assume exterior lighting savings for canopies against the baseline, but not the shading effects of canopies.
If exterior lighting is present on the project site, consider it as a constant in both energy model cases.
Any conditioned area must be included in the energy model.
The Energy Star portion of the form does not apply to international projects.
Use the tables and definitions provided in 90.1 Appendix B to determine an equivalent ASHRAE climate zone.
International projects are not required to enter a Target Finder score. Target Finder is based on U.S. energy use data.
For Section 18.104.22.168c, a manual control device would be sufficient to comply with mandatory provisions.
Submitting these forms is not common; however, it can be beneficial if you are applying for any exceptions.
Use the building area method.
Although there is no formal list of approved simulation tools, there are a few requirements per G2.2.1, including the ability of the program to provide hourly simulation for 8760 hours per year, and model ten or more thermal zones, which PHPP does not meet.
The automated Trace 700 report provides less information than is requested by the Section 1.4 tables spreadsheet. The Section 1.4 tables spreadsheet must be completed.
Assign HVAC systems as per Appendix-G and Section 6 but set thermostatic setpointsSetpoints are normal operating ranges for building systems and indoor environmental quality. When the building systems are outside of their normal operating range, action is taken by the building operator or automation system. out of range so that systems never turn on.
If it is only used for backup and not for regular use such as peak shaving—no.
SHGC is not a mandatory provision so it is available for trade-off and can be higher than the baseline.
You generally wouldn't need to upload any documentation, but particularly for a non-U.S. project, it may help to provide a short narrative about what they are based on.
Discuss your project’s energy performance objectives, along with how those are shaping design decisions, with the owner. Record energy targets in the Owners Project Requirements (OPR) for the commissioning credits EAp1 and EAc3.
You won’t earn this prerequisite by accident. The energy efficiency requirements here are typically much more stringent than local codes, so plan on giving it special attention with your team, including leadership from the owner.
Consider stating goals in terms of minimum efficiency levels and specific payback periods. For example: “Our goal is to exceed a 20% reduction from ASHRAE 90.1, with all efficiency measures having a payback period of 10 years or less.”
Develop a precedent for energy targets by conducting research on similar building types and using the EPA’s Target Finder program. (See Resources.)
For Option 1 only, you will need to comply with the mandatory requirements of ASHRAE 90.1-2007, to bring your project to the minimum level of performance. The ASHRAE 90.1-2007 User’s Manual is a great resource, with illustrated examples of solutions for meeting the requirements.
ASHRAE 90.1-2007 has some additional requirements compared with 2004. Read through the standard for a complete update. The following are some samples.
The prerequisite’s energy-reduction target of 10% is not common practice and is considered beyond code compliance.
Indirect sunlight delievered through clerestories like this helps reduce lighting loads as well as cooling loads. Photo – YRG Sustainability, Project – Cooper Union, New York A poorly designed envelope with a high-tech HVAC system is not, on the whole, efficient or cost-effective. Start with building orientation and passive design features first when looking for energy efficiency. Also look at envelope design, such as energy-efficient windows, walls and roof, before looking at HVAC and plug loads. HVAC may also be a good place to improve performance with more efficient equipment, but first reducing loads with smaller equipment can lead to even greater operational and upfront savings. A poorly designed envelope with a high-tech HVAC system is not, on the whole, efficient or cost-effective.
Don’t plan on using onsite renewable energy generation (see EAc2) to make your building energy-efficient. It is almost always more cost-effective to make an efficient building, and then to add renewables like photovoltaics as the “icing” on the cake.
Some rules of thumb to reduce energy use are:
Find the best credit compliance path based on your building type and energy-efficiency targets. Use the following considerations, noting that some projects are more suited to a prescriptive approach than others.
Option 1: Whole Building Energy Simulation requires estimating the energy use of the whole building over a calendar year, using methodology established by ASHRAE 90.1-2007, Appendix G. Option 1 establishes a computer model of the building’s architectural design and all mechanical, electrical, domestic hot water, plug load, and other energy-consuming systems and devices. The model incorporates the occupancy load and a schedule representing projected usage in order to predict energy use. This compliance path does not prescribe any technology or strategy, but requires a minimum reduction in total energy cost of 10% (5% for an existing building), compared to a baseline building with the same form and design but using systems compliant with ASHRAE 90.1-2007. You can earn additional LEED points through EAc1 for cost reductions of 12% and greater (8% for existing buildings).
Option 2: Prescriptive Compliance Path: ASHRAE Advanced Energy Design Guide refers to design guides published by ASHRAE for office, school, warehouse, and retail projects. These guides outline strategies to reduce energy use by 30% from ASHRAE 90.1-2001 levels, or an amount equivalent to a 10%–14% reduction from the ASHRAE 90.1-2007 standard. If you choose this compliance path, become familiar with the list of prescriptive requirements and commit to meeting them. (See the AEDG checklist in the Documentation Toolkit.)
Option 3: Prescriptive Compliance Path: Advanced Buildings Core Performance Guide is another, more basic prescriptive path. It’s a good option if your project is smaller than 100,000 ft2, cannot pursue Option 2 (because there is not an ASHRAE guide for the building type), is not a healthcare facility, lab, or warehouse—or you would rather not commit to the energy modeling required for Option 1. Your project can be of any other building type (such as office or retail). To meet the prerequisite, you must comply with all requirements within Sections 1 and 2 of the guide. If you choose this path, become familiar with the list of activities and requirements and commit to meeting them. (See Resources for a link to the Core Performance Guide and the Documentation Toolkit for the checklist of prescriptive items.)
EAc1: Optimize Energy Performance uses the same structure of Options 1–3, so it makes sense to think about the credit and the prerequisite together when making your choice. In EAc1, Option 1 offers the potential for far more points than Options 2 and 3, so if you see your project as a likely candidate for earning those points, Option 1 may be best.
Hotels, multifamily residential, and unconventional commercial buildings may not be eligible for either Option 2 or Option 3, because the prescriptive guidance of these paths was not intended for them. Complex projects, unconventional building types, off-grid projects, or those with high energy-reduction goals are better off pursuing Option 1, which provides the opportunity to explore more flexible and innovative efficiency strategies and to trade off high-energy uses for lower ones.
If your project combines new construction and existing building renovation then whatever portion contains more than 50% of the floor area would determine the energy thresholds.
Options 2 and 3 are suitable for small, conventional building types that may not have as much to gain from detailed energy modeling with Option 1.
Meeting the prescriptive requirements of Options 2 and 3 is not common practice and requires a high degree of attention to detail by your project team. (See the Documentation Toolkit for the Core Performance Guide Checklist.) These paths are more straightforward than Option 1, but don’t think of them as easy.
Options 2 and 3 require additional consultant time from architects and MEP engineers over typical design commitment, which means higher upfront costs.
Option 1 references the mandatory requirements of ASHRAE 90.1-2007, which are more stringent than earlier LEED rating systems that referred to ASHRAE 90.1-2004.
Option 1 energy simulation provides monthly and annual operating energy use and cost breakdowns. You can complete multiple iterations, refining energy-efficiency strategies each time. Payback periods can be quickly computed for efficiency strategies using their additional first costs. A building’s life is assumed to be 60 years. A payback period of five years is considered a very good choice, and 10 years is typically considered reasonable. Consult the OPR for your owners’ goals while selecting your efficiency strategies.
Option 1 energy simulation often requires hiring an energy modeling consultant, adding a cost (although this ranges, it is typically on the order of $0.10–$0.50/ft2 depending on the complexity). However, these fees produce high value in terms of design and decision-making assistance, and especially for complex or larger projects can be well worth the investment.
All compliance path options may require both the architectural and engineering teams to take some time in addition to project management to review the prescriptive checklists, fill out the LEED Online credit form, and develop the compliance document.
The architect, mechanical engineer, and lighting designer need to familiarize themselves and confirm compliance with the mandatory requirements of ASHRAE 90.1-2007, sections 5–9.
Use simple computer tools like SketchUp and Green Building Studio that are now available with energy analysis plug-ins to generate a first-order estimate of building energy use within a climate context and to identify a design direction. Note that you may need to refer to different software may not be the one used to develop complete the whole building energy simulations necessary for LEED certification.
Energy modeling can inform your project team from the start of design. Early on, review site climate data—such as temperature, humidity and wind, available from most energy software—as a team. Evaluate the site context and the microclimate, noting the effects of neighboring buildings, bodies of water, and vegetation. Estimate the distribution of energy across major end uses (such as space heating and cooling, lighting, plug loads, hot water, and any additional energy uses), targeting high-energy-use areas to focus on during design.
Use a preliminary energy use breakdown like this one to identify target areas for energy savings.Perform preliminary energy modeling in advance of the schematic design phase kick-off meeting or design charrette. The energy use breakdown can help identify targets for energy savings and point toward possible alternatives.
For existing buildings, the baseline energy model can reflect the pre-renovation features like rather than a minimally ASHRAE-compliant building. This will help you achieve additional savings in comparison with the baseline.
Projects generating renewable energy onsite should use Option 1 to best demonstrate EAp2 compliance and maximize points under EAc1. Other options are possible but won’t provide as much benefit. Like any other project, model the baseline case as a system compliant with ASHRAE 90.1-2007, using grid-connected electricity, and the design case is an “as-designed” system also using grid-connected electricity. You then plug in 100% onsite renewable energy in the final energy-cost comparison table, as required by the performance rating method (PRM) or the modeling protocol of ASHRRAE 90.1 2007, Appendix G. (Refer to the sample PRM tables in the Documentation Toolkit for taking account of onsite renewable energy.
LEED divides energy-using systems into two categories:
Besides energy modeling, you may need to use the exceptional calculation methodology (ECM) when any of the following situations occur:
Some energy-modeling software tools have a daylight-modeling capability. Using the same model for both energy and IEQc8.1: Daylight and Views—Daylight can greatly reduce the cost of your modeling efforts.
Provide a copy of the AEDG for office, retail, or warehouse, as applicable, to each team member as everyone, including the architect, mechanical and electrical engineers, lighting designer, and commissioning agents, are responsible for ensuring compliance. These are available to download free from the ASHRAE website. (See Resources.)
Find your climate zone before attempting to meet any detailed prescriptive requirements. Climate zones vary by county, so be sure to select the right one. (See the Documentation Toolkit for a list of climate zones by county.)
Develop a checklist of all requirements, and assign responsible team members to accomplish them. Hold a meeting to walk the team through the AEDG checklist for your project’s climate zone. Clarify specific design goals and prescriptive requirements in the OPR for EAp1: Fundamental Commissioning.
Early access to the AEDG by each team member avoids last-minute changes that can have cascading, and costly, effects across many building systems.
The AEDG prescriptive requirements include:
If your project team is not comfortable following these guidelines, consider switching to Option 1, which gives you more flexibility.
Although Option 2 is generally lower cost during the design phase than energy modeling, the compliance path is top heavy—it requires additional meeting time upfront for key design members.
Provide a copy of the New Buildings Institute Advanced Buildings: Core Performance Guide to each team member. The guide is available to download free from the NBI website. (See Resources.)
The guide provides practical design assistance that can be used throughout the design process.
Walk your team through the project checklist to clarify design goals and prescriptive requirements.
The guide provides an outline for approaching an energy-efficient design, in addition to a list of prescriptive measures. The first of its three sections emphasizes process and team interaction rather than specific building systems or features. Advise the owner to read through the guide in order to understand what is required of the architect and engineers.
Section 1 in the guide focuses on best practices that benefit the project during the pre-design and schematic design stages, such as analyzing alternative designs and writing the owner’s project requirements (OPR).
Section 2 of the Core Performance Guide describes architectural, lighting, and mechanical systems to be included. Section 3 is not required for EAp2 but includes additional opportunities for energy savings that can earn EAc1 points.
The guide mandates that your team develop a minimum of three different design concepts to select from for best energy use.
Though they can be a little daunting at first glance, a majority of the guide’s requirements overlap with other LEED credits, such as EAp1: Fundamental Commissioning, IEQp1: Minimum Indoor Air Quality Performance, and IEQc6.1: Controllability of Systems—Lighting Controls.
This compliance path is top-heavy due to upfront consultant time, but it provides adequate structure to ensure that your project is in compliance with the prerequisite requirements. For some projects it may be less expensive to pursue than Option 1.
The energy model itself will not account for any change in plug loads from the baseline case, even if your project is making a conscious effort to purchase Energy Star or other efficient equipment. Any improvement made in plug loads must be documented separately, using the exceptional calculation methodology (ECM), as described in ASHRAE 90.1-2007. These calculations determine the design case energy cost compared to the baseline case. They are included in the performance rating method (PRM) table or directly in the baseline and design case model.
The owner should now have finalized the OPR with the support of the architect, as part of the commissioning credits EAp1 and EAc3. The goals identified here will help your team identify energy-reduction and occupant-comfort strategies.
Consider a broad range of energy-efficiency strategies and tools, including passive solar, daylighting, cooling-load reduction, and natural ventilation to reduce heating and cooling loads.
Develop the basis of design (BOD) document in conjunction with your mechanical engineer and architect for EAp1: Fundamental Commissioning, noting key design parameters to help strategize design direction as outlined in the OPR.
The OPR and BOD serve the larger purpose of documenting the owner’s vision and your team’s ideas to meet those goals. The BOD is intended to be a work-in-progress and should be updated at all key milestones in your project. Writing the document gives you an opportunity to capture the owner’s goals, whether just to meet the prerequisite or to achieve points under EAc1.
Confirm that your chosen compliance path is the most appropriate for your project, and make any changes now. Following a review with the design team and owner, ensure that everyone is on board with contracting an energy modeler for Option 1 or meeting all the prescriptive requirements under Options 2 or 3.
Sometimes teams change from Option 1 to Options 2 or 3 very late in the design phase for various reasons including not realizing the cost of energy modeling. Making that change is risky, though: the prescriptive paths are all-or-nothing—you must comply with every item, without exception. Evaluate each requirement and consult with the contractor and estimator to ensure the inclusion of all activities within project management.
To avoid costly, last-minute decisions, develop a comprehensive, component-based cost model as a decision matrix for your project. The model will help establish additional cost requirements for each energy conservation measure. It will also illustrate cost reductions from decreased equipment size, construction rendered unnecessary by energy conservation measures, and reduced architectural provisions for space and equipment access. (See the Documentation Toolkit for an example.)
Use envelope design and passive strategies to reduce the heating and cooling loads prior to detailed design of HVAC systems. Passive strategies can reduce heating and cooling loads, giving the engineer more options, including smaller or innovative systems.
Load reduction requires coordinated efforts by all design members including the architect, lighting designer, interior designer, information-technology manager, and owner.
Involving facilities staff in the design process can further inform key design decisions, helping ensure successful operation and low maintenance costs.
Encourage your design team to brainstorm design innovations and energy-reduction strategies. This provides a communication link among team members so they can make informed decisions.
More energy-efficient HVAC equipment can cost more relative to conventional equipment. However, by reducing heating and cooling loads through good passive design, the mechanical engineer can often reduce the size and cost of the system. Reduced system size can save money through:
Review case studies of similar energy-efficient buildings in the same climate to provide helpful hints for selecting energy-efficiency measures. For example, a building in a heating-dominated climate can often benefit from natural ventilation and free cooling during shoulder seasons. (See Resources for leading industry journals showcasing success stories around the country and internationally.)
The relationship between first costs and operating costs can be complex. For example, more efficient windows will be more expensive, but could reduce the size and cost of mechanical equipment. A more efficient HVAC system may be more expensive, but will reduce operating costs. Play around with variables and different strategies to get the right fit for the building and the owner’s goals as stated in the OPR.
Review and confirm compliance with the mandatory requirements of all the relevant sections of ASHRAE 90.1-2007
Trust your project’s energy modeling task to a mechanical firm with a proven track record in using models as design tools, and experience with your building type.
Contract an energy modeling team for the project. These services may be provided by the mechanical engineering firm on the design team or by an outside consultant. Software used for detailed energy use analysis and submitted for final LEED certification must be accepted by the regulatory authority with jurisdiction, and must comply with paragraph G2.2 of ASHRAE Standard 90.1-2007. Refer to Resources for a list of Department of Energy approved energy-analysis software that may be used for LEED projects.
Design team members, including the architect and mechanical engineer at a minimum, need to work together to identify a percentage improvement goal for project energy use over the ASHRAE 90.1-2007-compliant baseline model. The percentage should be at least 10% to meet the prerequisite.
Plan on initiating energy modeling during the design process, and use it to inform your design—preferably executing several iterations of the design as you improve the modeled energy performance.
Ask the modeling consultant to develop an annual energy-use breakdown—in order to pick the “fattest” targets for energy reduction. A typical energy-use breakdown required for LEED submission and ASHRAE protocol includes:
Identify critical areas in which to reduce loads. For example, in a data center, the plug loads are the largest energy load. Small changes in lighting density might bring down the energy use but represent only a small fraction of annual energy use.
Don't forget that LEED (following ASHRAE) uses energy cost and not straight energy when it compares your design to a base case. That's important because you might choose to use a system that burns natural gas instead of electricity and come out with a lower cost, even though the on-site energy usage in kBtus or kWhs is higher. Generally you have to specify the same fuel in your design case and in the base case, however, so you can't simply switch fuels to show a cost savings
Explore and analyze design alternatives for energy use analyses to compare the cost-effectiveness of your design choices. For example, do you get better overall performance from a better window or from adding a PV panel? Will demand-control ventilation outperform increased ceiling insulation?
Simple, comparative energy analyses of conceptual design forms are useful ways to utilize an energy model at this stage. Sample scenarios include varying the area of east-facing windows and looking at 35% versus 55% glazing. Each scenario can be ranked by absolute energy use to make informed decisions during the design stage.
If your project is using BIM software, the model can be plugged into the energy analysis software to provide quick, real-time results and support better decisions.
Model development should be carried out following the PRM from ASHRAE 90.1-2007, Appendix G, and the LEED 2009 Design and Construction Reference Guide, Table in EAc1 and CS Appendix 2: Energy Modeling Guidelines. In case of a conflict between ASHRAE and LEED guidelines, follow LEED.
Projects using district energy systems have special requirements. For EAp2, the proposed building must achieve the 10% energy savings without counting the effects of the district generation system. To earn points in EAc1 you can take advantage of the district system’s efficiency, but you have to run the energy model again to claim those benefits (see EAc1 for details).
While you could run the required energy model at the end of the design development phase, simply to demonstrate your prerequisite compliance, you don’t get the most value that way in terms of effort and expense. Instead, do it early in the design phase, and run several versions as you optimize your design. Running the model also gives you an opportunity to make improvements if your project finds itself below the required 10% savings threshold.
The baseline model is the designed building with mechanical systems specified in ASHRAE 90.1-2007, Appendix G, for the specific building type, with a window-to-wall ratio at a maximum of 40%, and minimally code-compliant specifications for the envelope, lighting, and mechanical components. It can be developed as soon as preliminary drawings are completed. The baseline is compared to the design case to provide a percentage of reduction in annual energy use. To avoid any bias from orientation, you need to run the baseline model in each of the four primary directions, and the average serves as your final baseline figure.
The design-case is modeled using the schematic design, orientation, and proposed window-to-wall ratio—¬the model will return design-case annual energy costs. Earn points by demonstrating percentage reductions in annual energy costs from the design to the baseline case. EAp2 is achieved if the design case is 10% lower than the baseline in new construction (or 5% less in existing building renovations).
Provide as much project and design detail to the modeler as possible. A checklist is typically developed by the energy modeler, listing all the construction details of the walls, roof, slabs, windows, mechanical systems, equipment efficiencies, occupancy load, and schedule of operations. Any additional relevant information or design changes should be brought to the modeler’s attention as soon as possible. The more realistic the energy model is, the more accurate the energy use figure, leading to better help with your design.
Invite energy modelers to project meetings. An experienced modeler can often assist in decision-making during design meetings, even without running complete models each time.
All known plug loads must be included in the model. The baseline and design-case models assume identical plug loads. If your project is deliberately attempting to reduce plug loads, demonstrate this by following the exceptional calculation method (ECM), as described in ASHRAE 90.1-2007, G2.5. Incorporate these results in the model to determine energy savings.
For items outside the owner’s control—like lighting layout, fans and pumps—the parameters for the design and baseline models must be identical.
It can take anywhere from a few days to a few weeks to generate meaningful energy modeling results. Schedule the due dates for modeling results so that they can inform your design process.
Review the rate structure from your electrical utility. The format can inform your team of the measures likely to be most effective in reducing energy costs, especially as they vary over season, peak load, and additional charges beyond minimum energy use.
Performing a cost-benefit analysis in conjunction with energy modeling can determine payback times for all the energy strategies, helping the iterative design process.
Using energy modeling only to check compliance after the design stage wastes much of the value of the service, and thus your investment.
The architect and mechanical engineer should carefully read the applicable ASHRAE Advanced Energy Design Guide for office, warehouse, or retail projects, as applicable.
Keep the owner abreast of the design decisions dictated by the standard. Fill in the team-developed checklist, within the climate zone table’s prescribed requirements, with appropriate envelope improvements, system efficiencies, and a configuration that meets the standard requirements.
As a prescriptive path, this option relies heavily on following the requirement checklist, which is used throughout the design process to track progress. To assist design development, provide all critical team members—not limited to the architect, mechanical and electrical engineers, and lighting designer—with a checklist highlighting their appointed tasks.
The architect, mechanical engineer, and lighting designer need to discuss each requirement and its design ramifications. Hold these meetings every six to eight weeks to discuss progress and make sure all requirements are being met.
Core and Shell projects must mandate the requirements for the tenant spaces within a tenant guideline document such as one developed for SSc9: Tenant Design and Construction Guidelines.
Confirm that your project team is comfortable with following all the prescribed requirements. If not, switch to Option 1: Whole Building Energy Simulation.
The LEED Online credit form does not specify how to document each prescriptive requirement because they are so different for each project; it only requires a signed confirmation by the MEP for meeting AEDG requirements. You still have to provide documentation. Submit your checklist of requirements, and supporting information for each item, through LEED Online to make your case. If your project fails to meet even one requirement, it will fail to earn the prerequisite, thus jeopardizing LEED certification.
Although energy modeling consultant costs are avoided by this option, additional staff time will be required to document and track compliance status, as compared with conventional projects.
Energy efficiency measures prescribed by the guide can be perceived as additional costs in comparison with conventional projects. However, they are easy to implement and are cost-effective pn the whole.
Become familiar with the Core Performance Guide early in the design phase to know the multiple requirements and all requisite documents.
Note that the guide demands additional time, attention, and integrated process from the design team as compared to conventional projects. It’s not just a list of prescriptive requirements, but a prescribed process for achieving energy efficiency goals. LEED Online documentation requires proof of all steps outlined in Sections 1 and 2, including three conceptual design options and meeting minutes. The project manager, architect, and mechanical engineer should read the complete Core Performance Guide carefully to know beforehand the prescriptive requirements in Sections 1 and 2.
The project manager must take responsibility for ensuring that the requirement checklist is on track.
For Section 3, the design team needs to identify three or more of the listed strategies as possible targets for the project.
Create a checklist of requirements and assign a responsible party to each item.
The Core Performance Guide requires an integrated design contributed by the architect, mechanical and electrical engineers, and lighting designer. The project manager must take responsibility for shepherding and documenting the collaborative process to demonstrate compliance.
A long documentation list can be overwhelming for your team, so create a detailed checklist with tasks delegated to individual team members, allowing each member to focus on assigned tasks. The checklist can function as a status tracking document and, finally, the deliverable for LEED Online.
The architect and engineer, and other project team members, continue to develop a high-performance building envelope with efficient mechanical and lighting systems.
Constant communication and feedback among project team members, owner, and if possible, operational staff, during design development can minimize construction as well as operational costs and keep your project on schedule.
If you change or go through value-engineering on any specifications, such as the solar-heat gain coefficient of glazing, for example, be aware of impacts on mechanical system sizing. Making changes like this might not pay off as much as it first appears.
Consider using building information modeling (BIM) tools to keep design decisions up to date and well documented for all team members.
Schedule delays can be avoided if all team members share their ideas and update documents during the design development process.
The modeler completes the energy analysis of the selected design and system and offers alternative scenarios for discussion. The modeler presents the energy cost reduction results to the team, identifying the LEED threshold achieved.
It’s helpful for the energy modeling report to include a simple payback analysis to assist the owner in making an informed decision on the operational savings of recommended features.
Demonstrating reductions in non-regulated loads requires a rigorous definition of the baseline case. The loads must be totally equivalent, in terms of functionality, to the proposed design case. For example, reducing the number of computers in the building does not qualify as a legitimate reduction in non-regulated loads. However, the substitution of laptops for desktop computers, and utilization of flat-screen displays instead of CRTs for the same number of computers, may qualify as a reduction.
Residential and hospitality projects that use low-flow showers, lavatories, and kitchen sinks (contributing to WEp1) benefit from lower energy use due to reduced overall demand for hot water. However, for energy-savings calculations, these are considered process loads that must be modeled as identical in baseline and design cases, or you have the choice of demonstrating the savings with ECM for process loads.
Perform daylight calculations in conjunction with energy modeling to balance the potentially competing goals of more daylight versus higher solar-heat gain resulting in high cooling loads.
If your project is pursuing renewable energy, the energy generated is accounted for by using the PRM. These results provide information about whether the energy is contributing to EAc2: Onsite Renewable Energy.
A cost-benefit analysis can help the owner understand the return on investment of big-ticket, energy-conserving equipment that lowers operating energy bills with a quick payback.
Complete at least half of the energy modeling effort by the end of the design development stage. Help the design team to finalize strategy through intensive, early efforts in energy modeling. Once the team has a design direction, the modeler can develop a second model during the construction documents phase for final confirmation.
If pursuing ECM for non-regulated loads, calculate energy saving for each measure separately if you are, for example, installing an energy-efficient elevator instead of a typical one so that the reduction would contribute to total building energy savings. Calculate the anticipated energy use of the typical elevator in kBTUs or kWh. Using the same occupancy load, calculate the energy use of the efficient elevator. Incorporate the savings into design case energy use within the PRM. Refer to the ECM strategy for detailed calculation guidelines.
Ensure that all prescriptive requirements are incorporated into the design by the end of the design development stage.
Revisit the Advanced Energy Design Guides (AEDG) checklist to ensure that the design meets the prescriptive requirements.
The mechanical engineer, lighting consultant, and architect revisit the checklist for an update on the requirements and how they are being integrated into the design. All prescriptive requirements should be specifically incorporated into the design by the end of the design development phase.
The mechanical engineer and architect track the status of each requirement.
While the LEED Online credit form does not require detailed documentation for each Core Performance Guide requirement, it is important that each item be documented as required and reviewed by the rest of the team to confirm compliance, especially as further documentation may be requested by during review. Your design team should work with the owner to identify cost-effective strategies from Section 3 that can be pursued for the project.
The architect and HVAC engineer should agree on the design, working with the cost estimator and owner.
Construction documents clearly detail the architectural and mechanical systems that address energy-efficiency strategies.
Confirm that specifications and the bid package integrate all equipment and activities associated with the project.
If the project goes through value engineering, refer to the OPR and BOD to ensure that no key comfort, health, productivity, daylight, or life-cycle cost concerns are sacrificed.
During the budget estimating phase, the project team may decide to remove some energy-saving strategies that have been identified as high-cost items during the value-engineering process. However, it is very important to help the project team understand that these so-called add-ons are actually integral to the building’s market value and the owner’s goals.
Removing an atrium, for example, due to high cost may provide additional saleable floor area, but may also reduce daylight penetration while increasing the lighting and conditioning loads.
Although this prerequisite is a design-phase submittal, it may make sense to submit it, along with EAc1, after construction. Your project could undergo changes during construction that might compel a new run of the energy model to obtain the latest energy-saving information. Waiting until the completion of construction ensures that the actual designed project is reflected in your energy model.
Create a final energy model based completely on construction document drawings—to confirm actual energy savings as compared to ASHRAE 90.1-2007 requirements. An energy model based on the construction documents phase will provide realistic energy-cost savings and corresponding LEED points likely to be earned.
Make sure the results fit the LEED Online credit form requirements. For example, the unmet load hours have to be less than 300 and process loads will raise a red flag if they’re not approximately 25%. If any of the results are off mark, take time to redo the model. Time spent in design saves more later on in the LEED review process.
Finalize all design decisions and confirm that you’ve met all of the prescriptive requirements. Your team must document the checklist with relevant project drawings, including wall sections, specifications, and the MEP drawing layout.
Value engineering and other factors can result in design changes that eliminate certain energy features relevant to the prerequisite. As this compliance path is prescriptive, your project cannot afford to drop even one prescribed item.
Value engineering and other factors can result in design changes that eliminate certain energy features relevant to the credit. As this compliance path is prescriptive, your project cannot afford to drop even one listed item. Although perceived as high-cost, prescriptive requirements lower energy costs during operation and provide a simple payback structure.
The architect and mechanical engineer review the shop drawings to confirm the installation of the selected systems.
The commissioning agent and the contractor conduct functional testing of all mechanical equipment in accordance with EAp1: Fundamental Commissioning and EAc3: Enhanced Commissioning.
Find your Energy Star rating with EPA’s Target Finder tool if your building type is in the database. Input your project location, size, and number of occupants, computers, and kitchen appliances. The target may be a percentage energy-use reduction compared to a code-compliant building, or “anticipated energy use” data from energy model results. Add information about your fuel use and rate, then click to “View Results.” Your Target Finder score should be documented at LEED Online.
Plan for frequent site visits by the mechanical designer and architect during construction and installation to make sure construction meets the design intent and specifications.
Emphasize team interaction and construction involvement when defining the project scope with key design team members. Contractor and designer meetings can help ensure correct construction practices and avoid high change-order costs for the owner.
Subcontractors may attempt to add a premium during the bidding process for any unusual or unknown materials or practices, so inform your construction bidders of any atypical design systems at the pre-bid meeting.
The energy modeler ensures that any final design changes have been incorporated into the updated model.
Upon finalizing of the design, the responsible party or energy modeler completes the LEED Online submittal with building design inputs and a PRM result energy summary.
Although EAp2 is a design phase submittals, it may make sense to submit it (along with EAc1) after construction. Your project could undergo changes during construction that might require a new run of the energy model. Waiting until the completion of construction ensures that your actual designed project is reflected. On the other hand, it gives you less opportunity to respond to questions that might come up during a LEED review.
Include supporting documents like equipment cut sheets, specifications and equipment schedules to demonstrate all energy efficiency measures claimed in the building.
It common for the LEED reviewers to make requests for more information. Go along with the process—it doesn’t mean that you’ve lost the credit. Provide as much information for LEED Online submittal as requested and possible.
The design team completes the LEED Online documentation, signing off on compliance with the applicable AEDG, and writing the narrative report on the design approach and key highlights.
During LEED submission, the project team needs to make an extra effort to support the prerequisite with the completed checklist and the required documents. Although the LEED rating system does not list detailed documentation, it is best practice to send in supporting documents for the prescriptive requirements from the AEDG. The supporting documents should include relevant narratives, wall sections, mechanical drawings, and calculations.
Although the LEED Online sign-off does not include a checklist of AEDG requirements, it assumes that the team member is confirming compliance with all detailed requirements of the guide.
The design team completes the LEED Online credit form, signing off on compliance with the Core Performance Guide, and writing the narrative report on the design approach and key highlights.
During LEED submission, your project team needs to make an extra effort to support the prerequisite with the completed checklist and the required documents. Although not every requirement may be mentioned in the LEED documentation, the supporting documents need to cover all requirements with narratives, wall sections, mechanical drawings, and calculations.
Many of this option’s compliance documents are common to other LEED credits or design documents, thus reducing duplicated efforts.
Develop an operations manual with input from the design team in collaboration with facility management and commissioning agent if pursuing EAc3: Enhanced Commissioning.
The benefit of designing for energy efficiency is realized only during operations and maintenance. Record energy use to confirm that your project is saving energy as anticipated. If you are not pursuing EAc5: Measurement and Verification, you can implement tracking procedures such as reviewing monthly energy bills or on-the-spot metering.
Some energy efficiency features may require special training for operations and maintenance personnel. For example, cogeneration and building automation systems require commissioning and operator training. Consider employing a trained professional to aid in creating operation manuals for specialty items.
Energy-efficiency measures with a higher first cost often provide large savings in energy use and operational energy bills. These credit requirements are directly tied to the benefits of efficient, low-cost operations.
Excerpted from LEED 2009 for Core and Shell Development
To establish the minimum level of energy efficiency for the proposed building and systems to reduce environmental and economic impacts associated with excessive energy use.
Demonstrate a 10% improvement in the proposed building performance rating for new buildings, or a 5% improvement in the proposed building performance rating for major renovations to existing buildings, compared with the baseline building performanceBaseline building performance is the annual energy cost for a building design, used as a baseline for comparison with above-standard design. rating.
Calculate the baseline building performance rating according to the building performance rating method in Appendix G of ANSI/ASHRAE/IESNA Standard 90.1-2007 (with errata but without addenda1) using a computer simulation model for the whole building project. Projects outside the U.S. may use a USGBC approved equivalent standard2.
Appendix G of Standard 90.1-2007 requires that the energy analysis done for the building performance rating method include all energy costs associated with the building project. To achieve points using this credit, the proposed design must meet the following criteria:
For the purpose of this analysis, process energy is considered to include, but is not limited to, office and general miscellaneous equipment, computers, elevators and escalators,kitchen cooking and refrigeration, laundry washing and drying, lighting exempt from the lighting power allowance (e.g., lighting integral to medical equipment) and other (e.g., waterfall pumps).
Regulated (non-process) energy includes lighting (for the interior, parking garage, surface parking, façade, or building grounds, etc. except as noted above), heating, ventilation and air conditioning (HVAC) (for space heating, space cooling, fans, pumps, toilet exhaust, parking garage ventilation, kitchen hood exhaust, etc.), and service water heating for domestic or space heating purposes.
Process loads must be identical for both the baseline building performance rating and the proposed building performance rating. However, project teams may follow the exceptional calculation method (ANSI/ASHRAE/IESNA Standard 90.1-2007 G2.5) or USGBC approved equivalent to document measures that reduce process loads. Documentation of process load energy savings must include a list of the assumptions made for both the base and the proposed design, and theoretical or empirical information supporting these assumptions.
Projects in California may use Title 24-2005, Part 6 in place of ANSI/ASHRAE/IESNA Standard 90.1-2007 for Option 1.
Comply with the prescriptive measures of the ASHRAE Advanced Energy Design Guide appropriate to the project scope, outlined below. Project teams must comply with all applicable criteria as established in the Advanced Energy Design Guide for the climate zoneOne of five climatically distinct areas, defined by long-term weather conditions which affect the heating and cooling loads in buildings. The zones were determined according to the 45-year average (1931-1975) of the annual heating and cooling degree-days (base 65 degrees Fahrenheit). An individual building was assigned to a climate zone according to the 45-year average annual degree-days for its National Oceanic and Atmospheric Administration (NOAA) Division. in which the building is located. Projects outside the U.S. may use ASHRAE/ASHRAE/IESNA Standard 90.1-2007 Appendices B and D to determine the appropriate climate zone.
The building must meet the following requirements:
Comply with the prescriptive measures identified in the Advanced Buildings™ Core Performance™ Guide developed by the New Buildings Institute. The building must meet the following requirements:
Projects outside the U.S. may use ASHRAE/ASHRAE/IESNA Standard 90.1-2007 Appendices B and D to determine the appropriate climate zone.
Projects in Brazil that are certified at the “A” level under the Regulation for Energy Efficiency Labeling (PBE Edifica) program for all attributes (Envelope, Lighting, HVAC) achieve this prerequisite. The following building types cannot achieve this prerequisite using this option: Healthcare, Data Centers, Manufacturing Facilities, Warehouses, and Laboratories.
1Project teams wishing to use ASHRAE approved addenda for the purposes of this prerequisite may do so at their discretion. Addenda must be applied consistently across all LEED credits.
2 Projects outside the U.S. may use an alternative standard to ANSI/ASHRAE/IESNA Standard 90.1-2007 if it is approved by USGBC as an equivalent standard using the process identified in the LEED 2009 Green Building Design and Construction Global ACP Reference Guide Supplement.
The following pilot alternative compliance path is available for this prerequisite. See the pilot credit library for more information.
EApc95: Alternative Energy Performance Metric ACP
Design the building envelope and systems to meet baseline requirements. Use a computer simulation model to assess the energy performance and identify the most cost-effective energy efficiency measures. Quantify energy performance compared with a baseline building.
If local code has demonstrated quantitative and textual equivalence following, at a minimum, the U.S. Department of Energy (DOE) standard process for commercial energy code determination, then the results of that analysis may be used to correlate local code performance with ANSI/ASHRAE/IESNA Standard 90.1-2007. Details on the DOE process for commercial energy code determination can be found at http://www.energycodes.gov/implement/ determinations_com.stm.
1 Project teams wishing to use ASHRAE approved addenda for the purposes of this prerequisite may do so at their discretion. Addenda must be applied consistently across all LEED credits.
2 Projects outside the U.S. may use an alternative standard to ANSI/ASHRAE/IESNA Standard 90.1‐2007 if it is approved by USGBC as an equivalent standard using the process located at www.usgbc.org/leedisglobal
Useful web resource with information on local/regional incentives for energy-efficiency programs.
This database shows state-by-state incentives for energy efficiency, renewable energy, and other green building measures. Included in this database are incentives on demand control ventilation, ERVs, and HRVs.
ACEEE is a nonprofit organization dedicated to advancing energy efficiency through technical and policy assessments; advising policymakers and program managers; collaborating with businesses, public interest groups, and other organizations; and providing education and outreach through conferences, workshops, and publications.
The New Buildings Institute is a nonprofit, public-benefits corporation dedicated to making buildings better for people and the environment. Its mission is to promote energy efficiency in buildings through technology research, guidelines, and codes.
The Building Energy Codes program provides comprehensive resources for states and code users, including news, compliance software, code comparisons, and the Status of State Energy Codes database. The database includes state energy contacts, code status, code history, DOE grants awarded, and construction data. The program is also updating the COMcheck-EZ compliance tool to include ANSI/ASHRAE/IESNA 90.1–2007. This compliance tool includes the prescriptive path and trade-off compliance methods. The software generates appropriate compliance forms as well.
Research center at RPI provides access to a wide range of daylighting resources, case studies, design tools, reports, publications and more.
International association of energy modelers with various national and local chapters.
Non-profit organization aiming at design community to increase collaboration for designing energy efficient buildings.
The Low Impact Hydropower Institute is a non-profit organization and certification body that establishes criteria against which to judge the environmental impacts of hydropower projects in the United States.
The Building Technologies Program (BTP) provides resources for commercial and residential building components, energy modeling tools, building energy codes, and appliance standards including the Buildings Energy Data Book, High Performance Buildings Database and Software Tools Directory.
This website discusses the step-by-step process for energy modeling.
This online resource, supported by Natural Resources Canada, presents energy-efficient technologies, strategies for commercial buildings, and pertinent case studies.
This website is a comprehensive resource for U.S. Department of Energy information on energy efficiency and renewable energy and provides access to energy links and downloadable documents.
Information on cogenerationThe simultaneous production of electric and thermal energy in on-site, distributed energy systems; typically, waste heat from the electricity generation process is recovered and used to heat, cool, or dehumidify building space. Neither generation of electricity without use of the byproduct heat, nor waste-heat recovery from processes other than electricity generation is included in the definition of cogeneration., also called combined heat and power, is available from EPA through the CHPCombined heat and power (CHP), or cogeneration, generates both electrical power and thermal energy from a single fuel source. Partnership. The CHP Partnership is a voluntary program seeking to reduce the environmental impact of power generation by promoting the use of CHP. The Partnership works closely with energy users, the CHP industry, state and local governments, and other clean energy stakeholders to facilitate the development of new projects and to promote their environmental and economic benefits.
Free download of AHSRAE energy savings guide, use for Option 2.
Research warehouse for strategies and case studies of energy efficiency in buildings.
An online window selection tool with performance characteristics.
This website lays out design process for developing an energy efficient building.
This website discusses ways to improve design for lower energy demand as they relate to the AIA 2030 challenge.
This website includes discussion of design issues, materials and assemblies, window design decisions and case studies.
This site lists multiple web-based and downloadable tools that can be used for energy analyses.
This database is maintainted by the California Energy Commission and lists resources related to energy use and efficiency.
Energy design tools are available to be used for free online or available to download.
This website lists performance characteristics for various envelope materials.
This is an online forum of discussion for energy efficiency, computer model software users.
Target Finder is a goal-setting tool that informs your design team about their project’s energy performance as compared to a national database of projects compiled by the EPA.
This directory provides information on 406 building software tools for evaluating energy efficiency, renewable energy, and sustainability in buildings.
Weather data for more than 2100 locations are available in EnergyPlus weather format.
Weather data for U.S. and Non-U.S. locations in BIN format.
A web-based, free content project by IBPSA-USA to develop an online compendium of the domain of Building Energy Modeling (BEM). The intention is to delineate a cohesive body of knowledge for building energy modeling.
A guide for achieving energy efficiency in new commercial buildings, referenced in the LEED energy credits.
This manual is a strategic guide for planning and implementing energy-saving building upgrades. It provides general methods for reviewing and adjusting system control settings, plus procedures for testing and correcting calibration and operation of system components such as sensors, actuators, and controlled devices.
This manual offers guidance to building energy modelers, ensuring technically rigorous and credible assessment of energy performance of commercial and multifamily residential buildings. It provides a streamlined process that can be used with various existing modeling software and systems, across a range of programs.
Chapter 19 is titled, “Energy Estimating and Modeling Methods”. The chapter discusses methods for estimating energy use for two purposes: modeling for building and HVAC system design and associated design optimization (forward modeling), and modeling energy use of existing buildings for establishing baselines and calculating retrofit savings (data-driven modeling).
Required reference document for DES systems in LEED energy credits.
ASHRAE writes standards for the purpose of establishing consensus for: 1) methods of test for use in commerce and 2) performance criteria for use as facilitators with which to guide the industry.
Energy statistics from the U.S. government.
This guide includes instructional graphics and superior lighting design solutions for varying types of buildings and spaces, from private offices to big box retail stores.
This website offers information on energy efficiency in buildings, highlighting success stories, breakthrough technology, and policy updates.
Bimonthly publication on case studies and new technologies for energy efficiency in commercial buildings.
AIA publication highlighting local and state green building incentives.
2008 guidelines and performance goals from the National Science and Technology Council.
Information about energy-efficient building practices available in EDR's Design Briefs, Design Guidelines, Case Studies, and Technology Overviews.
DOE tools for whole building analyses, including energy simulation, load calculation, renewable energy, retrofit analysis and green buildings tools.
This is a computer program that predicts the one-dimensional transfer of heat and moisture.
DesignBuilder is a Graphical User Interface to EnergyPlus. DesignBuilder is a complete 3-D graphical design modeling and energy use simulation program providing information on building energy consumption, CO2Carbon dioxide emissions, occupant comfort, daylighting effects, ASHRAE 90.1 and LEED compliance, and more.
IES VE Pro is an integrated computing environment encompassing a wide range of tasks in building design including model building, energy/carbon, solar, light, HVAC, climate, airflow, value/cost and egress.
Use this checklist of prescriptive requirements (with sample filled out) to have an at-a-glance picture of AEDG requirements for Option 2, and how your project is meeting them.
This spreadsheet lists all the requirements for meeting EAp2 – Option 3 and and EAc1 – Option 3. You can review the requirements, assign responsible parties and track status of each requirement through design and construction.
Sometimes the energy simulation software being used to demonstrate compliance with Option 1 doesn't allow you to simulate key aspects of the design. In this situation you'll need to write a short sample narrative, as in these examples, describing the situation and how it was handled.
In your supporting documentation, include spec sheets of equipment described in the Option 1 energy model or Options 2–3 prescriptive paths.
This is a sample building energy performance and cost summary using the Performance Rating Method (PRM). Electricity and natural gas use should be broken down by end uses including space heating, space cooling, lights, task lights, ventilation fans, pumps, and domestic hot water, at the least.
Option 1 calculates savings in annual energy cost, but utility prices may vary over the course of a year. This sample demonstrates how to document varying electricity tariffs.
This graph, for an office building design, shows how five overall strategies were implemented to realize energy savings of 30% below an ASHRAE baseline. (From modeling conducted by Synergy Engineering, PLLC.)
The climate zones shown on this Department of Energy map are relevant to all options for this credit.
This spreadsheet, provided here by 7group, can be used to calculate the fan volume and fan power for Appendix G models submitted for EAp2/EAc1. Tabs are included to cover both ASHRAE 90.1-2004 and 90.1-2007 Appendix G methodologies.
Sample LEED Online forms for all rating systems and versions are available on the USGBC website.
Documentation for this credit can be part of a Design Phase submittal.
We have Core & Shell project while calculating the area of the locations, Pif and EAp2 have difference approximately 4% please let us know what is the maximum percentage deviation.
I don't think this would be a problem. If you were using the older forms and not the new excel spreadsheet you would see that there was an allowance of 10% when referencing the model area compared to PIf area.
I am James, eQuest beginner, and have a simple question.
I tried to ask eQuest people but no response so I upload question here.
I have E-series reports after running eQuest but the annual energy use baseline shows all zero both at site & at source.
I must miss something but couldn't figure it out.
Can anyone tell me what did I miss?
Any advice would be grateful.
Hi James - There could be any number of reasons for this which is probably why you have not been getting any responses. Your question is too broad and general. Figure out as much as you can on your own and then ask more specific questions and you will likely get responses. It is hard to give someone basic training in a forum for specific questions.
Did you get some numbers yet?
I appreciate your response.
In fact, I find how to get percent savings from eQuest 3-65.
It can be obtained from File->Export File->LEED Results (CSV)...
Then, in the pop up window, click the "Export LEED Results".
This is what I am looking for.
I couldn't find this from the classic ES-C/D reports.
So that settles.
Sorry for confusing you.
I have a heating-only warehouse (with small conditioned office) I'm modeling for C&S 2009. Based on the heating consumption in the proposed design, the warehouse space qualifies as semi-conditioned. For the Baseline I used the 5.5 envelope requirements for semi-heated space and System 9 with the required parameters: 80% efficiency and a 105deg supply temp. GBCIThe Green Building Certification Institute (GBCI) manages Leadership in Energy and Environmental Design (LEED) building certification and professional accreditation processes. It was established in 2008 with support from the U.S. Green Building Council (USGBC). did not take issue with me claiming this space was semi-heated, but they did provide me with the following comment as part of their design-phase review:
"Baseline HVAC system types in Table G3.1.1.A can be modeled for conditioned spaces only, whereas semi-conditioned spaces in the Baseline model must be modeled using the HVAC system type from the actual design. Revise the Baseline model so that the HVAC systems that serve semi-heated spaces are modeled according to the actual design. Ensure that the HVAC parameters such as heating source type, heating efficiency, and fan power are modeled identically between the models. Additionally, note that heating capacity and supply air volume for the Baseline model must be auto-sized using the temperature setpointsSetpoints are normal operating ranges for building systems and indoor environmental quality. When the building systems are outside of their normal operating range, action is taken by the building operator or automation system. and temperature difference from the actual design."
I do not see anything in 90.1 that says systems must be equal if the space is semi-conditioned. There is nothing to that effect in Table G3.1 (section 10). I do not see anything in G22.214.171.124 that says I have to use a different efficiency for the Baseline if it is semi-conditioned. I do not see anything in G126.96.36.199.2 (addendum dn) that says I must use the design temperature difference instead of 105deg. It certainly seems odd that some parameters must be held equal but some must be determined using the usual auto-sizing.
In addition to savings from the envelope, since I can classify this as semi-conditioned, we are benefiting from 92% efficiency heating units which use a 160deg supply air temperature. If I have to bring the Baseline up to equal these parameters, obviously we're going to lose points, so I want to avoid that.
Has anyone had a similar experience with a LEED review on this topic? After a quick search, I did not see any LEED Interpretations that seemed relevant. Can anyone point me to language in 90.1 that directs me to do what GBCI is telling me to do? Ultimately, the LEED reviewer determines what is and is not acceptable, but I do not see any justification for their comment in the ASHRAE text. Thanks for your input.
It does not sound right to me either. I would suggest you submit a project team inquiry to the reviewer through the contact us page on USGBC's web site. Ask them to cite the justification and question the comment.
I can't figure it out how to model an excepted spaces and its baseline systems correctly. Here is my issue:
We are working on office building, C&S v2009, HVAC completely designed. According to G3.1.1 exception (b) I need to model separate HVAC system for server rooms (but not only for server rooms), the primary HVAC system is system 7. Since server rooms are unoccupied but conditioned by DX systems it should has its own baseline HVAC system if I am not wrong - it should be system 3. In case when server rooms are not directly supplied by OA but they are supplied by transfer air from office spaces, how should be system 3 set? The issue is that in such a configuration of HVAC systems we will have increased OA ventilation rates in baseline against the proposed which will occur in Table 1.4 in "Outdoor Airflow" totals. When we consider the other excepted spaces with transfer air and model the separate systems the OA vent rates might be twice as high as in proposed when I exaggerate it. And it's not only about OA rates but fan energy etc. So what to do? Or it's not such a problem and it would be OK just explain the discrepancies in OA vent rates between proposed and baseline in narration? Or myabe the best question is: Must be the Minimum Outdoor Airflow Totals the same in Table 1.4 for P and B?
Thanks in advance for any help and suggestions!
If the proposed system has no outside air then the corresponding baseline system should not either. Always remember that you are not "designing" the baseline system to function. The outside air must be identical. It must be identical in the Table 1.4 documents and the models.
Thank you Marcus.
We have an apartment building project. In 1 dwelling unit has 1 bedroom 1 living unit and restroom. Do I need to separate between bedroom and living quarter ? Can I grouping it in 1 thermal zone per 1 dwelling unit?
We use eQUEST for simulate this model and it have some limit for zone.
The zone is too much if we separate all of the zone for 29 floors building even we used floor multiply method.
Thank you in advance.
See ASHRAE 90.1-2007 Table G3.1-9. You can zone it a couple of ways.
If exhaust fans serving unconditioned spaces are considered as a process loads (e.g. parking garage exhaust fans) and should be modeled as in proposed case, it means that it should be modeled with exactly the same eff., PD and Pfan? Or these fans are also regulated and it is necessary to follow Table 10.8 of Standard? In that case I presume the calculation of Pfan depends on wheter the fan is CAV or VAVVariable Air Volume (VAV) is an HVAC conservation feature that supplies varying quantities of conditioned (heated or cooled) air to different parts of a building according to the heating and cooling needs of those specific areas. and also if residential or non-res... So if I have office buidling and the fans in question are CAV I should use bhp equation for "Systems 3-4".
Is that assumption correct?
Thank you very much!
Yes they should be modeled identically. Just the fan motors are regulated, not their use in that application like the HVAC system fans. You can claim credit for using premium efficiency motors in this application as an exceptional calculation.
Yes in your proposed model use the BHP of the fans in accordance with the design.
Thank you Marcus. Now I see what you mean, but we are outside the U.S. It means that our garage fan motors do not follow Standard efficiency requirements according to Table 10.8. We have designed fan motors according to Eurovent standards and that's the point what confuses me, because our fan motor design is little more efficient as it is required by Table 10.8. I still don't get it if in this case the Baseline garage fan motors should be as designed in proposed or should follow minimum nominal full-load efficiency listed in Table 10.8? So the Pfan will be different of course.
So if you do an exceptional calculation you can claim credit for motor efficiency in a process load. The baseline is according to Table 10.8, the proposed as designed.
If you don't do an exceptional calculation then model the baseline identical to the proposed design.
I appreciate your help Marcus! Thank you.
For HVAC systems that consist of Fan Coil Units with Air Handling Units providing 100% Outside air - constant volume (based on the min ASHRAE 62.1 requirements) - Will the baseline systems require heat recovery as per ASHRAE 90.1 G188.8.131.52. All our AHU1.Air-handling units (AHUs) are mechanical indirect heating, ventilating, or air-conditioning systems in which the air is treated or handled by equipment located outside the rooms served, usually at a central location, and conveyed to and from the rooms by a fan and a system of distributing ducts. (NEEB, 1997 edition)
2.A type of heating and/or cooling distribution equipment that channels warm or cool air to different parts of a building. This process of channeling the conditioned air often involves drawing air over heating or cooling coils and forcing it from a central location through ducts or air-handling units. Air-handling units are hidden in the walls or ceilings, where they use steam or hot water to heat, or chilled water to cool the air inside the ductwork.'s specified have a design air capcity of greater than 2400 l/s. Not sure if this requirement applies to constant volume systems supplying min outdoor air ? can anyone provide guidance on this ?
The Proposed systems do not matter. Model the baseline systems according to Appendix G. See G3.1.1 which tells you how to zone the baseline HVAC system depending on the type of system. If any of the baseline systems require heat recovery according to G184.108.40.206 then include it in the baseline model.
Hi Marcus, Thanks for your comment. I am also wondering if the outdoor air modelled in both the baseline and proposed models should be the same OR is it the Minimum outdoor air quantity. I have a baseline auto sized model that has a much higher outdoor air quantity in CFM compared to the proposed model but the min. levels of the same. For info its not a VAVVariable Air Volume (VAV) is an HVAC conservation feature that supplies varying quantities of conditioned (heated or cooled) air to different parts of a building according to the heating and cooling needs of those specific areas. system. Can you please provide some guidnace ?
The quantity of OA should be identical in both models. Only exception is if the Proposed has demand controlled ventilation.
Another exception could be if in a model there is an economizerAn economizer is a device used to make building systems more energy efficient. Examples include HVAC enthalpy controls, which are based on humidity and temperature. that increase the OA flow rate in order to minimize the cooling demand, correct?
Not really an exception per se, more like a different situation. The outside ventilation air should be identical in both models. The situation you describe would be bringing more OA into the building than is necessary for ventilation. If there is an economizerAn economizer is a device used to make building systems more energy efficient. Examples include HVAC enthalpy controls, which are based on humidity and temperature. in one model and not the other the OA flow will vary when the economizer is operating but that is not to meet the ventilation requirements, it is to provide free cooling. So to be clear it is the minimum OA for ventilation that must be identical.
I am modelling a 6 storey office building which also has a basement car park. The basement car park is is naturally ventilated and also consists of a few small storage rooms, IT rooms and a security room. Under this current LEED effort we will be construction some showers in the basement. My question is should I also assign the ASHRAE Baseline system to this basement level of the building in the ASHRAE 90.1 energy model ?
Sounds like you have some conditioned spaces so yes.
Our project is a high rise building, which consists of offices, bank, dining area and so on. Now it is under the LEED V3 CS review. I have a question about the spaces which are not normally conditioned.
In our proposed building, kitchens are designed as unconditioned spaces, which only contain exhaust fans and supply fans. So I set these spaces as unconditioned zone in both proposed and baseline model, and put the fan power in the electric meter directly to calculate the energy cost of these fans.
The technical advice of reviewer told that an additional HVAC system type should be reflected in the baseline model for the kitchens. I know that according to the exception (b) of Section G3.1.1, additional system types must be included in the Baseline model if some spaces have occupancy or process loads or schedules that differ significantly from the rest of the building.(e.g., data/telecom rooms, kitchens, movie theaters), but in this project, the kitchens are unconditioned spaces, no cooling and heating system is used in the kitchen.
The question is that if I use system3 or system4 in the baseline model, can I keep the kitchens in the proposed model still as unconditioned spaces? Or should I add the same system in the proposed model?
I feel so confused about this question, looking forward to the help and advice
The Proposed gets modeled as designed according to G3.1-1 Proposed (a) so do not add a system to the kitchen.
Even though the kitchen does not have a separate conditioning unit perhaps it is considered indirectly conditioned (conditioned air coming from adjoining spaces) by the reviewer. Personally I think you might have a case for arguing that the baseline should not have a system since the proposed does not as this is the conservative approach. If you want to take this route I would suggest you contact the reviewer and make your case to be sure it will be OK before resubmitting. Alternatively add the system in the baseline to the kitchen. It will only increase your baseline energy use and therefore increase your savings.
Has anyone any feedback in modelling either of these two chillers in a 90.1 Energy model. Are people finding that the large fans in the dry air cooler adds a significant additional electrical consumption even if the COP / SEER of the water cooled chiller is higher. Any feedback would be great
This is with regard to an open air shopping plaza, which is registered as a group project with 7 structures.
We received guidance to follow the “Treatment of District or Campus Thermal Energy in LEED” documentation re: how to apply our district cooling energy efficiencies across one model. To clarify – that implies that our energy model should be a single model, for the entire area within our scope of work - correct? We were also informed to be sure to include all non-contiguous buildings that fall within our LEED project boundary (“ancillary” spaces such as storage or mechanical) into the designation of those Building which they serve. (eg: if the One building has a storage room located on the parking level, it should be allocated to the One Building, despite no physical connection).
When we document this, we foresee some confusion, as the Schedules on the Minimum Energy Performance Calculator are broken down by Area Served. For example, the Building 1 includes One Building (served by package units) as well as adjacent retail (served by central plant). Do we simply report this as such? For Building Two: this is a cold dark shell being served by further tenant HVAC, however it also has contiguous ancillary mechanical spaces served by the central plant. Does this get reported as two line items for one building (Building Two?)
And, with regard to the remaining spaces served by the central plant: Do we itemize each Building in the Schedule, or can the remaining buildings be grouped into one line items, with efficiencies averaged amongst the overall square footage? (Or is there another way to allocate the energy demands vs efficiencies besides square foot?)
Is there any scenario where we would need to create separate energy models for each building?
Thank you in advance!
If it is in all one certification then yes it could be one model. It could possible be separate models but I think would be easier to do the modeling as one with separate meters for each building. I think each building will need to demonstrate compliance with the minimum savings required.
As far as the forms go I could see that you will have some issues. In general you should report how it was modeled. You should provide a modeling narrative explaining some of the anomalies you will need to make the information fit in the form and when doing the modelings. Explanations go a long way in minimizing reviewer confusion.
You will probably need to report the total energy use in the form and then provide a breakdown of the energy use of each building in a separate document. You will probably also have to do this for the input summary tabs in the rest of the form too. I don't think that the form was created to easily accommodate multiple buildings.
I have calculated the U-ValueU-value describes how well a building element conducts heat. It measures the rate of heat transfer through a building element over a given area, under standardized conditions. The greater the U-value, the less efficient the building element is as an insulator. The inverse of (1 divided by) the U-value is the R-value. of a Slab on Grade Floor to be 0.12 (metric) using 100mm insulation. The Leed reviewer wants to see the F-Factor equivalent in agreement with ASHRAE 90.1 2007 Table A6.3 however the min horizontal insulation is 300mm (within this table) and it does not quote R values above R-2.6. Therefore there is no real direct match from this table that I can pick. What would be the best way to respond in this case. Will a calculated U-Value not suffice ?
ASHRAE doesn't really allow other calculation methods for F-Factors.
Since your 100mm thick insulation would adequate +/-Rsi-3.5, I suggest you use the F-Factor of Rsi 2.6 as there's not a major change in value for unheated slabs.
What's the width of your insulation?
Also, have a look at Figure 5-K in the 90.1 User's Manual to see if you have others options depending on your project specifics.
You can extrapolate from the tables or provide a similar calculation to the method used in the table.
LEED does allow other than F-factor calculations because some of the modeling software does not model F-factor.
Shall the PIU fans of System 8 cycle according to paragraph G220.127.116.11?
In EneryPlus you can impose the "Fan On Flow Fraction", which is defined as:
The fraction of the primary air flow at which fan turns on. In the parallel PIU the fan operation is intermittent. If the primary air flow is above this fraction of the maximum, the fan is off. Otherwise the secondary fan will run according to the Availability Schedule specified in the Fan:ConstantVolume object (see Fan Name below), unless it is overridden by an availability manager (ref. AvailabilityManager:NightCycle and others).
Could the "Fan On Flow Fraction" be equal to 0.5 and the fans be always available? In this way they are continuously on during the winter season and they turn off sometimes during the summer season (when more primary air is required).
The PIU fans should not cycle according to G18.104.22.168. This applies to the main fans in the air handling units.
The PIU fans should operate when the primary air flow has reached the minimum setting. The minimum flow is 30% as indicated in G22.214.171.124. So the fraction should be 0.3.
It means that during the winter season (when no cooling is requested) the PIU fan shall operate 24 hours/day, doesn't it?
It shouldn't. The PIU fan should cycle based on the temperature in the space. It should also be off when the space is unoccupied unless there is a call for heat. The main air handler fans should operate during occupied to meet the minimum outside air requirements.
This document on pages 3.97 to 3.98 explains how the system fan control should operate.
For a building I have to use the Building Area Method (ASHRAE 90.1-2007, 9.5.1) because some calculations were already developed through that method and now changing the method would be complicated (the building is very big). For retails, does the value provided in Table 9.5.1 consider also the lighting disigned and directed to highlight merchandise (e.g. in the shop windows)? I see this specification for the Space-by-Space method.
I would guess that it includes merchandise lighting. But it does not really matter. If you are using the BAM that is all you get. To get the extra display lighting allowance you must use the SBSSick building syndrome (SBS): Building whose occupants experience acute health and/or comfort effects that appear to be linked to time spent therein, but where no specific illness or cause can be identified. Complaints may be localized in a particular room or zone, or may spread throughout the building. A pattern of health complaints related to poor indoor air quality in a specific building, but without a known cause or a definite, diagnosable pattern of symptoms. method.
For the calculation of the % of energy cost influenced or directly controlled by CS Owner/Developer would the the latter be compared to the total energy cost of the proposed and not the baseline building? In other words do the relevant calculations refer to the proposed and not the baseline building?
Yes the Proposed.
We have an office core/shell project that we are considering for certification. The Owner may want to just design a small mechanical unit to service the restrooms and not much more. The future tenant would have to provide the mechanical system for the bulk of the building which would be outside our current scope. Is it possible to submit just the small unit for E and A credits? How would the energy model be handled?
Thank you for the assistance.
The fewer parameters that are designed, the more parameters are modeled identical to the baseline. In a cold/dark shell you would need to get enough savings from the envelop and any requirements in the tenant lease agreement. This type of project is harder but it is possible.
Cooling system in our project (shopping mall) consists of dry-coolers sprayed with water. What are ASHRAE efficiency requirements for dry-coolers? Should they be qualified as air-cooled condensers in Table 6.8.1G?
This sounds like an evaporative cooler which is covered in Table 6.8.1A.
I just wanted to clarify that these dry-coolers are providing chill for heat pumpA type of heating and/or cooling equipment that draws heat into a building from outside and, during the cooling season, ejects heat from the building to the outside. Heat pumps are vapor-compression refrigeration systems whose indoor/outdoor coils are used reversibly as condensers or evaporators, depending on the need for heating or cooling. In the 2003 CBECS, specific information was collected on whether the heat pump system was a packaged unit, residential-type split system, or individual room heat pump, and whether the heat pump was air source, ground source, or water source. units in tenant spaces. Cooling capacity of one dry-cooler is around 1500kW. I checked Table 6.8.1A and it seems that it covers smaller equipment. What do you think?
I think I don't really understand what type of equipment you are trying to find. Can you pass along more specific information of the equipment? It is certainly possible that the type of equipment is not covered by any of the 6.8.1 tables. If that is the case there is no minimum efficiency you would need to meet. This happens frequently with equipment that is not commonly used in the USA.
Dry-coolers are located on the roof of the building. Large fans create a forced airflow along heat exchangers. They are designed to provide cooling of Ethylene Glycol 35%. Additionally water is sprayed in the opposite direction to the air flow goiung through the coils in order to improve efficiency of the equipment. This system is then connected to the heat pumpA type of heating and/or cooling equipment that draws heat into a building from outside and, during the cooling season, ejects heat from the building to the outside. Heat pumps are vapor-compression refrigeration systems whose indoor/outdoor coils are used reversibly as condensers or evaporators, depending on the need for heating or cooling. In the 2003 CBECS, specific information was collected on whether the heat pump system was a packaged unit, residential-type split system, or individual room heat pump, and whether the heat pump was air source, ground source, or water source. units which provide air conditioning in tenant spaces.
The equipment is similar to this: http://www.luve.it/cms/view/prodotti/co2-refrigeration-systems-special-o...
Or should dry-coolers be qualified as cooling towers, do you have any thoughts on that? If not do you know who can I contact to confirm how this type of equipment should be qualified or to confirm that as you mentioned it's not covered by AHRAE?
Thanks the details help. It is heat rejection equipment but this particular type is not covered under 90.1-2007. It was added to Table 6.8.1g in 90.1-2010. So technically it does not have a minimum efficiency requirement under LEED 2009.
Thank you for your hepl!
I am working on a project, which is going for LEED C&S. The project has tenant occupied space, which has designed HVAC system for it. I want to know if there is any provision for modelling this system. Should I go for system as per design or as per baseline model?
Kindly tell me the provision given in LEED C&S for modelling HVAC systems for tenant occupied spacesOccupied Spaces are defined as enclosed spaces that can accommodate human activities. Occupied spaces are further classified as regularly occupied or non-regularly occupied spaces based on the duration of the occupancy, individual or multi-occupant based on the quantity of occupants, and densely or non-densely occupied spaces based upon the concentration of occupants in the space..
If the system is designed you can model it in the Proposed case. If the tenant system is not designed you model it the same as the baseline system.
The reference would be in 90.1-2007 Table G3.1-10 Proposed (a).
Hi, can you kindly clarify whether the glazing percentage and floor area for the base case needs to match the project case when reviewing compliance for EAp2?
Hi, I am new to LEED and looking at the energy model submitted by our consultant for the compliance on EAp2. I have a basic question. Should the base case scenario and the real project be modelled with the same percentage of glazing and floor area? When comparing the input data I see these values are very different. It would seem as if we were comparing apples with pears, as these are buildings with different amount of windows and floor area. This is a C&S certification. Thank you for your support!
Floor area should be identical. Window Wall Ratio (WWR) should also be identical unless it is over 40%, in which case base should be at 40% and proposed should reflect actual WWR.
I've done a number of Core and Shell models before, and always use the ACP calculator. However, something that I've noticed before but never understood is why the Revised Point threshold column is a single column and NOT separate revised thresholds for New and Existing. As an example: In a current project, I have a developer control percentage of 47%. It says that any savings over 13.8% gets you 6 pts. This is a nice drop from the 18% required for a non-ACP path to get 6 pts as a new construction project. However, the non-ACPT path for 6 pts requires a renovation project to have 14%. In other words, the ACP only lowers the 6 pt threshold from 14% to 13.8% for renovations. Why does this happen? Is it just something you have to live with for renovations? Or is there a way you can pro-rate this to be valid for existing building renovations? Thanks!
There are two cells at the top of the table. For an existing building with 47% control you would enter 0% in the % new construction cell and 47% in the control cell. You will then see a similar drop for the existing building threshold.
I have a question concerning the the function of a elevator lobby as a vestibule.
Regarding to Standard 90.1, every building entrance that separate cond. space from the exterior has to have an enclosed vestibule.
The question now is: Does a lift lobby function as an Standard 90.1-accepted vestibule if the door from the lobby to the exterior fulfills the mandatory door requirements and also the additional interior doors from the lobby to other building areas fulfill the requirements? Are there also requirments on the elevator door itself (air leakage, etc.)?
Sounds like it would comply. The elevator doors are not exterior so there is no leakage requirement.
So am I right in assuming that the Mandatory Provisions of ASHRAE Standard 90.1-2007 for 5.4.3 Air Leakage -> 126.96.36.199 Fenestration and Doors only apply to the exterior doors and windows of a vestibule and not for the inside doors/windows?
Are there any requirments on air leakage, etc. for the inside doors/windows of vestibules?
Yes I think that is correct.
Not that I know of.
Has anybody noticed issues with the Minimum Energy Performance Calculator for version 2009. I have noticed a few issues where the formulas don't work properly. For example it wont apply the Lighting Adjustments with Occupancy sensors are used. Will LEED except Table 1.4 instead as I have fill this out already for EAc1. It contains much of the same information.
Yes they will accept the prior version.
Do tankless Electrical water heaters have to comply with any efficiency requirements, in order to comply with the 7.4 mandatory provisions? On table 7.8 the performance requirements for electrical water heaters seem to depend of the rated volume.
No, they are not regulated.
I’m working in a Core & Shell building in Bogota, Colombia. The project was signed up in Leed Online in April 2016 (V3 – LEED 2009), therefore V07 form appears for EAp2 and V06 form for EAc1. In these forms I can’t mark that I’m going to use the Alternative Compliance Path (ACP EAp2-c1). How should I document the additional points? I have 15% of savings, which means 4 points, but if I use the ACP the project will get 17 points. Is the ACP integrated in the minimum energy performance calculator? If it is integrated, how should I use it?
It does not show up because the new forms were created for v4 and then revised for 2009. This ACP is not applicable to v4.
I would provide the spreadsheet along with a narrative explanation.
Thank you Marcus
As you know, in V05 form, projects not located in the United States were not able to get a Target Finder Score. In V07 form, must international projects use this tool?
LEEDuser is produced by BuildingGreen, Inc., with YR&G authoring most of the original content. LEEDuser enjoys ongoing collaboration with USGBC. Read more about our team
Copyright 2016 – BuildingGreen, Inc.