If your cleaning staff already keeps your building relatively clean, this credit—and the associated exemplary performanceIn LEED, certain credits have established thresholds beyond basic credit achievement. Meeting these thresholds can earn additional points through Innovation in Design (ID) or Innovation in Operations (IO) points. As a general rule of thumb, ID credits for exemplary performance are awarded for doubling the credit requirements and/or achieving the next incremental percentage threshold. However, this rule varies on a case by case basis, so check the credit requirements. point—should be easy to achieve. If performed professionally and objectively, the audit can help you evaluate the quality of your cleaning services and highlight areas of the building that present particular cleaning challenges.
This credit might initially strike your project team as an odd one, since it gives you the option of training in-house staff members to perform the audit without third-party oversight. To make sure you get the most out of your audit, however, make sure it is conducted objectively. It’s more valuable to your project to learn the truth about the quality of service delivered by your janitorial provider—whether that service is good or bad.
It can be difficult to maintain objectivity and assign numerical scores to something as seemingly subjective as cleanliness. The credit and APPA protocol provide a fairly objective framework for evaluating cleanliness, however, so you’ll have plenty of support to work with.
Determining how many rooms and how much square footage needs to be audited can also be a challenge.
The audit must occur during a period of normal operations when occupant loads and building activities reflect normal levels and patterns (the holidays would be a bad time, for example). The audit can be performed at any time during the day or night: it doesn’t have to be within normal business hours.
There’s no restriction to the number of audits you can perform. A preliminary audit is a great way to collect information and notify custodial and facilities staff of the building’s cleanliness before certification application. Just be sure to submit an audit that falls within the performance period for your LEED application.
A cleaning audit based on APPA guidelines should be conducted for your building interior at least once annually.
While the APPA guidelines were developed for educational facilities they still can be applied to a variety of building types. All projects pursuing this LEED credit, regardless of building type, must use the APPA guidelines.
The best way to quality control your audit is to have a third person trained in APPA protocol get involved. Have this person review the audit procedure and spot check a percentage of the audited spaces to ensure that the findings are appropriate and impartial.
No, perform the audit based on 10% of the total number of each space type within the entire building, regardless of which tenant occupies which space.
No, only audit spaces that are cleaned on a regular basis. Remember that if occupancy is below 50% during the performance period an audit cannot be conducted during that time.
You’re not required to purchase the guidelines, but it is worth considering if you plan on using in-house staff to conduct the audit. Training can consist of reading through the APPA guidelines, learning the benefits of honest audit results (such as pinpointing opportunities for improvement), and reviewing the forms. It’s up to your team to decide if the information available publicly is adequate for your team to conduct an audit.
Decide who will conduct the audit. You may choose one of the following paths:
Although you can use your current cleaning service provider, it’s not recommended. Even if you are happy with your current provider, they are less likely to provide an impartial audit, and you miss the benefit of a fresh set of eyes reviewing the cleanliness of the building.
Your project team can receive credit for a non-APPA audit that doesn't follow the exact APPA procedures, but you'll need to demonstrate that the audit was already in place prior to commencing work on your LEED application. Additionally, you must “demonstrate equivalence or superiority to the APPA procedures" in regards to the following key areas in the LEED application materials:
Alternative audit procedures present a challenge for reviewers in knowing whether they are as stringent as APPA. Teams that use other audit protocols must clearly demonstrate to the reviewer that their approach is valid and equivalent to the APPA protocol.
This credit is frequently pursued, because it’s very easy to earn as long as you’re willing to hire an auditor or take the time to conduct the audit yourself.
Remember that either in-house staff or an outside auditor will have to take the time to train, conduct the audit, and compile results. You’ll still save money by not hiring an outside auditor to do all of these things.
If you'd like to hire a third-party auditor to perform the audit but are having trouble tracking one down, contact cleaning service contractors that offer comprehensive, LEED-compliant, green cleaning programs. These service providers often offer a compliant auditing service. It is always suggested that you hire a contractor with a proven track record for submitting adequate LEED documentation. If your project team chooses a third-party auditor, you must provide a summary of the auditor’s professional credentials and experience.
If the audit is performed by two individuals—either from the project team or associated with the project building—this credit requires either one of the following:
Someone with cleaning expertise (such as a third-party auditor) is likely to work faster and more accurately than in-house staff.
Conducting an in-house audit requires staff time, and the feasibility of this depends on the size of your building. However, there should be no additional cost associated with this option.
If you decide to conduct the audit through your current cleaning service provider or a third-party auditor, you are likely to incur costs that increase in proportion to your building's square footage and number of rooms.
Determine the appropriate spaces to audit (such as offices, break rooms, and dining areas) and categorize the various spaces according to the APPA space types. If the APPA categories do not match your space, choose the listed category that is most similar. (See Figure 1, page 4, APPA Guidelines.)
You are only required to include space types that are cleaned on a regular basis. If you have storage areas, mechanical rooms, or any other spaces that are not cleaned regularly, you don't need to audit them. Therefore, the total area included in your square footage calculations for required audit space does not have to match the gross square-footage value you provided for other LEED credit submittals. In the provided tracking worksheet, the non-audited space can be entered to ensure that your project remains consistent with your other credit submittals. (See Documentation Toolkit.)
If you have space types in your project building that don’t fall into APPA categories, you can create your own and apply weightings to them. To create a weighting (each space type has elements such as floors, horizontal surfaces, and vertical surfaces that should be prioritized and “weighted” in the audit results), determine which components of the space type you clean most frequently and determine what percentage of time you spend cleaning each one. The percentage you come up with for each space-type component is the associated weighting. For example: If you have a medical treatment space in your building, you might determine that you spend:
To see how these and other weightings are used to calculate audit scores, see the Medical Treatment Room Audit Form in the APPA Audit Form workbook in the Documentation Toolkit. This template allows and encourages you to set your own weightings for spaces in your building.
Randomly select spaces to be audited, and ensure that each space type is sufficiently represented. APPA requires that you audit a number of rooms equivalent to at least 10% of each space type, and at least 10% of the total floor area of each space type. For any space types with fewer than five rooms, include all five rooms in the audit. (See the APPA Audit Form in the Documentation Toolkit, second tab, “roster of audit spaces” to help you figure out if the rooms you've selected collectively meet the requirements listed above.)
After randomly selecting the spaces to audit, print out the same number of forms as rooms, and fill out a form for each space type. (See instructions in the Documentation Toolkit.)
Conduct your audit using the forms provided in the Documentation Toolkit.
The following table outlines the levels (1–5) of cleanliness used to rate the components of each room (all taken from the APPA guidelines).
The custodial effectiveness audit should be performed during a period of normal business operations (although it need not be performed during business hours), when occupant loads and activities are anticipated to reflect normal levels and patterns. The auditors should not perform their inspection during the day, as custodial staff have no control over things like occupants leaving a mess at lunchtime. It makes more sense to audit relatively soon after the day's (or night's) cleaning is done so that you’re auditing the job done by the service provider rather than the messiness of the occupants.
The audit should not be announced to custodial staff or contractors. This will limit changes in standard practices in anticipation of the evaluation.
APPA estimates that no more than 10 minutes are required to assess any given room.
The audit is meant to help you improve your cleaning program. If you instruct your auditors to give each space a good score, you will not benefit from the honest results that will help you improve the cleanliness of the building.
Average the overall scores of the auditors to come up with a final score for the entire building. The sample size of audited space is in proportion to a space type’s prominence in the building, therefore no further normalizing based on square footage is necessary.
Conduct your cleaning audit early enough in the LEED project timeline so that if you score lower than expected, you can work with your provider to improve cleanliness levels and then re-audit. If your appearance level is between 2.1 and 3, you’ll earn one point. If you score a 2 or less, you can earn an additional point for exemplary performance.
The audit cannot be performed during times when occupancy is below 50%. If occupancy levels fluctuate during the performance period, be sure to conduct the audit when occupancy is above 50% or the results will not be eligible for this credit.
Excerpted from LEED 2009 for Existing Buildings: Operations & Maintenance
To reduce the exposure of building occupants and maintenance personnel to potentially hazardous chemical, biological and particulate contaminants, which adversely affect air quality, human health, building finishes, building systems and the environment, by implementing, managing and auditing cleaning procedures and processes.
Conduct an audit in accordance with APPA Leadership in Educational Facilities’ (APPA) “Custodial Staffing Guidelines” to determine the appearance level of the facility.
More information about the audit procedures is provided in the LEED Reference Guide for Green Building Operations & Maintenance, 2009 Edition.
Designate an individual or team to conduct a walk-through inspection of a sample of rooms in the building to evaluate the effectiveness of the cleaning program. Identify areas that fall below the owner’s expected standard and make improvements to the cleaning program accordingly.
APPA, formerly known as the Association of Physical Plant Administrators, is an association of more than 5,200 educational facility professionals at some 1,500 international institutions. The association promotes best practices in educational facilities by providing members with access to research, publications, professional development, and credentialing.
This spreadsheet categories dozens of specific space types according to how they should be applied under various IEQ credits. This document is essential if you have questions about how various unique space types should be treated.
Use this form to figure out which space types you will need to audit, how many rooms you will need to audit, and how much floor area of each type you’ll need to audit. Create and print audit forms for each room and aggregate results for reporting. This spreadsheet contains multiple worksheets — be sure to use the navigation options at the bottom of the window to view them all. The very first worksheet gives instructions for using the rest.
This document outlines the processes required for the APPA audit associated with this credit.
The following links take you to the public, informational versions of the dynamic LEED Online forms for each EBOMEBOM is an acronym for Existing Buildings: Operations & Maintenance, one of the LEED 2009 rating sytems.-2009 IEQ credit. You'll need to fill out the live versions of these forms on LEED Online for each credit you hope to earn.
Version 4 forms (newest):
Version 3 forms:
These links are posted by LEEDuser with USGBC's permission. USGBC has certain usage restrictions for these forms; for more information, visit LEED Online and click "Sample Forms Download."
This sample annotated LEED Online form demonstrates how to document IEQc3.2.
In LEEDuser's APPA audit form Excel worksheet under the General Building Information tab, there is a column labeled "Floor Type." What information about the space goes in this column? I am confused as to what the space's "floor type" is.
APPA distinguishes a few space categories by the type of floor in the space. For example, the Office space type is categorized by carpet floor or hard floor. Not all space types are broken out like this however, and Table IEQc3.2-1 on the LEED Credit Form can provide more information on which spaces should be scored separately based on floor type. The idea behind this is that the auditor should give a separate score for these spaces because the different floor types influence the cleaning requirements and potentially the appearance level. By scoring these spaces separately, auditors can better uncover targeted opportunities for improvement.
One thing to note is that APPA doesn't get more specific than carpet floor versus hard floor, so don't worry about categorizing spaces by the specific installed flooring like wood versus tile, etc.
As far as the LEEDuser audit worksheet goes, it can be useful to have a record of the floor type in each space so you can quickly and accurately transfer your APPA scores into the Credit Form.
Thanks LEEDuser for publishing credit achievement rates - should be very helpful for the industry to address gaps.
I find it curious that the achievement rate for this performance monitoring credit is 73%, while IEc3.1 Green CleaningGreen cleaning is the use of cleaning products and practices that have lower environmental impacts and more positive indoor air quality impacts than conventional products and practices. Program rate is only 57%. Are some project teams actually achieving high cleaning performance scores without implementing a green cleaning program?
The APPA audit doesn't take into account any sustainability factors, just the visual appearance level of interior spaces. So its likely that some teams have custodial programs that produce clean buildings, but they're not meeting (or choosing not to pursue) the requirements of a high-performance green cleaningGreen cleaning is the use of cleaning products and practices that have lower environmental impacts and more positive indoor air quality impacts than conventional products and practices. program per IEQc3.1.
We are considering to conduct an audit with in-house staff. They have already read the Guidelines, made their own forms according to the guidelines and did some tests.
To be compliant with LEED do we have to follow a specific training? APPA does not seem to offer training about these guidelines, neither the USGBC.
It sounds like you're on the right track. You're not required to take a formal training course offered by a third party. Check out the last FAQ above for more info.
Should the audit be strictly performed by only two (2) individuals then average their scores? Or it can be three or more?
The reference manual says 2. That said, there are potential benefits to using additional auditors. If the auditors are from the project team, then having an additional auditor (or two) would fulfill the requirement for a "postaudit quality control process to assure accurate results."
Of course if you are close to the line your results could be affected by your choice of auditors to use which would create something of a moral quandary...
We are undertaking the space inventory in advance of our audit. The building is a +/- 1,000,000 sf office tower. I'm wondering if the audit needs to include the loading dock area. This area is cleaned by our in-house dockmaster and not by the cleaning company hired to clean the rest of the building.
Patrick, that space should definitely be included. Who knows what kind of waste moves through there, and what diversion or reduction opportunities there might be? An audit will tell you.
How to calculate the average score for space type ?
Once you have established a raw score for each space (out of 100 based on APPA weightings) within a space type, you simply add all the raw scores for the spaces within a space type together and divide by the number of spaces you added together to get the average.
I am working on a building that includes a machine shop on the first floor that accounts for more than 10% of the total building area. Does the shop need to be included in the APPA audit?
Andy, in my experience shops areas like this oftentimes aren't regularly cleaned in the same way as office portions of the building, which would mean they do need to be included. Is this space regularly cleaned?
Thanks, Jenny. The shop is not regularly cleaned by the janitorial staff that cleans the rest of the building but is cleaned by the people that work in the shop. We went ahead and included the shop in the audit to make sure we had all of our bases covered.
Hello LEEDUser! I am working on a rather large building in NYC (2 million SF). They want to conduct an audit for IEQc3.2 but we are concerned about consistency. Here's why: 1) the building is too large to conduct a full audit in a timely manner with 2 people. Even starting first thing in the morning before occupants come to the building, we are still going to be auditing well into the evening hours which means that the spaces we get to later will be less clean because they will have been occupied all day. We may not even be able to complete the audit in under a day, which runs into more consistency issues. 2) we are considering using 2 teams of 2 auditors (4 people total) to get the job done faster to avoid this, BUT then we run into consistency issues with how the auditors are scoring and the fact that each team will only see half of the audited spaces. 2 teams will get the job done faster and all 4 people will receive the same APPA training. Is this an acceptable method? Has anyone ever conducted the audit like this? It seems like no matter what we do we are compromising the consistency of the audit. What do you recommend? Thank you!!
Alexis- do you still feel the building is too big even auditing only 10 of the spaces as allowed by APPA?
Yes, we are concernced about the size and consistency of the audit. We are definitely only going to audit 10% of the building but still...10% of 2mil is 200,000 SF!! I've done these audits myself in the past, and the most I've ever audited is 60,000SF and that took apprx 6 hours. Even with that size we were moving slightly faster than the APPA recommended 10 min per space. With 200,000 SF of space it would take about 20 hours to complete the audit with a single team moving at this pace (which is why we are proposing the 2 team approach). We are at odds here because if we move any faster than 10,000 SF an hour, we risk the integrity/thoroughness of the audit; if we move at 10,00SF an hour it will take a single team 2 10-hour days or 3 7-hour days to complete it; and if we use a 2 team approach then we risk consistency with scoring. Ideas? Thank you!!
We have a building that is not pursuing EQ3.1 because they're having trouble getting some tenants who use their own cleaning contractor on board with the building's approach. Is it still possible to achieve EQ3.2 ? As part of the cleaning audit, they still plan to audit tenant spaces, however some of these spaces (over 10%) are cleaned by a separate contractor who is not necessarily adhering perfectly to their green cleaningGreen cleaning is the use of cleaning products and practices that have lower environmental impacts and more positive indoor air quality impacts than conventional products and practices. policy. Thank you for any guidance!
IEQc3.1 is not a prerequisite for iEQc3.2. FYI, if it were, it would be stated in the credit language (see tab above).
I agree with Tristan, though if over 10% of the area is cleaned by a separate entity and they are not participating in the audit or responding to the audit results, I'm not sure it's legitimate to pursue the credit per its intent. Is the tenant contractor willing to participate to the extent that they will take into consideration / respond to any issues uncovered in the audit of the spaces they clean?
I recently received a clarification asking if all spaces within the building had been included in the audit, such as the restaurant, fitness center, and preschool space. In the past the audit has covered conference rooms, lobbies/entries, offices, corridors/ stairwells, storage, and washrooms. If a building has spaces such as the three mentioned above that do not perfectly match these descriptions, must they be audited as well, as their own category? I know you can exclude them, but if I did not want to go that route would they still have to be audited simply because they are different from the rest of the building? Thanks
My understanding that you should include all regularly cleaned spaces in the audit, except in the case of areas under separate management and are no more than 10% of the floor area. Even if there is not a predefined APPA category, you can still evaluate the space according to the protocol set forth in APPA.
I'm in a similar situation. I'm wondering what category to qualify a very large (almost entire first floor) data center under. Our thoughts are office or storage. Have their been any additional APPA guidelines created to fit unique spaces or are they just supposed to be audited using the criteria of the existing category that most closely resembles it? I've tried navigating the website for information on how to audit unique spaces, but come away empty handed.
AS APPA was designed for educational facilities there are many space types that are not covered. You can designate your own space types in performing the audit if none of the defined spaces appear to be relevant.
As long as the criteria that you use to judge the cleanliness of the space make sense then you are actually improving the results. Of course, now you have to think about what a clean data center looks like...
It appears that the guidelines references in the LEED 2009 manual have now been revised and are no longer available. Does anyone have any experience with the new updated (with revised title above?). I would rather avoid spending $110 on the wrong book!
Michael, I'm not familiar with the updated guidelines, but I suspect that there are enough tools on this site and info in the Reference Guide to successfully perform the audit per the old guidelines without purchasing the guide.
I have the same question as Michael : the Guidelines required for EBOMEBOM is an acronym for Existing Buildings: Operations & Maintenance, one of the LEED 2009 rating sytems. IEQ3.2 (APPA Custodial guidelines edition 2) are no longer available. In our case we don't have any of the guidelines. Should we buy the new edition though it isn't cited in the requirements?
We are intending to train 2 inhouse staff members to conduct an in-house audit, and the project will be an international LEED certification (so we will have to translate the documents)
Is there a digest of the edition 2 guidelines that we could use? I see below that Tristan suggests looking at the documentation toolkit which we will do, but any advice would be helpful.
Amanda- I do not have the third edition, but I just compared the table of contents of the third edition to the second edition that I have and they are VERY similar. I can't say for sure since I don't have the third edition, but if you don'r feel that the documentation toolkit gives you enough information I suspect that the third edition would work.
I'd like to share a recent reviewer comment. If we had not already achieved more than 60 points, I would have appealed this ruling, but it's not worth my time at this point.
"For future submittals, ensure that for any space types where 10% consists of fewer than five rooms, the required numberof rooms are audited."
This comment is not specific enough to sufficently document compliance in an appeal. It is the same comment from the prelim review, which we corrected by auditing additional spaces (example - all staircases, both elevators, and all restrooms). I am confused by what else could be missing. There are more than 5 workstations and conference rooms and we audited 10% of each. I think part of the problem is that the APPA space types do not match the space type inputs in PIF3, nor do they auto-fill. So for future projects, we are using the APPA space type as the starting point for defining regularly occupied space types for PIF3--this semes backwards for me.
Is there a more appropriate venue to make these comments on LEED forms? (besides feedback form on LO)
Lastly, beware of ranking your janitorial staff to high, we also got this comment, "It appears that each space received an average score of 1, which is atypical for a building with numerous spacetypes and for a building of this size. ... Please provide a clarification narrativedescribing the methods used to audit each space and confirming that each space type was assigned an accurate cleanliness score. Ensure that thenarrative confirms that the audit was conducted in accordance with APPA Custodial Staffing Guidelines to determine the appearance level of the facility."
I was offended by this comment. Our property manager pays a premium for premiumn cleaning services. I believe this credit has fundamental flaws in the documentation requirements.
Would it have been quesitoned if we used the leed user worksheet?
Alyson- did they actually deny the credit? Or just provide you with "helpful" advice for next time? I agree that the form for this one is frustrating. I do tend to use and submit a separate worksheet (whether is is LEEDuser's or a different one) to try to show exactly what we did.
Alyson, I'm not totally sure, but I think what they maybe have been communicating is that in cases when the number of rooms is greater than 5, but 10% of the number of rooms is less than 5, you must audit at least 5 rooms. For example, if you have 10 rooms, 10% is only 1, but to meet the rules in the RG you must audit 5. If you have fewer than 5 rooms, you have to audit the total number of rooms that exist.
Our client follows ISO 90001 audit guidelines (and has for years). The site team does an internal audit once a month, and conducts an ISO 90001 audit once a year. Can we submit our ISO audit information in lieu of an APPA audit?
You could attempt to submit the ISO 90001 audits as an alternate compliance path, but I don't believe that it would be accepted since the credit very specifically requires an APPA audit. I haven't tried this alternate compliance path for this credit, but have had other similar alternate compliance approach turned down.
Did you submit your alternate approach, and how is it accepted by the reviewer? I have also a alternative situation, with respect of the 10%/10% area/space type requirement, with the level equal to level 2 but with a statistical "# of accepted failures" before denial..
To whom it may concern,
I have a question that I did not find a solution to in the LEED EBOMEBOM is an acronym for Existing Buildings: Operations & Maintenance, one of the LEED 2009 rating sytems. Reference Guide or in the credit-by-credit forum on this website.
In the audit that will be made in the building, do I have to consider the garage areas? In the site plan there is a parking garage.
We have never audited garage spaces and been fine. That's never a 100% guarantee that they won't start requiring them in the future, but you should be OK not doing the garage.
Do spaces that are not regularly cleaned such as mechanical rooms and tenant storage rooms need to be counted as the 10% exempted? We have one tenant with their own custodial service declining to participate. When you add them to the areas I noted, the total is over 10%.
Mechanical rooms do not need to be audited, but storage rooms typically do. You may take a little bit of a hit on your average appearance levels by including storage rooms as required if they are not regularly cleaned, but it may not be enough to negatively impact your changes on this credit.
I am working with a client to identify which spaces in their building to audit and am curious if anyone has handled open workstations (i.e. cubes) differently than closed offices? What I would like to do is treat closed offices as one space category and open workstations as another space category. For open area workspaces, we would break the area into quadrants per floor. We would have the auditor(s) review at least 10% of the quadrants (by both area and number).
As an example, a floor has ten open areas with approximately 300 cubes on the floor (30 cubes/area). We would randomly select one of these areas and evaluate the cleanliness of the floors, horizontal & vertical services, lighting fixtures, and trash containers in that area. On the next floor, we would select an area on a different part of the floor to evaluate.
Katie- in the past I have always differentiated between open office and private office spaces, making sure that I audit at least 10% of each type. Your quadrant system sounds fine to me, you can also simplify even further by simply ensuring that you audit at least 10% of the open office space area.
Can someone please clarify the following points as the LEED forms seem to very confusing on the appropriate space to audit?
If there are less than five total spaces for a space type, you need to audit all spaces. Otherwise, you need to audit 10% of the total floor area of that space type.
Do you audit all rooms if there is less than 5, and if 10% of the rooms equate to less than 5, then you must audit at least 5 rooms?
If there are more than 5 spaces, then do you simply have to audit 10% of the total floor area, and 10% of the floor area for each space type, or do you also have to audit 10% of the total number of rooms for each space type?
If there are less than 5 spaces of any type, you must audit all spaces of that type. If there are more than 5 of any type of space you should audit 10% of the spaces or 5 spaces, whichever is larger.
If more than 5 spaces, audit 10% of the number of spaces. If your randomly selected 10% of the spaces do not equal at least 10% of the total area of that space type, add additional spaces until you also reach 10% of the area of that type.
If some tenants in a multi-tenant office building prefer to use their own cleaning service rather than the one the management uses on the rest of the building, can those spaces be excluded from the audit? If so, do they need to account for less than 10% of the total gross square footageSum of the floor areas of the spaces within the building including basements, mezzanine and intermediate-floored tiers, and penthouses with headroom height of 7.5 ft or greater. It is measured from the exterior faces of exterior walls or from the centerline of walls separating buildings, but excluding covered walkways, open roofed-over areas, porches and similar spaces, pipe trenches, exterior terraces or steps, chimneys, roof overhangs, and similar features. of the building? Or, if those tenants will allow it, can their spaces be included in the audit, and counted, even though they are not under the control of the management?
You should go ahead and include all of the spaces in the audit even if they are not under the control of the management. You may be able to exclude up to 10% (if you are not trying to exclude a different 10% for other credits), but the better solution is to go ahead and include the spaces.
We are preparing a LEED EB certification for a school and need an audit form for classroom areas. Is there one available for free or do we need to purchase the APPA Guidelines to get the audit forms for classrooms?
Brian- there may be some free forms floating around on the internet. I have also found that many janitorial companies have all of the forms and are willing to share. I would recommend purchasing the guide, though, if you think you may be doing more of these audits in the future.
I have about one million square feet of commercial office space that obviously includes mail rooms, entries, break rooms, small conference rooms, rest rooms, elevators, etc. Do I really need to measure each and every space to figure out total sq ft of each type? This could take weeks! Since it's all cleaned by the same crew can't I just do 10% of the total "Office" space?
Lee- In order to be in total compliance with the APPA guidelines, you would have to total up your actual square footage of each space type and then audit 10% (or at least five rooms) of each type, so 10% of breakrooms, 10% of copy areas, 10% of private office, 10% of conference rooms, etc. There may be some latitude in estimating the total square footage of spaces of each type, but lumping everything together as "office" will definitely not fly.
From doing the audit in the past, I can also tell you that cleaning crews do put more or less effort into certain types of spaces and have specific issues associated with certain types of areas (i.e. sticky floors in break rooms, dirty blinds in conference rooms or burnt out lights in restrooms). Consequently, part of the value of the information derived from the audit has to do with dividing the spaces into types.
If this credit is more labor intensive for your building type than you would like, there are always other credits you can pursue instead!
Anyone know where I can find the weighting factors for hotel guest rooms?
It's unlikely the weighting factors for hotel guest rooms are available in the APPA Guidelines as they were written for use in schools. Because APPA does not designate weighting factors for many room types in office buildings, hotels, convention facilities, etc., you're allowed to create your own factors. You can learn how to do this in the “Before the Performance Period” section on the “Checklists” tab.
I was wondering if it was necessary to purchase the Custodial Staffing Guidelines handbook or are the guidelines provided in the LEED reference guide and through LEEDuser enough to conduct the audit properly?
You certainly aren't required to purchase the APPA guidelines, and the LEED Reference Guide and the information provided above in LEEDuser, including the protocol in the Documentation Toolkit, may be enough.
However, you'd have to decide this for your project based on your team's comfort level and expertise.
Architect, Director of Sustainability
SHP Leading Design
A custodial audit will help you evaluate the effectiveness of your green cleaning policy.
You can evaluate the effectiveness of your green cleaning program through your custodial audit.
Auditing the effectiveness of your mat maintenance program will strengthen your approach to IEQc3.5.
LEEDuser is produced by BuildingGreen, Inc., with YR&G authoring most of the original content. LEEDuser enjoys ongoing collaboration with USGBC. Read more about our team
Copyright 2013 – BuildingGreen, Inc.