This prerequisite is a big one, not only because it’s required for all projects, but also because it feeds directly into EAc1: Optimize Energy Performance, where about a fifth of the total available points in LEED are at stake. Master these minimum requirements, and you can use the same compliance path as in EAp2 to earning points.
You won’t earn the prerequisite by accident, though. Although “energy efficiency” is on everyone’s lips, the mandatory and performance-based requirements for EAp2 go beyond code compliance in most places. That said, there is nothing to stop you from meeting the requirements with a reasonable amount of effort, and the environmental benefits as well as the operational cost savings are significant.
Most projects start by choosing which of the three available compliance paths to follow. We’ll look at them each in turn.
Option 1 alone gives you access to all of the points available through EAc1, and offers the most flexibility in giving you credit for innovative designs.
First, you need to meet the mandatory requirements of ASHRAE 90.1-2007 for all major components, including the envelope, HVAC, lighting, and domestic hot water. ASHRAE 90.1 has had some changes and new mandatory requirements since the 2004 version, which was referenced on previous LEED systems, so be sure to review the standard carefully.
Energy efficiency is an area where it behooves project teams to start early and work together to maximize savings. Playing catch-up later on can be costly.Second, you need to demonstrate a 10% savings (5% for existing buildings) for your designed building compared with a baseline case meeting the minimum requirements of ASHRAE 90.1 (or Title 24-2005, Part 6 for California projects). You do this by creating a computer model following rules described in Appendix G of ASHRAE 90.1.
Computer modeling offers the following key advantages:
Your building type may not have a choice—you may have to follow this path, because both Options 2 and 3 are prescriptive compliance paths that are only available to specific building types and sizes.
However, if your building type and size allow, and you don’t want to embark on the complex process of computer modeling, which also requires expert assistance from a modeler or from a member of the mechanical engineer’s team, the prescriptive compliance paths are a good way to earn the prerequisite simply by following a checklist.
Passive design strategies such as shading to reduce solar heat gain are the most cost-effective ways to improve energy performance.Note, however, that when you get to EAc1, there are a lot fewer points on the table for the prescriptive paths, and that you have to follow each prescriptive requirement. These paths also require more collaboration and focus early on in design than you might think. The design team must work together to integrate all of the prescriptive requirements, and Option 3 even requires documentation of certain design processes.
The Advanced Energy Design Guides are published by ASHRAE for office, warehouse, and retail projects less than 20,000 ft2—so if you don’t fall into one of those categories, you’re not eligible for this path.
These guides outline strategies to reduce energy use by 30% from 2001 levels, or an amount equivalent to approximately 10%–14% reduction from ASHRAE 90.1-2007. If you choose this compliance path, become familiar with the list of prescriptive requirements and commit to meeting all of them.
The Core Performance Guide path is a good option if all of the following are true:
Comply with all requirements within Sections 1 and 2 of the guide. If you choose this path, become familiar with the list of prescriptive requirements and commit to meeting them. Also note that it’s not just a list of prescriptive requirements, but a prescribed process for achieving energy efficiency goals. You must demonstrate that you considered a couple of alternate designs, for example, and that certain team meetings were held.
Energy efficiency offers a clear combination of environmental benefit and benefit to the owner through reduced operational expenses, and potentially reduced first costs, if you’re able to reduce the size and complexity of your HVAC system with a more efficient envelope.
High-tech HVAC systems, and onsite renewable energy generation are often signature components of green buildings, but consider these strategies more “icing” on the cake, rather than a place to start. Start with building orientation and passive design features first. Also look at envelope design, such as energy-efficient windows, walls and roof, before looking at HVAC and plug loads. A poorly designed envelope with a high-tech HVAC system is not, on the whole, efficient or cost-effective.
Projects connected to district energy systems will not be able to utilize the system efficiencies of the base plant to demonstrate compliance with the prerequisite. They can plan on benefiting from these systems under EAc1, however.
Focusing on energy efficiency and renewable energy generation can seem to add costs to a project, but there are a variety of utility-provided, as well as state, and federal incentives available to offset those premiums. (See Resources.)
Ideally if the software you are using cannot model a technology directly then seek a published workaround related to your software. If you can't find a published workaround then model it as you think it should be modeled and explain how you have modeled it in the preliminary LEED submission.
No, not if it is part of the LEED project. However, there is an exemption for existing building envelopes in Appendix G that allow you to model the existing condition in the baseline so you do not pay a penalty.
No, not for an existing building.
You must model accurately. Since you don't have enough savings in the building energy, find savings in the process. Either you will be able to demonstrate that compared to a conventional baseline the process being installed into the factory is demonstrably better than "similar newly constructed facilities," allowing you to claim some savings, or the owner needs to install some energy-saving measures into the process to get the project the rest of the way there. Either option can be difficult, but not impossible.
Account for process load reductions through the exceptional calculation method. A baseline must be established based on standard practice for the process in your location. Any claim of energy savings needs a thorough narrative explaining the baseline and the strategy for energy savings along with an explanation of how the savings were calculated.
It is common to have a 80%–90% process load in a manufacturing facility. The 25% default in LEED is based on office buildings. If you think your load is lower than 25%, it is recommended that you explain why in a short narrative. It is also recommended to briefly explain it if your load is 25% exactly, since that level commonly reveals that the process loads were not accurately represented.
The energy savings are based on the whole building energy use—building and process. LEED does not stipulate exactly where they come from.
For LEED 2009 you'll need touse 90.1-2007. There were some significant changes in 90.1-2010—too many to account for in your LEED review, and your project would also have a much harder time demonstrating the same percentage energy savings.
Yes according to LEED, although it is not recommended as a best practice, and it is usually more cost-effective to invest in energy savings in the building.
You can assume exterior lighting savings for canopies against the baseline, but not the shading effects of canopies.
If exterior lighting is present on the project site, consider it as a constant in both energy model cases.
Any conditioned area must be included in the energy model.
The Energy Star portion of the form does not apply to international projects.
Use the tables and definitions provided in 90.1 Appendix B to determine an equivalent ASHRAE climate zone.
International projects are not required to enter a Target Finder score. Target Finder is based on U.S. energy use data.
For Section 22.214.171.124c, a manual control device would be sufficient to comply with mandatory provisions.
Submitting these forms is not common; however, it can be beneficial if you are applying for any exceptions.
Use the building area method.
Although there is no formal list of approved simulation tools, there are a few requirements per G2.2.1, including the ability of the program to provide hourly simulation for 8760 hours per year, and model ten or more thermal zones, which PHPP does not meet.
The automated Trace 700 report provides less information than is requested by the Section 1.4 tables spreadsheet. The Section 1.4 tables spreadsheet must be completed.
Assign HVAC systems as per Appendix-G and Section 6 but set thermostatic setpointsSetpoints are normal operating ranges for building systems and indoor environmental quality. When the building systems are outside of their normal operating range, action is taken by the building operator or automation system. out of range so that systems never turn on.
If it is only used for backup and not for regular use such as peak shaving—no.
SHGC is not a mandatory provision so it is available for trade-off and can be higher than the baseline.
You generally wouldn't need to upload any documentation, but particularly for a non-U.S. project, it may help to provide a short narrative about what they are based on.
Discuss your project’s energy performance objectives, along with how those are shaping design decisions, with the owner. Record energy targets in the Owners Project Requirements (OPR) for the commissioning credits EAp1 and EAc3.
You won’t earn this prerequisite by accident. The energy efficiency requirements here are typically much more stringent than local codes, so plan on giving it special attention with your team, including leadership from the owner.
Consider stating goals in terms of minimum efficiency levels and specific payback periods. For example: “Our goal is to exceed a 20% reduction from ASHRAE 90.1, with all efficiency measures having a payback period of 10 years or less.”
Develop a precedent for energy targets by conducting research on similar building types and using the EPA’s Target Finder program. (See Resources.)
For Option 1 only, you will need to comply with the mandatory requirements of ASHRAE 90.1-2007, to bring your project to the minimum level of performance. The ASHRAE 90.1-2007 User’s Manual is a great resource, with illustrated examples of solutions for meeting the requirements.
ASHRAE 90.1-2007 has some additional requirements compared with 2004. Read through the standard for a complete update. The following are some samples.
The prerequisite’s energy-reduction target of 10% is not common practice and is considered beyond code compliance.
Indirect sunlight delievered through clerestories like this helps reduce lighting loads as well as cooling loads. Photo – YRG Sustainability, Project – Cooper Union, New York A poorly designed envelope with a high-tech HVAC system is not, on the whole, efficient or cost-effective. Start with building orientation and passive design features first when looking for energy efficiency. Also look at envelope design, such as energy-efficient windows, walls and roof, before looking at HVAC and plug loads. HVAC may also be a good place to improve performance with more efficient equipment, but first reducing loads with smaller equipment can lead to even greater operational and upfront savings. A poorly designed envelope with a high-tech HVAC system is not, on the whole, efficient or cost-effective.
Don’t plan on using onsite renewable energy generation (see EAc2) to make your building energy-efficient. It is almost always more cost-effective to make an efficient building, and then to add renewables like photovoltaics as the “icing” on the cake.
Some rules of thumb to reduce energy use are:
Find the best credit compliance path based on your building type and energy-efficiency targets. Use the following considerations, noting that some projects are more suited to a prescriptive approach than others.
Option 1: Whole Building Energy Simulation requires estimating the energy use of the whole building over a calendar year, using methodology established by ASHRAE 90.1-2007, Appendix G. Option 1 establishes a computer model of the building’s architectural design and all mechanical, electrical, domestic hot water, plug load, and other energy-consuming systems and devices. The model incorporates the occupancy load and a schedule representing projected usage in order to predict energy use. This compliance path does not prescribe any technology or strategy, but requires a minimum reduction in total energy cost of 10% (5% for an existing building), compared to a baseline building with the same form and design but using systems compliant with ASHRAE 90.1-2007. You can earn additional LEED points through EAc1 for cost reductions of 12% and greater (8% for existing buildings).
Option 2: Prescriptive Compliance Path: ASHRAE Advanced Energy Design Guide refers to design guides published by ASHRAE for office, school, warehouse, and retail projects. These guides outline strategies to reduce energy use by 30% from ASHRAE 90.1-2001 levels, or an amount equivalent to a 10%–14% reduction from the ASHRAE 90.1-2007 standard. If you choose this compliance path, become familiar with the list of prescriptive requirements and commit to meeting them. (See the AEDG checklist in the Documentation Toolkit.)
Option 3: Prescriptive Compliance Path: Advanced Buildings Core Performance Guide is another, more basic prescriptive path. It’s a good option if your project is smaller than 100,000 ft2, cannot pursue Option 2 (because there is not an ASHRAE guide for the building type), is not a healthcare facility, lab, or warehouse—or you would rather not commit to the energy modeling required for Option 1. Your project can be of any other building type (such as office or retail). To meet the prerequisite, you must comply with all requirements within Sections 1 and 2 of the guide. If you choose this path, become familiar with the list of activities and requirements and commit to meeting them. (See Resources for a link to the Core Performance Guide and the Documentation Toolkit for the checklist of prescriptive items.)
EAc1: Optimize Energy Performance uses the same structure of Options 1–3, so it makes sense to think about the credit and the prerequisite together when making your choice. In EAc1, Option 1 offers the potential for far more points than Options 2 and 3, so if you see your project as a likely candidate for earning those points, Option 1 may be best.
Hotels, multifamily residential, and unconventional commercial buildings may not be eligible for either Option 2 or Option 3, because the prescriptive guidance of these paths was not intended for them. Complex projects, unconventional building types, off-grid projects, or those with high energy-reduction goals are better off pursuing Option 1, which provides the opportunity to explore more flexible and innovative efficiency strategies and to trade off high-energy uses for lower ones.
If your project combines new construction and existing building renovation then whatever portion contains more than 50% of the floor area would determine the energy thresholds.
Options 2 and 3 are suitable for small, conventional building types that may not have as much to gain from detailed energy modeling with Option 1.
Meeting the prescriptive requirements of Options 2 and 3 is not common practice and requires a high degree of attention to detail by your project team. (See the Documentation Toolkit for the Core Performance Guide Checklist.) These paths are more straightforward than Option 1, but don’t think of them as easy.
Options 2 and 3 require additional consultant time from architects and MEP engineers over typical design commitment, which means higher upfront costs.
Option 1 references the mandatory requirements of ASHRAE 90.1-2007, which are more stringent than earlier LEED rating systems that referred to ASHRAE 90.1-2004.
Option 1 energy simulation provides monthly and annual operating energy use and cost breakdowns. You can complete multiple iterations, refining energy-efficiency strategies each time. Payback periods can be quickly computed for efficiency strategies using their additional first costs. A building’s life is assumed to be 60 years. A payback period of five years is considered a very good choice, and 10 years is typically considered reasonable. Consult the OPR for your owners’ goals while selecting your efficiency strategies.
Option 1 energy simulation often requires hiring an energy modeling consultant, adding a cost (although this ranges, it is typically on the order of $0.10–$0.50/ft2 depending on the complexity). However, these fees produce high value in terms of design and decision-making assistance, and especially for complex or larger projects can be well worth the investment.
All compliance path options may require both the architectural and engineering teams to take some time in addition to project management to review the prescriptive checklists, fill out the LEED Online credit form, and develop the compliance document.
The architect, mechanical engineer, and lighting designer need to familiarize themselves and confirm compliance with the mandatory requirements of ASHRAE 90.1-2007, sections 5–9.
Use simple computer tools like SketchUp and Green Building Studio that are now available with energy analysis plug-ins to generate a first-order estimate of building energy use within a climate context and to identify a design direction. Note that you may need to refer to different software may not be the one used to develop complete the whole building energy simulations necessary for LEED certification.
Energy modeling can inform your project team from the start of design. Early on, review site climate data—such as temperature, humidity and wind, available from most energy software—as a team. Evaluate the site context and the microclimate, noting the effects of neighboring buildings, bodies of water, and vegetation. Estimate the distribution of energy across major end uses (such as space heating and cooling, lighting, plug loads, hot water, and any additional energy uses), targeting high-energy-use areas to focus on during design.
Use a preliminary energy use breakdown like this one to identify target areas for energy savings.Perform preliminary energy modeling in advance of the schematic design phase kick-off meeting or design charrette. The energy use breakdown can help identify targets for energy savings and point toward possible alternatives.
For existing buildings, the baseline energy model can reflect the pre-renovation features like rather than a minimally ASHRAE-compliant building. This will help you achieve additional savings in comparison with the baseline.
Projects generating renewable energy onsite should use Option 1 to best demonstrate EAp2 compliance and maximize points under EAc1. Other options are possible but won’t provide as much benefit. Like any other project, model the baseline case as a system compliant with ASHRAE 90.1-2007, using grid-connected electricity, and the design case is an “as-designed” system also using grid-connected electricity. You then plug in 100% onsite renewable energy in the final energy-cost comparison table, as required by the performance rating method (PRM) or the modeling protocol of ASHRRAE 90.1 2007, Appendix G. (Refer to the sample PRM tables in the Documentation Toolkit for taking account of onsite renewable energy.
LEED divides energy-using systems into two categories:
The energy model itself will not account for any change in plug loads from the baseline case, even if your project is making a conscious effort to purchase Energy Star or other efficient equipment. Any improvement made in plug loads must be documented separately, using the exceptional calculation methodology (ECM), as described in ASHRAE 90.1-2007. These calculations determine the design case energy cost compared to the baseline case. They are included in the performance rating method (PRM) table or directly in the baseline and design case model.
Besides energy modeling, you may need to use the exceptional calculation methodology (ECM) when any of the following situations occur:
Some energy-modeling software tools have a daylight-modeling capability. Using the same model for both energy and IEQc8.1: Daylight and Views—Daylight can greatly reduce the cost of your modeling efforts.
Provide a copy of the AEDG for office, retail, or warehouse, as applicable, to each team member as everyone, including the architect, mechanical and electrical engineers, lighting designer, and commissioning agents, are responsible for ensuring compliance. These are available to download free from the ASHRAE website. (See Resources.)
Find your climate zone before attempting to meet any detailed prescriptive requirements. Climate zones vary by county, so be sure to select the right one. (See the Documentation Toolkit for a list of climate zones by county.)
Develop a checklist of all requirements, and assign responsible team members to accomplish them. Hold a meeting to walk the team through the AEDG checklist for your project’s climate zone. Clarify specific design goals and prescriptive requirements in the OPR for EAp1: Fundamental Commissioning.
Early access to the AEDG by each team member avoids last-minute changes that can have cascading, and costly, effects across many building systems.
The AEDG prescriptive requirements include:
If your project team is not comfortable following these guidelines, consider switching to Option 1, which gives you more flexibility.
Although Option 2 is generally lower cost during the design phase than energy modeling, the compliance path is top heavy—it requires additional meeting time upfront for key design members.
Provide a copy of the New Buildings Institute Advanced Buildings: Core Performance Guide to each team member. The guide is available to download free from the NBI website. (See Resources.)
The guide provides practical design assistance that can be used throughout the design process.
Walk your team through the project checklist to clarify design goals and prescriptive requirements.
The guide provides an outline for approaching an energy-efficient design, in addition to a list of prescriptive measures. The first of its three sections emphasizes process and team interaction rather than specific building systems or features. Advise the owner to read through the guide in order to understand what is required of the architect and engineers.
Section 1 in the guide focuses on best practices that benefit the project during the pre-design and schematic design stages, such as analyzing alternative designs and writing the owner’s project requirements (OPR).
Section 2 of the Core Performance Guide describes architectural, lighting, and mechanical systems to be included. Section 3 is not required for EAp2 but includes additional opportunities for energy savings that can earn EAc1 points.
The guide mandates that your team develop a minimum of three different design concepts to select from for best energy use.
Though they can be a little daunting at first glance, a majority of the guide’s requirements overlap with other LEED credits, such as EAp1: Fundamental Commissioning, IEQp1: Minimum Indoor Air Quality Performance, and IEQc6.1: Controllability of Systems—Lighting Controls.
This compliance path is top-heavy due to upfront consultant time, but it provides adequate structure to ensure that your project is in compliance with the prerequisite requirements. For some projects it may be less expensive to pursue than Option 1.
The owner should now have finalized the OPR with the support of the architect, as part of the commissioning credits EAp1 and EAc3. The goals identified here will help your team identify energy-reduction and occupant-comfort strategies.
Consider a broad range of energy-efficiency strategies and tools, including passive solar, daylighting, cooling-load reduction, and natural ventilation to reduce heating and cooling loads.
Develop the basis of design (BOD) document in conjunction with your mechanical engineer and architect for EAp1: Fundamental Commissioning, noting key design parameters to help strategize design direction as outlined in the OPR.
The OPR and BOD serve the larger purpose of documenting the owner’s vision and your team’s ideas to meet those goals. The BOD is intended to be a work-in-progress and should be updated at all key milestones in your project. Writing the document gives you an opportunity to capture the owner’s goals, whether just to meet the prerequisite or to achieve points under EAc1.
Confirm that your chosen compliance path is the most appropriate for your project, and make any changes now. Following a review with the design team and owner, ensure that everyone is on board with contracting an energy modeler for Option 1 or meeting all the prescriptive requirements under Options 2 or 3.
Sometimes teams change from Option 1 to Options 2 or 3 very late in the design phase for various reasons including not realizing the cost of energy modeling. Making that change is risky, though: the prescriptive paths are all-or-nothing—you must comply with every item, without exception. Evaluate each requirement and consult with the contractor and estimator to ensure the inclusion of all activities within project management.
To avoid costly, last-minute decisions, develop a comprehensive, component-based cost model as a decision matrix for your project. The model will help establish additional cost requirements for each energy conservation measure. It will also illustrate cost reductions from decreased equipment size, construction rendered unnecessary by energy conservation measures, and reduced architectural provisions for space and equipment access. (See the Documentation Toolkit for an example.)
Use envelope design and passive strategies to reduce the heating and cooling loads prior to detailed design of HVAC systems. Passive strategies can reduce heating and cooling loads, giving the engineer more options, including smaller or innovative systems.
Load reduction requires coordinated efforts by all design members including the architect, lighting designer, interior designer, information-technology manager, and owner.
Involving facilities staff in the design process can further inform key design decisions, helping ensure successful operation and low maintenance costs.
Encourage your design team to brainstorm design innovations and energy-reduction strategies. This provides a communication link among team members so they can make informed decisions.
More energy-efficient HVAC equipment can cost more relative to conventional equipment. However, by reducing heating and cooling loads through good passive design, the mechanical engineer can often reduce the size and cost of the system. Reduced system size can save money through:
Review case studies of similar energy-efficient buildings in the same climate to provide helpful hints for selecting energy-efficiency measures. For example, a building in a heating-dominated climate can often benefit from natural ventilation and free cooling during shoulder seasons. (See Resources for leading industry journals showcasing success stories around the country and internationally.)
The relationship between first costs and operating costs can be complex. For example, more efficient windows will be more expensive, but could reduce the size and cost of mechanical equipment. A more efficient HVAC system may be more expensive, but will reduce operating costs. Play around with variables and different strategies to get the right fit for the building and the owner’s goals as stated in the OPR.
Review and confirm compliance with the mandatory requirements of all the relevant sections of ASHRAE 90.1-2007
Trust your project’s energy modeling task to a mechanical firm with a proven track record in using models as design tools, and experience with your building type.
Contract an energy modeling team for the project. These services may be provided by the mechanical engineering firm on the design team or by an outside consultant. Software used for detailed energy use analysis and submitted for final LEED certification must be accepted by the regulatory authority with jurisdiction, and must comply with paragraph G2.2 of ASHRAE Standard 90.1-2007. Refer to Resources for a list of Department of Energy approved energy-analysis software that may be used for LEED projects.
Design team members, including the architect and mechanical engineer at a minimum, need to work together to identify a percentage improvement goal for project energy use over the ASHRAE 90.1-2007-compliant baseline model. The percentage should be at least 10% to meet the prerequisite.
Plan on initiating energy modeling during the design process, and use it to inform your design—preferably executing several iterations of the design as you improve the modeled energy performance.
Ask the modeling consultant to develop an annual energy-use breakdown—in order to pick the “fattest” targets for energy reduction. A typical energy-use breakdown required for LEED submission and ASHRAE protocol includes:
Identify critical areas in which to reduce loads. For example, in a data center, the plug loads are the largest energy load. Small changes in lighting density might bring down the energy use but represent only a small fraction of annual energy use.
Don't forget that LEED (following ASHRAE) uses energy cost and not straight energy when it compares your design to a base case. That's important because you might choose to use a system that burns natural gas instead of electricity and come out with a lower cost, even though the on-site energy usage in kBtus or kWhs is higher. Generally you have to specify the same fuel in your design case and in the base case, however, so you can't simply switch fuels to show a cost savings
Explore and analyze design alternatives for energy use analyses to compare the cost-effectiveness of your design choices. For example, do you get better overall performance from a better window or from adding a PV panel? Will demand-control ventilation outperform increased ceiling insulation?
Simple, comparative energy analyses of conceptual design forms are useful ways to utilize an energy model at this stage. Sample scenarios include varying the area of east-facing windows and looking at 35% versus 55% glazing. Each scenario can be ranked by absolute energy use to make informed decisions during the design stage.
If your project is using BIM software, the model can be plugged into the energy analysis software to provide quick, real-time results and support better decisions.
Model development should be carried out following the PRM from ASHRAE 90.1-2007, Appendix G, and the LEED 2009 Design and Construction Reference Guide, Table in EAc1. In case of a conflict between ASHRAE and LEED guidelines, follow LEED.
Projects using district energy systems have special requirements. For EAp2, the proposed building must achieve the 10% energy savings without counting the effects of the district generation system. To earn points in EAc1 you can take advantage of the district system’s efficiency, but you have to run the energy model again to claim those benefits (see EAc1 for details).
While you could run the required energy model at the end of the design development phase, simply to demonstrate your prerequisite compliance, you don’t get the most value that way in terms of effort and expense. Instead, do it early in the design phase, and run several versions as you optimize your design. Running the model also gives you an opportunity to make improvements if your project finds itself below the required 10% savings threshold.
The baseline model is the designed building with mechanical systems specified in ASHRAE 90.1-2007, Appendix G, for the specific building type, with a window-to-wall ratio at a maximum of 40%, and minimally code-compliant specifications for the envelope, lighting, and mechanical components. It can be developed as soon as preliminary drawings are completed. The baseline is compared to the design case to provide a percentage of reduction in annual energy use. To avoid any bias from orientation, you need to run the baseline model in each of the four primary directions, and the average serves as your final baseline figure.
The design-case is modeled using the schematic design, orientation, and proposed window-to-wall ratio—¬the model will return design-case annual energy costs. Earn points by demonstrating percentage reductions in annual energy costs from the design to the baseline case. EAp2 is achieved if the design case is 10% lower than the baseline in new construction (or 5% less in existing building renovations).
Provide as much project and design detail to the modeler as possible. A checklist is typically developed by the energy modeler, listing all the construction details of the walls, roof, slabs, windows, mechanical systems, equipment efficiencies, occupancy load, and schedule of operations. Any additional relevant information or design changes should be brought to the modeler’s attention as soon as possible. The more realistic the energy model is, the more accurate the energy use figure, leading to better help with your design.
Invite energy modelers to project meetings. An experienced modeler can often assist in decision-making during design meetings, even without running complete models each time.
All known plug loads must be included in the model. The baseline and design-case models assume identical plug loads. If your project is deliberately attempting to reduce plug loads, demonstrate this by following the exceptional calculation method (ECM), as described in ASHRAE 90.1-2007, G2.5. Incorporate these results in the model to determine energy savings.
For items outside the owner’s control—like lighting layout, fans and pumps—the parameters for the design and baseline models must be identical.
It can take anywhere from a few days to a few weeks to generate meaningful energy modeling results. Schedule the due dates for modeling results so that they can inform your design process.
Review the rate structure from your electrical utility. The format can inform your team of the measures likely to be most effective in reducing energy costs, especially as they vary over season, peak load, and additional charges beyond minimum energy use.
Performing a cost-benefit analysis in conjunction with energy modeling can determine payback times for all the energy strategies, helping the iterative design process.
Using energy modeling only to check compliance after the design stage wastes much of the value of the service, and thus your investment.
The architect and mechanical engineer should carefully read the applicable ASHRAE Advanced Energy Design Guide for office, warehouse, or retail projects, as applicable.
Keep the owner abreast of the design decisions dictated by the standard. Fill in the team-developed checklist, within the climate zone table’s prescribed requirements, with appropriate envelope improvements, system efficiencies, and a configuration that meets the standard requirements.
As a prescriptive path, this option relies heavily on following the requirement checklist, which is used throughout the design process to track progress. To assist design development, provide all critical team members—not limited to the architect, mechanical and electrical engineers, and lighting designer—with a checklist highlighting their appointed tasks.
The architect, mechanical engineer, and lighting designer need to discuss each requirement and its design ramifications. Hold these meetings every six to eight weeks to discuss progress and make sure all requirements are being met.
Confirm that your project team is comfortable with following all the prescribed requirements. If not, switch to Option 1: Whole Building Energy Simulation.
The LEED Online credit form does not specify how to document each prescriptive requirement because they are so different for each project; it only requires a signed confirmation by the MEP for meeting AEDG requirements. You still have to provide documentation. Submit your checklist of requirements, and supporting information for each item, through LEED Online to make your case. If your project fails to meet even one requirement, it will fail to earn the prerequisite, thus jeopardizing LEED certification.
Although energy modeling consultant costs are avoided by this option, additional staff time will be required to document and track compliance status, as compared with conventional projects.
Energy efficiency measures prescribed by the guide can be perceived as additional costs in comparison with conventional projects. However, they are easy to implement and are cost-effective pn the whole.
Become familiar with the Core Performance Guide early in the design phase to know the multiple requirements and all requisite documents.
Note that the guide demands additional time, attention, and integrated process from the design team as compared to conventional projects. It’s not just a list of prescriptive requirements, but a prescribed process for achieving energy efficiency goals. LEED Online documentation requires proof of all steps outlined in Sections 1 and 2, including three conceptual design options and meeting minutes. The project manager, architect, and mechanical engineer should read the complete Core Performance Guide carefully to know beforehand the prescriptive requirements in Sections 1 and 2.
The project manager must take responsibility for ensuring that the requirement checklist is on track.
For Section 3, the design team needs to identify three or more of the listed strategies as possible targets for the project.
Create a checklist of requirements and assign a responsible party to each item.
The Core Performance Guide requires an integrated design contributed by the architect, mechanical and electrical engineers, and lighting designer. The project manager must take responsibility for shepherding and documenting the collaborative process to demonstrate compliance.
A long documentation list can be overwhelming for your team, so create a detailed checklist with tasks delegated to individual team members, allowing each member to focus on assigned tasks. The checklist can function as a status tracking document and, finally, the deliverable for LEED Online.
The architect and engineer, and other project team members, continue to develop a high-performance building envelope with efficient mechanical and lighting systems.
Constant communication and feedback among project team members, owner, and if possible, operational staff, during design development can minimize construction as well as operational costs and keep your project on schedule.
If you change or go through value-engineering on any specifications, such as the solar-heat gain coefficient of glazing, for example, be aware of impacts on mechanical system sizing. Making changes like this might not pay off as much as it first appears.
Consider using building information modeling (BIM) tools to keep design decisions up to date and well documented for all team members.
Schedule delays can be avoided if all team members share their ideas and update documents during the design development process.
The modeler completes the energy analysis of the selected design and system and offers alternative scenarios for discussion. The modeler presents the energy cost reduction results to the team, identifying the LEED threshold achieved.
It’s helpful for the energy modeling report to include a simple payback analysis to assist the owner in making an informed decision on the operational savings of recommended features.
The architect and HVAC engineer should agree on the design, working with the cost estimator and owner.
Demonstrating reductions in non-regulated loads requires a rigorous definition of the baseline case. The loads must be totally equivalent, in terms of functionality, to the proposed design case. For example, reducing the number of computers in the building does not qualify as a legitimate reduction in non-regulated loads. However, the substitution of laptops for desktop computers, and utilization of flat-screen displays instead of CRTs for the same number of computers, may qualify as a reduction.
Residential and hospitality projects that use low-flow showers, lavatories, and kitchen sinks (contributing to WEp1) benefit from lower energy use due to reduced overall demand for hot water. However, for energy-savings calculations, these are considered process loads that must be modeled as identical in baseline and design cases, or you have the choice of demonstrating the savings with ECM for process loads.
Perform daylight calculations in conjunction with energy modeling to balance the potentially competing goals of more daylight versus higher solar-heat gain resulting in high cooling loads.
If your project is pursuing renewable energy, the energy generated is accounted for by using the PRM. These results provide information about whether the energy is contributing to EAc2: Onsite Renewable Energy.
A cost-benefit analysis can help the owner understand the return on investment of big-ticket, energy-conserving equipment that lowers operating energy bills with a quick payback.
Complete at least half of the energy modeling effort by the end of the design development stage. Help the design team to finalize strategy through intensive, early efforts in energy modeling. Once the team has a design direction, the modeler can develop a second model during the construction documents phase for final confirmation.
If pursuing ECM for non-regulated loads, calculate energy saving for each measure separately if you are, for example, installing an energy-efficient elevator instead of a typical one so that the reduction would contribute to total building energy savings. Calculate the anticipated energy use of the typical elevator in kBTUs or kWh. Using the same occupancy load, calculate the energy use of the efficient elevator. Incorporate the savings into design case energy use within the PRM. Refer to the ECM strategy for detailed calculation guidelines.
Ensure that all prescriptive requirements are incorporated into the design by the end of the design development stage.
Revisit the Advanced Energy Design Guides (AEDG) checklist to ensure that the design meets the prescriptive requirements.
The mechanical engineer, lighting consultant, and architect revisit the checklist for an update on the requirements and how they are being integrated into the design. All prescriptive requirements should be specifically incorporated into the design by the end of the design development phase.
The mechanical engineer and architect track the status of each requirement.
While the LEED Online credit form does not require detailed documentation for each Core Performance Guide requirement, it is important that each item be documented as required and reviewed by the rest of the team to confirm compliance, especially as further documentation may be requested by during review. Your design team should work with the owner to identify cost-effective strategies from Section 3 that can be pursued for the project.
Construction documents clearly detail the architectural and mechanical systems that address energy-efficiency strategies.
Confirm that specifications and the bid package integrate all equipment and activities associated with the project.
If the project goes through value engineering, refer to the OPR and BOD to ensure that no key comfort, health, productivity, daylight, or life-cycle cost concerns are sacrificed.
During the budget estimating phase, the project team may decide to remove some energy-saving strategies that have been identified as high-cost items during the value-engineering process. However, it is very important to help the project team understand that these so-called add-ons are actually integral to the building’s market value and the owner’s goals.
Removing an atrium, for example, due to high cost may provide additional saleable floor area, but may also reduce daylight penetration while increasing the lighting and conditioning loads.
Although this prerequisite is a design-phase submittal, it may make sense to submit it, along with EAc1, after construction. Your project could undergo changes during construction that might compel a new run of the energy model to obtain the latest energy-saving information. Waiting until the completion of construction ensures that the actual designed project is reflected in your energy model.
Create a final energy model based completely on construction document drawings—to confirm actual energy savings as compared to ASHRAE 90.1-2007 requirements. An energy model based on the construction documents phase will provide realistic energy-cost savings and corresponding LEED points likely to be earned.
Make sure the results fit the LEED Online credit form requirements. For example, the unmet load hours have to be less than 300 and process loads will raise a red flag if they’re not approximately 25%. If any of the results are off mark, take time to redo the model. Time spent in design saves more later on in the LEED review process.
Finalize all design decisions and confirm that you’ve met all of the prescriptive requirements. Your team must document the checklist with relevant project drawings, including wall sections, specifications, and the MEP drawing layout.
Value engineering and other factors can result in design changes that eliminate certain energy features relevant to the prerequisite. As this compliance path is prescriptive, your project cannot afford to drop even one prescribed item.
Value engineering and other factors can result in design changes that eliminate certain energy features relevant to the credit. As this compliance path is prescriptive, your project cannot afford to drop even one listed item. Although perceived as high-cost, prescriptive requirements lower energy costs during operation and provide a simple payback structure.
The architect and mechanical engineer review the shop drawings to confirm the installation of the selected systems.
The commissioning agent and the contractor conduct functional testing of all mechanical equipment in accordance with EAp1: Fundamental Commissioning and EAc3: Enhanced Commissioning.
Find your Energy Star rating with EPA’s Target Finder tool if your building type is in the database. Input your project location, size, and number of occupants, computers, and kitchen appliances. The target may be a percentage energy-use reduction compared to a code-compliant building, or “anticipated energy use” data from energy model results. Add information about your fuel use and rate, then click to “View Results.” Your Target Finder score should be documented at LEED Online.
Plan for frequent site visits by the mechanical designer and architect during construction and installation to make sure construction meets the design intent and specifications.
Emphasize team interaction and construction involvement when defining the project scope with key design team members. Contractor and designer meetings can help ensure correct construction practices and avoid high change-order costs for the owner.
Subcontractors may attempt to add a premium during the bidding process for any unusual or unknown materials or practices, so inform your construction bidders of any atypical design systems at the pre-bid meeting.
The energy modeler ensures that any final design changes have been incorporated into the updated model.
Upon finalizing of the design, the responsible party or energy modeler completes the LEED Online submittal with building design inputs and a PRM result energy summary.
Although EAp2 is a design phase submittals, it may make sense to submit it (along with EAc1) after construction. Your project could undergo changes during construction that might require a new run of the energy model. Waiting until the completion of construction ensures that your actual designed project is reflected. On the other hand, it gives you less opportunity to respond to questions that might come up during a LEED review.
Include supporting documents like equipment cut sheets, specifications and equipment schedules to demonstrate all energy efficiency measures claimed in the building.
It common for the LEED reviewers to make requests for more information. Go along with the process—it doesn’t mean that you’ve lost the credit. Provide as much information for LEED Online submittal as requested and possible.
The design team completes the LEED Online documentation, signing off on compliance with the applicable AEDG, and writing the narrative report on the design approach and key highlights.
During LEED submission, the project team needs to make an extra effort to support the prerequisite with the completed checklist and the required documents. Although the LEED rating system does not list detailed documentation, it is best practice to send in supporting documents for the prescriptive requirements from the AEDG. The supporting documents should include relevant narratives, wall sections, mechanical drawings, and calculations.
Although the LEED Online sign-off does not include a checklist of AEDG requirements, it assumes that the team member is confirming compliance with all detailed requirements of the guide.
The design team completes the LEED Online credit form, signing off on compliance with the Core Performance Guide, and writing the narrative report on the design approach and key highlights.
During LEED submission, your project team needs to make an extra effort to support the prerequisite with the completed checklist and the required documents. Although not every requirement may be mentioned in the LEED documentation, the supporting documents need to cover all requirements with narratives, wall sections, mechanical drawings, and calculations.
Many of this option’s compliance documents are common to other LEED credits or design documents, thus reducing duplicated efforts.
Develop an operations manual with input from the design team in collaboration with facility management and commissioning agent if pursuing EAc3: Enhanced Commissioning.
The benefit of designing for energy efficiency is realized only during operations and maintenance. Record energy use to confirm that your project is saving energy as anticipated. If you are not pursuing EAc5: Measurement and Verification, you can implement tracking procedures such as reviewing monthly energy bills or on-the-spot metering.
Some energy efficiency features may require special training for operations and maintenance personnel. For example, cogeneration and building automation systems require commissioning and operator training. Consider employing a trained professional to aid in creating operation manuals for specialty items.
Energy-efficiency measures with a higher first cost often provide large savings in energy use and operational energy bills. These credit requirements are directly tied to the benefits of efficient, low-cost operations.
Excerpted from LEED 2009 for New Construction and Major Renovations
To establish the minimum level of energy efficiency for the proposed building and systems to reduce environmental and economic impacts associated with excessive energy use.
Demonstrate a 10% improvement in the proposed building performance rating for new buildings, or a 5% improvement in the proposed building performance rating for major renovations to existing buildings, compared with the baseline building performanceBaseline building performance is the annual energy cost for a building design, used as a baseline for comparison with above-standard design. rating.
Calculate the baseline building performance rating according to the building performance rating method in Appendix G of ANSI/ASHRAE/IESNA Standard 90.1-2007 (with errata but without addenda1) using a computer simulation model for the whole building project. Projects outside the U.S. may use a USGBC approved equivalent standard2.
Appendix G of Standard 90.1-2007 requires that the energy analysis done for the building performance rating method include all energy costs associated with the building project. To achieve points using this credit, the proposed design must meet the following criteria:
For the purpose of this analysis, process energy is considered to include, but is not limited to, office and general miscellaneous equipment, computers, elevators and escalators,kitchen cooking and refrigeration, laundry washing and drying, lighting exempt from the lighting power allowance (e.g., lighting integral to medical equipment) and other (e.g., waterfall pumps).
Regulated (non-process) energy includes lighting (for the interior, parking garage, surface parking, façade, or building grounds, etc. except as noted above), heating, ventilation and air conditioning (HVAC) (for space heating, space cooling, fans, pumps, toilet exhaust, parking garage ventilation, kitchen hood exhaust, etc.), and service water heating for domestic or space heating purposes.
Process loads must be identical for both the baseline building performance rating and the proposed building performance rating. However, project teams may follow the exceptional calculation method (ANSI/ASHRAE/IESNA Standard 90.1-2007 G2.5) or USGBC approved equivalent to document measures that reduce process loads. Documentation of process load energy savings must include a list of the assumptions made for both the base and the proposed design, and theoretical or empirical information supporting these assumptions.
Projects in California may use Title 24-2005, Part 6 in place of ANSI/ASHRAE/IESNA Standard 90.1-2007 for Option 1.
Comply with the prescriptive measures of the ASHRAE Advanced Energy Design Guide appropriate to the project scope, outlined below. Project teams must comply with all applicable criteria as established in the Advanced Energy Design Guide for the climate zoneOne of five climatically distinct areas, defined by long-term weather conditions which affect the heating and cooling loads in buildings. The zones were determined according to the 45-year average (1931-1975) of the annual heating and cooling degree-days (base 65 degrees Fahrenheit). An individual building was assigned to a climate zone according to the 45-year average annual degree-days for its National Oceanic and Atmospheric Administration (NOAA) Division. in which the building is located. Projects outside the U.S. may use ASHRAE/ASHRAE/IESNA Standard 90.1-2007 Appendices B and D to determine the appropriate climate zone.
The building must meet the following requirements:
Comply with the prescriptive measures identified in the Advanced Buildings™ Core Performance™ Guide developed by the New Buildings Institute. The building must meet the following requirements:
Projects outside the U.S. may use ASHRAE/ASHRAE/IESNA Standard 90.1-2007 Appendices B and D to determine the appropriate climate zone.
Projects in Brazil that are certified at the “A” level under the Regulation for Energy Efficiency Labeling (PBE Edifica) program for all attributes (Envelope, Lighting, HVAC) achieve this prerequisite. The following building types cannot achieve this prerequisite using this option: Healthcare, Data Centers, Manufacturing Facilities, Warehouses, and Laboratories.
1Project teams wishing to use ASHRAE approved addenda for the purposes of this prerequisite may do so at their discretion. Addenda must be applied consistently across all LEED credits.
2 Projects outside the U.S. may use an alternative standard to ANSI/ASHRAE/IESNA Standard 90.1-2007 if it is approved by USGBC as an equivalent standard using the process identified in the LEED 2009 Green Building Design and Construction Global ACP Reference Guide Supplement.
Design the building envelope and systems to meet baseline requirements. Use a computer simulation model to assess the energy performance and identify the most cost-effective energy efficiency measures. Quantify energy performance compared with a baseline building.
If local code has demonstrated quantitative and textual equivalence following, at a minimum, the U.S. Department of Energy (DOE) standard process for commercial energy code determination, then the results of that analysis may be used to correlate local code performance with ANSI/ASHRAE/IESNA Standard 90.1-2007. Details on the DOE process for commercial energy code determination can be found at http://www.energycodes.gov/implement/ determinations_com.stm.
1 Project teams wishing to use ASHRAE approved addenda for the purposes of this prerequisite may do so at their discretion. Addenda must be applied consistently across all LEED credits.
2 Projects outside the U.S. may use an alternative standard to ANSI/ASHRAE/IESNA Standard 90.1‐2007 if it is approved by USGBC as an equivalent standard using the process located at www.usgbc.org/leedisglobal
This database shows state-by-state incentives for energy efficiency, renewable energy, and other green building measures. Included in this database are incentives on demand control ventilation, ERVs, and HRVs.
Useful web resource with information on local/regional incentives for energy-efficiency programs.
ACEEE is a nonprofit organization dedicated to advancing energy efficiency through technical and policy assessments; advising policymakers and program managers; collaborating with businesses, public interest groups, and other organizations; and providing education and outreach through conferences, workshops, and publications.
The New Buildings Institute is a nonprofit, public-benefits corporation dedicated to making buildings better for people and the environment. Its mission is to promote energy efficiency in buildings through technology research, guidelines, and codes.
The Building Energy Codes program provides comprehensive resources for states and code users, including news, compliance software, code comparisons, and the Status of State Energy Codes database. The database includes state energy contacts, code status, code history, DOE grants awarded, and construction data. The program is also updating the COMcheck-EZ compliance tool to include ANSI/ASHRAE/IESNA 90.1–2007. This compliance tool includes the prescriptive path and trade-off compliance methods. The software generates appropriate compliance forms as well.
Research center at RPI provides access to a wide range of daylighting resources, case studies, design tools, reports, publications and more.
International association of energy modelers with various national and local chapters.
Non-profit organization aiming at design community to increase collaboration for designing energy efficient buildings.
The Low Impact Hydropower Institute is a non-profit organization and certification body that establishes criteria against which to judge the environmental impacts of hydropower projects in the United States.
The Building Technologies Program (BTP) provides resources for commercial and residential building components, energy modeling tools, building energy codes, and appliance standards including the Buildings Energy Data Book, High Performance Buildings Database and Software Tools Directory.
This website discusses the step-by-step process for energy modeling.
This online resource, supported by Natural Resources Canada, presents energy-efficient technologies, strategies for commercial buildings, and pertinent case studies.
This website is a comprehensive resource for U.S. Department of Energy information on energy efficiency and renewable energy and provides access to energy links and downloadable documents.
Information on cogenerationThe simultaneous production of electric and thermal energy in on-site, distributed energy systems; typically, waste heat from the electricity generation process is recovered and used to heat, cool, or dehumidify building space. Neither generation of electricity without use of the byproduct heat, nor waste-heat recovery from processes other than electricity generation is included in the definition of cogeneration., also called combined heat and power, is available from EPA through the CHPCombined heat and power (CHP), or cogeneration, generates both electrical power and thermal energy from a single fuel source. Partnership. The CHP Partnership is a voluntary program seeking to reduce the environmental impact of power generation by promoting the use of CHP. The Partnership works closely with energy users, the CHP industry, state and local governments, and other clean energy stakeholders to facilitate the development of new projects and to promote their environmental and economic benefits.
Free download of AHSRAE energy savings guide, use for Option 2.
Research warehouse for strategies and case studies of energy efficiency in buildings.
An online window selection tool with performance characteristics.
This website lays out design process for developing an energy efficient building.
This website discusses ways to improve design for lower energy demand as they relate to the AIA 2030 challenge.
This website includes discussion of design issues, materials and assemblies, window design decisions and case studies.
This site lists multiple web-based and downloadable tools that can be used for energy analyses.
This database is maintainted by the California Energy Commission and lists resources related to energy use and efficiency.
Energy design tools are available to be used for free online or available to download.
This website lists performance characteristics for various envelope materials.
This is an online forum of discussion for energy efficiency, computer model software users.
Target Finder is a goal-setting tool that informs your design team about their project’s energy performance as compared to a national database of projects compiled by the EPA.
This directory provides information on 406 building software tools for evaluating energy efficiency, renewable energy, and sustainability in buildings.
Weather data for more than 2100 locations are available in EnergyPlus weather format.
Weather data for U.S. and Non-U.S. locations in BIN format.
A web-based, free content project by IBPSA-USA to develop an online compendium of the domain of Building Energy Modeling (BEM). The intention is to delineate a cohesive body of knowledge for building energy modeling.
A guide for achieving energy efficiency in new commercial buildings, referenced in the LEED energy credits.
This manual is a strategic guide for planning and implementing energy-saving building upgrades. It provides general methods for reviewing and adjusting system control settings, plus procedures for testing and correcting calibration and operation of system components such as sensors, actuators, and controlled devices.
This document is USGBC’s second (v2.0) major release of guidance for district or campus thermal energy in LEED, and is a unified set of guidance comprising the following an update to the original Version 1.0 guidance released May 2008 for LEED v2.x and the initial release of formal guidance for LEED v2009.
This manual offers guidance to building energy modelers, ensuring technically rigorous and credible assessment of energy performance of commercial and multifamily residential buildings. It provides a streamlined process that can be used with various existing modeling software and systems, across a range of programs.
Chapter 19 is titled, “Energy Estimating and Modeling Methods”. The chapter discusses methods for estimating energy use for two purposes: modeling for building and HVAC system design and associated design optimization (forward modeling), and modeling energy use of existing buildings for establishing baselines and calculating retrofit savings (data-driven modeling).
Required reference document for DES systems in LEED energy credits.
ASHRAE writes standards for the purpose of establishing consensus for: 1) methods of test for use in commerce and 2) performance criteria for use as facilitators with which to guide the industry.
Energy statistics from the U.S. government.
This guide includes instructional graphics and superior lighting design solutions for varying types of buildings and spaces, from private offices to big box retail stores.
This website offers information on energy efficiency in buildings, highlighting success stories, breakthrough technology, and policy updates.
Bimonthly publication on case studies and new technologies for energy efficiency in commercial buildings.
AIA publication highlighting local and state green building incentives.
2008 guidelines and performance goals from the National Science and Technology Council.
Information about energy-efficient building practices available in EDR's Design Briefs, Design Guidelines, Case Studies, and Technology Overviews.
DOE tools for whole building analyses, including energy simulation, load calculation, renewable energy, retrofit analysis and green buildings tools.
This is a computer program that predicts the one-dimensional transfer of heat and moisture.
DesignBuilder is a Graphical User Interface to EnergyPlus. DesignBuilder is a complete 3-D graphical design modeling and energy use simulation program providing information on building energy consumption, CO2Carbon dioxide emissions, occupant comfort, daylighting effects, ASHRAE 90.1 and LEED compliance, and more.
IES VE Pro is an integrated computing environment encompassing a wide range of tasks in building design including model building, energy/carbon, solar, light, HVAC, climate, airflow, value/cost and egress.
Use this checklist of prescriptive requirements (with sample filled out) to have an at-a-glance picture of AEDG requirements for Option 2, and how your project is meeting them.
This spreadsheet lists all the requirements for meeting EAp2 – Option 3 and and EAc1 – Option 3. You can review the requirements, assign responsible parties and track status of each requirement through design and construction.
Sometimes the energy simulation software being used to demonstrate compliance with Option 1 doesn't allow you to simulate key aspects of the design. In this situation you'll need to write a short sample narrative, as in these examples, describing the situation and how it was handled.
In your supporting documentation, include spec sheets of equipment described in the Option 1 energy model or Options 2–3 prescriptive paths.
This is a sample building energy performance and cost summary using the Performance Rating Method (PRM). Electricity and natural gas use should be broken down by end uses including space heating, space cooling, lights, task lights, ventilation fans, pumps, and domestic hot water, at the least.
Option 1 calculates savings in annual energy cost, but utility prices may vary over the course of a year. This sample demonstrates how to document varying electricity tariffs.
This graph, for an office building design, shows how five overall strategies were implemented to realize energy savings of 30% below an ASHRAE baseline. (From modeling conducted by Synergy Engineering, PLLC.)
The climate zones shown on this Department of Energy map are relevant to all options for this credit.
This spreadsheet, provided here by 7group, can be used to calculate the fan volume and fan power for Appendix G models submitted for EAp2/EAc1. Tabs are included to cover both ASHRAE 90.1-2004 and 90.1-2007 Appendix G methodologies.
The following links take you to the public, informational versions of the dynamic LEED Online forms for each NC-2009 EA credit. You'll need to fill out the live versions of these forms on LEED Online for each credit you hope to earn.
Version 4 forms (newest):
Version 3 forms:
These links are posted by LEEDuser with USGBC's permission. USGBC has certain usage restrictsions for these forms; for more information, visit LEED Online and click "Sample Forms Download."
Documentation for this credit can be part of a Design Phase submittal.
Thanks a lot Marcus.
According to 126.96.36.199 (mandatory provision) enclosed vestibules shall protect building entrances that separate the conditioned space from the exterior. In the building that I’m considering, a factory, a huge space is occupied for the production and it is conditioned. There are big doors where trucks can enter the building. Shall those entrances have enclosed vestibules or could some exception exclude them? Could air curtains (“air doors”) be used as alternative option? Since they would be used by trucks, the vestibules would occupy a big area. Regards
I think this applies to primary pedestrian entrances only.
It is necessary to prove the power density in external illuminations with the following characteristics:
- Accent lighting (lighting focused on plants and trees)
- Lighting for visual communication
These lights are not part of the load of lighting design.
Should I consider them as exceptions, correct?
There is a list of exceptions in 9.4.5. I do not see anything on the list that would exempt the accent lighting. The lighting for visual communication might be under a, b, or c?
You can exempt those exceptions listed from the requirements of the standard but you still must include them in your energy models as identical process loads.
I believe these fixtures focused on plants and trees, do not make sense considering the illuminated area. Made this analysis and the power of the baseline was much higher compared to the proposed.
I think in this case the best option is to consider according to what you said. Identical process loads.
Lights for visual communication, I think in some cases can be considered both in Option A, as in Option B.
If you are exempting any exterior lighting you will need to cite an exception in order to consider it a process load. Other wise this lighting goes in the Proposed and not the Baseline.
Marcus, thank you.
Now I understand. I will follow with this parameter.
Hi everyone! I've some doubts about this points.
Whats is the setback temperatures?
The time setpoint not met is calculated only in the occupied hours? I ask this because the air conditioning in my building works at the same time that the time of occupation.
How can I prove these hours when there is no air conditioning in unoccupied schedules?
My energy simulation software presents a summary of the LEED only with "setpoint team not met" in time of occupation however, I received a question about the hours of non-occupation.
Setpoint does not work in that time has no occupation.
Setback generally refers to the adjustment of temperature settings during unoccupied periods.
Unmet load hours could possible occur at any time but they are far more likely during occupied periods.
If the air conditioning is shut off during unoccupied hours and the temperature settings in the model reflect this sequence then you should not generate any unmet load hours.
Sounds like maybe you need to enter a very high set point that would never be reached during unoccupied hours.
I'm considering a "Multi-purpose indoor unit for use in 4-pipe systems for the simultaneous production of chilled and hot water by means of two independent water circuits". The unit transfers heat from a chilled water loop to a heated water loop. If the requests of heated water and chilled water are not balanced, then heat is exchanged with ambient air.
What mandatory provisions shall such a system respect? Shall I consider Table 6.8.1C?
Section 6.4.3 in general perhaps.
Section 6.5.2 certainly comes to mind as well.
Based on your description I am not sure which 6.8.1 table would apply. If none of them specifically apply then there is no minimum efficiency requirement since 90.1 does not not address it.
I would like to ask if anyone has a comment on two questions regarding the baseline model for existing buildings:
1) According to Table 3.1 from Appendix G, thermal loads due to occupancy and equipment as well as all schedules should be the same for both Baseline and Proposed models.
I concluded that the disposal of the interior areas should be common to both models (eg same areas for restrooms and offices).
Question: Should I use the proposed model to define the indoor areas distribution and replicate in baseline?
2) My existing building (before retrofit) have outside shading (brises) and there is the intention to keep this device in the new project. In accordance with G3.5.1 table:
"f. Existing Buildings: For existing buildings envelopes, the baseline building design shall reflect existing conditions prior to any revisions that are part of the scope of work being evaluated"
But the same table says I should model the baseline with no shading devices:
"5.5-1- through 5.5-8: All vertical glazing shall be assumed to be flush with the exterior wall, and no shading projections shall be modeled..."
Question: Should I ignore this last quote and include shadowing devices in the baseline model?
Further on, I contacted ASHRAE as well, and they answered me that I should look to 2013 version in order to clarify my doubt of version 2007. According toTable G.3.15:
"d. Vertical Fenestration Assemblies. Fenestration for new buildings, existing buildings, and additions shall comply with the following:
- Fenestration U-factores shall match the appropriate requirements..."
- Fenestration SHGCs shall match the appropriate...
ALL VERTICAL FENESTRATION SHALL BE ASSUMED TO BE FLUSH WITH THE EXTERIOR WALL, AND NO SHADING PROJECTIONS SHALL BE MODELED"
1. Yes the interior areas should be the same.
2. Model the baseline without any external shading. Table G3.1-5 Baseline (f) only applies to the envelop which includes insulation and windows, not external shading.
One review comments that i have received about E&Ap2 prerequisite is:
2. No exterior lighting power has been modeled for the Baseline or Proposed Case. Confirm that no exterior lighting is included in the building site or revise the models to reflect exterior lighting. Verify that the Proposed Case exterior lighting reflects the actual building design and the Baseline Case reflects the allowed lighting power from Section 9. Ensure that no credit is taken in the Proposed Case for lighting reductions on non#tradable surfaces; additional lighting power allowance cannot be claimed in the Baseline Case for surfaces that are not provided with lighting in the actual design and lighting fixtures cannot be double-counted for different exterior surfaces. Report the tradable and non#tradable surface lighting power separately (in units of Watts or Kilowatts) for both the Baseline and Proposed Case in Supplemental Table 1.4. Update the model and results to reflect exterior lighting if included in the model and is consistent with SSc8: Light Pollution Reduction.
I´m updating the Section 1.4 with new version (Jan 2014), and I have a problem with this excell (Secction 1.4):
When i input the Total Exterior Lighting Power Modeled (Watts), similar to Total Exterior Lighting Power Calculated (Watts), this cells are coloured red.
I don´t understand the reason to happen it.
Do I have to include these Kw (exterior lighting) in my Baseline and Proposed models?? Or no.
Thanks in advanced
It is likely red because it does not match the value calculated by the form. The form adds the 5% unrestricted allowance.
Yes you must include exterior lighting in the models. Note that exterior lighting is a mandatory provision so you must comply with the requirements.
My surprise is that the values are the same.
If I match the valou 0, the cells are green.
These are tradable surfaces
I've found the error.
It is an error of excell (Section 1.4)
Must impute all decimal upper cells.
I hope that they resolve this cuestion.
Here is a response from Tyler in our office who actually authored the spreadsheet.
Yeah I’ve noticed that one too, but it’s not really an error so much as an imperfect formula. It is set up so that the cell turns red if the modeled exterior lighting power does not equal the calculated allowance, but does not account for rounding. So if the allowance is actually 49.99 (which gets displayed as 50) and you enter 50, it will turn red.
We are looking at an energy model report for a Residential tower. The project was initially achieving 12% savings. Later they removed the non-regulated use items (residential light & receptacle loads) and now the project performs 15.7% better than ASHRAE.
Is this allowed per GBCI?
No you must include all of the energy use associated with the project.
The project I'm working on currently is for a production plant and office zones all in one building. There is no cooling coils in all designed system with the exception of the Dx unit in the server room.
All systems are Ventilation and heating.
The question is related to the system in the Baseline model. There are allowed heating only systems when it is for stores, stairs, technical rooms, etc. In my case however the office zones are also designed as Heating only (ventilation and aux radiator heating).
Should this be modeled in the Baseline also as the other heating only systems, regarding that it is for office areas.
You can use the heating only systems for any space type.
Thanks a lot for your reply.
There are however few more clearing questions to this issue, for which I'm not sure how to proceed.
1. Baseline system arrangement. In ASHRAE 90.1 2010 Manual (G-28) is written "For systems ...9 and 10, each floor is modeled with a separate HVAC system".
My project has two floors (46 000 sqft), but has 8 different heating system servicing various zones, which are Radiation (heating only) and ventilation DOA (also heating only).
Reading the manual, I'm considering that for Baseline I have to model 2 systems - Ventilation - heating only. Is this correct or I should model the systems as they are in the Proposed?
2. Number of Boilers, pumps. In app. G are written the conditions for these equipment, but applicable to systems 1, 5 and 7.
My project has two gas fired boilers and the whole system is based on hot water circulated by pumps.
Should I stick also to these systems (1,5,7) ?
Your support will be highly appreciated.
1. Baseline is one system per floor. Do not map the baseline systems to the proposed systems.
2. A system 9 uses a furnace, not a boiler. So the baseline would not have a boiler, pumps, etc.
Marcus you are always(?!) right. However, I would like to ask you to perhaps bring this up with the TAGLEED Technical Advisory Group (TAG): Subcommittees that consist of industry experts who assist in developing credit interpretations and technical improvements to the LEED system. if you get the chance, i.e. to allow the baseline to map to the design case. It would make things a lot easier for the simulation program TrnSys (and most others as well) on large geometery projects and makes some sense on both accuracy (especially the routing and controls) and zoning practice.
If you are of the other oppinion, I'd love to hear the reasoning from an expert such as yourself.
Jean I am frequently wrong, just ask my wife.
I am no longer on the EA TAGLEED Technical Advisory Group (TAG): Subcommittees that consist of industry experts who assist in developing credit interpretations and technical improvements to the LEED system. and the issue is embedded in Appendix G so I don't think the TAG would opt to change it.
You raise a good point. This makes sense in certain building type but does not make sense in others. 90.1-2013 has added building types and differentiates system type by climate zoneOne of five climatically distinct areas, defined by long-term weather conditions which affect the heating and cooling loads in buildings. The zones were determined according to the 45-year average (1931-1975) of the annual heating and cooling degree-days (base 65 degrees Fahrenheit). An individual building was assigned to a climate zone according to the 45-year average annual degree-days for its National Oceanic and Atmospheric Administration (NOAA) Division. instead of heating fuel. I think that as this continues to be refined hopefully they will do more differentiation by building type to address this issue.
Your issue is with the Appendix G folks, not the LEED folks I think.
We are working on a project that uses heat reclaim as a source of energy for service hot water. Heat is reclaimed from the flue gases of a generator set that is used to complement the utility grid in providing electricity since the utility doesn't provide 24/7 electricity.
How can this reclaimed heat be modeled? And is this considered CHPCombined heat and power (CHP), or cogeneration, generates both electrical power and thermal energy from a single fuel source. and to be modeled according to the document titled: "Treatment of District or Campus Thermal Energy in LEED V2 and LEED 2009 – Design & Construction"?
Yes that is CHPCombined heat and power (CHP), or cogeneration, generates both electrical power and thermal energy from a single fuel source.. In addition to the DESv2 there is guidance in CHP modeling in the Reference Guide.
Thank you for your reply Marcos.
We have indeed gone over the mentioned guidance in the reference guide and have the following query:
Case 1 "Same ownership, CHPCombined heat and power (CHP), or cogeneration, generates both electrical power and thermal energy from a single fuel source. inside building" - which is the case of our project - mentions that "electricity produced is considered free, as is the produced thermal energy";
Having 50% of electricity being produced by the generators (Utility grid only produces 50% of electricity), what is the rate charged to the proposed and baseline cases after the overall electrical energy demand has been simulated?
E.g. if we have 1000 MWh for the proposed case and 1100 MWh for the baseline case.
The calculation is done so that 500 MWh are charged according to the Utility grid rate and the other 500 MWh are considered free of charge?!
The calculation is done so that 550 MWh are charged according to the Utility grid rate and the other 550 MWh are considered free of charge?!
And according to the above rationale, where are the heat reclaim savings accounted for? Are they accounted for as reductions in the 500 MWh of the proposed? This seems a bit extreme because we will end up with very high cost savings.
Your advice is highly appreciated.
Mario, I just had the same issue with the CHPCombined heat and power (CHP), or cogeneration, generates both electrical power and thermal energy from a single fuel source. that I was working on last week and what I would do in your case is showing the calculations as 1100 MWh for the Baseline and 1000 MWh for the Proposed, then I can show the reduction in the Exceptional Calculation Method section (ECMEnergy conservation measures are installations or modifications of equipment or systems intended to reduce energy use and costs.) by addressing the cost of the fuel needed for the CHP too, so it will look like (Saving $$: 500 MWh - Cost $$: CHP fuel and accessories)
The savings are offset by adding the cost of the fuel used to produce the electricity. So the electricity is not really free even though you do not assign a cost to it as the cost is already in the fuel used to produce it.
Hi, not sure if I am missing something but the USGBC website's 'Resources' section does not have an updated section 1.4 table for LEED v4. The version on their website (Revised Section 1.4 Tables (Jan 2014)) is still based on ASHRAE 90.1 2007. Is there a version of the excel sheet that is based on ASHRAE 2010 for us to use on LEED v4 projects?
Apologies, found the document!
Further, to the preliminary review of EAp2 our project team got a comment with regard to demand control ventilation (DCV). however, although the project includes spaces larger than 500 sf, none of those ha a design occupancy of greater than 40 people per 1.000 sf of floor area. Would a notification of the occupancy not exceeding 40 people/1,000 sf be sufficient to justify why DCV is not required to our project? Thank you in advance.
That would be a start. It is always a good idea to back up your claims, statements and notifications with documentation. In this case you could point to the calculations for IEQp1. Make sure that you are not contradicting yourself in documentation submitted for another credit. Projects usually get this comment when they show a space as having 40 people per 1000 in the documentation for IEQp1 or if there is a large gathering space in the project like an auditorium where this density is likely at peak ventilation requirements.
Thank you Marcus. We are not contradicting ourselves with IEQp1 since no space exceeds the threshold (40pax/1,000sf). Although there is an auditorium in the project, occupancy will be still lower than 40pax/1,000sf.
However, although DCV is not required (based on not exceeding the occupancy threshold) all large areas (>500sf) of our project are equipped with carbon dioxide sensors allowing for demand control ventilation.
Perhaps the reviewer saw the auditorium and this is why they raised the question. State that the auditorium is under 40/1000 and provide the max occupancy and total square footage for that (and any similar) spaces in your response.
Hi Marcus etEvapotranspiration (ET) is the loss of water by evaporation from the soil and by transpiration from plants. It is expressed in millimeters per unit of time. al.,
I received a question from one of our project energy modelers that I cannot answer -
Recently we have been receiving a new comment on EAp2 that states
“The HVAC equipment capacities cannot be autosized in the Proposed model.”
This comment brings up the following concerns. Our actual design documents include engineering of the building, safety factors, owner desired extra capacities, & good engineering practices for operation & functionality. If we are to put in the true design capacities (which are peak capacities plus safety factors not average operating conditions) but allow the baseline to auto calculate, we are never going to show energy savings as the baseline has none of the previously mentioned included. The baseline is bare bones and as minimal as one can get. Are we allowed to also put in the design capacities in for the baseline? For example, in past experience, the baseline requires more airflow because the equipment is a little less efficient and the envelope typically has a lower R value & better glazing than the proposed. However, if we have to hard input our design Peak airflows but allow the baseline to calculate airflows there will be skewed results. The reason I say this is that in general an interior room may require 50 CFM to meet its load. However, we know that diffusersIn an HVAC context, diffusers disperse heating, cooling, or ventilation air as it enters a room, ideally preventing uncomfortable direct currents and in many cases, reducing energy costs and improving indoor air quality (IAQ). In light fixtures, diffusers filter and disperse light. need a minimum of 75-100 CFM for the air to actually reach the occupant and effectively cool the space. Therefore, our design would show 100 CFM and the baseline model would calculate 50 CFM. This does not seem like a fair and true comparison.
Can you offer insight and direction for how to adjust our model to address the reviewer concerns while still showing energy cost savings and reflecting our actual design conditions?
My two cents... Appendix G is pretty clear that if you have completed design documents, you cannot auto-size the proposed case, and you must model the HVAC system "as designed" including the scheduled capacities. Remember, the baseline capacities are to be over-sized by 15% for cooling and 25% for heating, so that should help make up for a little "over-engineering" on the proposed case.
You should still be able to squeeze some points out even with these restrictions. I've found the baseline systems pretty much always have lower airflows, but in the end the proposed systems are usually still more efficient and use less overall energy than the baseline theoretical systems.
Safety factors and "good engineering practice" enter a grey area of violating the energy code and engineering in extra capacity isn't really "green" and being green is the whole point; getting the certification is just a bonus.
Agreed. If you oversize the Proposed systems to any significant degree you should pay a penalty. The software will calculate peaks and average based on the actual loads so you are not really comparing average to peak. You enter the full capacity and the software automatically matches the capacity needed to the loads in both models.
This issue brings a question to my mind. The multifamily building that I am working at right now has some unconditioned (no cooling) spaces and according to Appx.G I should model these spaces identically with the baseline. I am wondering if I will ever receive a comment from the reviewer about some proposed systems being (auto-sized) and being (15% over-sized).
The reviewer will check the proposed system capacities against the information in the mechanical schedules to ensure that the proposed is modeled as designed. If they are only slightly off you should not get a comment however.
There are times when auto-sizing proposed systems is appropriate. Like when you have to model a space that does not have a mechanical design identically to the baseline system.
What is the threshold that the reviewer consider reasonable in terms of capacities and airflows? 10%?
For capacities and airflows I would say under 10%. For fan power it should be identical or explained.
A radiant tube gas can be associated with the table 6.8.1E ASHRAE 2007?
Gas radiant heaters are not covered in the 6.8.1 Tables. So there is no minimum efficiency requirement.
I am working on a dining facility where we have two makeup air units serving the kitchen hoods. The units in the proposed case are equipped with chilled water coils served with the building air cooled chiller to tamper the air to 80 degree F. the units are considered as process and are supposed to be modeled identical in the proposed and the baseline case. Since the building chiller is a high performance magnetic chiller serving the whole building what is the baseline piece of equipment that needs to be modeled to serve the makeup units since the baseline system is type 3 dx packaged units.
Is it an air cooled chiller with ASHRAE 90.1 performance and sized for the coils capacity?
Any guidance would be appreciated. Thanks.
One way of thinking about this (I am be wrong) is that perhaps the makeup units are not classed as process energy if they have chilled water coils as they are conditioning the space. However the outside ventilation rates should be the same in both building so the baseline building would also need to makeup this air. If the baseline system is type 3 DX packaged units, then this serves the space but with the outside air rate to match the proposed building (E.g. there will be a constant outside air during times the makeup unit is in operating in the proposed at that rate).
Anyone have any other thoughts? I have come across similar tricky situations with makeup air in buildings.
The kitchen makeup units are serving 80% of the hood required makeup the rest is coming from the building system and are not really conditioning the space. The only reason the air is tempered to 80F is for the cooks safety purpose and RFP requirement. All the hoods ventilation system is for kitchen heat and smoke removal. Therefore I believe that it is process, (correct me if I am wrong).
My question is that if it is process how will it be modeled in the base line and what type of equipment will be modeled for the chilled water coils. Since the base line model does not have a chilled water system.
I guess the only way is to compare it to a chiller with ASHRAE 90.1 performance and claim savings.
Anyone had this situation?
Two options come to mind.
One - model a little mini-chiller identical to the Proposed in the Baseline. This may present some major issues in certain software.
Two - calculate the overall seasonal system efficiency for the Proposed chilled water system (pumps, etc.) and apply that to a DX system with a flat curve.
Since it is process you can only claim savings through an exceptional calculation. Section 188.8.131.52 prohibits the use of cooling in kitchen make-up air hoods over 5000 cfm. If that is the case then the proposed should be modeled as designed and the baseline should be modeled without any cooling.
ASHRAE 90.1 section 184.108.40.206 allows the cooling or heating in kitchen make-up hoods under the Two exceptions a and b and almost all engineered hoods will meet exception b. we are in such hot and humid climate that it is almost becoming a requirement to provide some sort of cooling thru the make-up to provide some comfort in the kitchen. That said. If I am claiming saving thru exceptional calculations. Can I model the baseline make up with a chiller that meets the minimum requirement of 90.1 or am I missing something.
You could use one of the two methods mentioned above but substitute the a similar type of chiller's efficiency from 90.1 as the baseline. Makes sense to us as a reasonable rationale for the baseline.
We have a project that consists of 1 level of retail, 7 levels of above grade parking, 8 levels of commercial office space, and 16 levels of residential (apartment) space. Based on overall building square footage, the baseline energy model would utilize System 7 – VAVVariable Air Volume (VAV) is an HVAC conservation feature that supplies varying quantities of conditioned (heated or cooled) air to different parts of a building according to the heating and cooling needs of those specific areas. with Reheat. However, under normal circumstances, if the building was 100% residential the baseline would use System 1- PTAC. It could also be argued that because the office space is an 8am-5pm occupancy and the residential space is 24/7 that exception G3.1.1.b could be used to model each residential unit as an individual thermal zone with a packaged rooftop unit. How can we determine how the baseline should be set up? Any guidance would be appreciated. Thanks.
Assuming the parking is unconditioned it does not enter into the equation at all. The residential is a system 1 and is predominant. Exception "a" then applies since the other uses are nonresidential. The 8 office floors and 1 retail floor are still greater than 5 floors so they are a system 7. Not sure if the retail would meet any of the other exceptions.
I'm modeling a manufacturing plant. The issues I'm looking for advises are related to modeling the manufacturing process and specifically:
Cooling. There are several molding presses, which are cooled with cold water via their cooling shell (closed loop). The cold water is provided by two air cooled chillers having the total capacity of 128 tons. The chillers are designed to operate with an integrated free cooling package whenever the weather allows it.
The questions are:
1. How could this cooling system be assigned to any of the app. G3.1 table. The building as a whole (area, floors..) belongs to System 5, but I'm not sure how to actually proceed - may be exceptional calculation method?
2. In case the cooling system should be identical for Proposed and Baseline (industrial process), should the free cooling option also to be applied to the Baseline model or there should be just an air cooled chiller. The presumption is that the Proposed building is investing more for increasing the energy efficiency.
This cooling is a process load.
1. Table G3.1.1A does not apply. You must model this process identically in the Baseline unless you are trying to claim savings. If you are trying to claim savings then follow the exceptional calculation method.
2. You would need to justify any savings association with the free cooling as an exceptional calculation. A narrative should describe all Baseline and Proposed case assumptions included for this measure as well as the calculation methodology used to determine the projected savings. The narrative and energy savings should be reported separately from the other efficiency measures in Section 1.7 - Table EAp2-7. The Baseline case description should verify that the efficiency measure is not standard practice for a similar newly constructed facility. Baseline justification must be provided by referencing a recently published document (published within five years of the project registration date), utility program that incentivizes the equipment installed, or by documenting systems used to perform the same function in other newly constructed facilities (three facilities built within the past five years of the project registration date). Savings associated with the proposed case measure should also be justified with published or monitored data.
Markus, thanks again for your answer.
For this particular project I've not been provided with any data of the manufacturing equipment (molding press), so I can't make any exceptional calculation for it. In one previous project I've been receiving such data and when I've made there the exceptional calculation as explained by you, I've received the reviewr's approval.
But here I'm asking only about the way of organizing the cold water supply.
In principle there are standart cooling options - air cooled chiller or water cooled with a cooling tower. In this case it was selected one of these typical solution, but with one extra - free cooling option.
If I make an exceptional calculation method just for this cooling part by comparing a standart air cooled chiller with an air cooled with free cooling, will this be accepted?
If not, then all process loads will be identical. So , again my question is just for the cooling.
If it were me I would tell my client that I cannot complete the model without data on the equipment.
If you try to claim savings for a component of a system but you do not have any real basis for that system I would certainly not accept it. The Baseline must be well defined and in this case you are making a big assumption.
If you make it identical it should be accepted.
Thanks for the reply, Markus.
I have the data of the manufacturing equipment, but the client didn't provide data that he has purchased equipment which is different from the standart practice regardless how many time I've mentioned about it. Even quoting my previous project where such approach was approved.
The cooling option was reported to me as a free coise, which are to be made by client's specialists, base on the climate zoneOne of five climatically distinct areas, defined by long-term weather conditions which affect the heating and cooling loads in buildings. The zones were determined according to the 45-year average (1931-1975) of the annual heating and cooling degree-days (base 65 degrees Fahrenheit). An individual building was assigned to a climate zone according to the 45-year average annual degree-days for its National Oceanic and Atmospheric Administration (NOAA) Division. analysis. So their final decision was to an air cooled chiller with free cooling pacage.
Modeling everything identical is not a problem, I've been just thinking whether it desrves a trial for cooling exceptional calculation, but as you say that it will not be accepted, then better save time in this issue,
So again if you can define the baseline within an exceptional calculation method you can certainly pursue it. You will need to make the case for a baseline. Perhaps the manufacturer can help you with that instead of the client.
I have couple of questions about filling table 1.4.7:
1- Table 1.4.7A asks for the total cooling capacity, I use HAP 4.6 and the cooling capacities are calculated according to ASHRAE 90.1. Shall I run the simulation and then get the output results?
2- Table 1.4.7B, I am not sure of some system inputs yet in the proposed model, so I use ASHRAE 90.1 and let the software calculate. Shall I fill the table with the software results? Will it still be accepted although it is mentioned that all inputs should be consistent with the Proposed energy model andthe mechanical drawings and equipment schedules submitted to LEED ONLINE.
Note: HAP output cooling capacities are away smaller than my actual equipments capacities used in the Proposed model. Will I receive a comment on this?
1. Yes, the cooling capacity HAP calculated would be the input.
2.You should be virtually certain about the inputs for your proposed model before you do the final model for LEED. The software should not auto-size anything. Whether it will be questioned depends on the degree to which the input variable is off and which particular input is in question. If the system capacity is slightly off it should be fine. If the fan power is way off it will be questioned.
Note. If they are way smaller then it will probably be questioned.
Always model the Proposed as designed. Do not auto-size anything.
We are working on a warehouse project with small attached administration building. I have a question regarding reference systems for this project. The warehouse building has floor heating and exhaust fans (outdoor air is supplied naturally via loading gates; there's no cooling system). Administration building (which is smaller than 1900sqm) has a separate HVAC system (AHUs and VRF system).
1. According to table G3.1.1A the reference system for the warehouse (predominant condition) should be system 7. However there are no supply fans in the proposed case so I'm not sure if we should include them in the reference model?
2. Since the administration office is smaller than 1900sqm exception a) of section G3.1.1 doesn't apply. In that case since there are different occupancy and loads schedules than in the warehouse we assumed that exception b) should be implemented and system 4 should be modeled (electric heating in the administartion building), is that correct?
To avoid some of the "rules" around heating only systems I would apply Addendum dn and model the warehouse as a system 9 or 10. Then apply exception b to the office.
Thank you Marcus. I checked Addendum dn and as you mentioned system 11 would be most appropriate for the warehouse. If I understood it well, this system should be modeled as packaged rooftop with warm air furnance? And I have one more question regarding fans in this reference system:
1. In the proposed case there are only exhaust fans (outdoor air is supplied naturally via loading gates). Should the fans in the reference be simulated identically as in the proposed case or should the energy usage of the reference fans be calculated based on ASHRAE guidelines (power of fans calculated based on pressure drop only for exhaust airflow control devices)?
The addendum mislabels the system numbers. If you look in 90.1-2010 they are labeled system 9 and 10.
ASHRAE 90.1-2010 defines System Type 9 as a constant volume warm air furnace, gas fired, with no cooling. System Type 10 is defined as a constant volume warm air furnace, electric resistance. The Baseline efficiencies for these systems should be determined based on ASHRAE 90.1-2007 Table 6.8.1E.
Baseline system air flow rates for System Types 9 and 10 shall be determined based on the temperature differential between 105 degrees F and the design space heating temperature setpoint, the minimum outdoor air flow rate, or the air flow rate required to meet applicable code or accreditation standards, whichever is greater. The fan power for System Type 9 or 10 should be 0.3 Watts per cfm of Baseline heating supply airflow.
Should the system include a fan to provide non-mechanical cooling (i.e. increased fan air flow rates set to operate once indoor or outdoor temperature exceed a certain temperature, or direct or indirect evaporative cooling), the Baseline model should also include a separate fan to provide non-mechanical cooling, sized and controlled the same as the Proposed design. For non-mechanical cooling fans, the Baseline fan power should be modeled as 0.054 Watts per cfm of non-mechanical cooling airflow.
The Green Engineer, LLP
EAc1 relies directly on the EAp2 documentation, and the strategies to earn the prerequisite are often similar to earning points under the credit.
Limits on interior and exterior light use can help in reducing energy loads.
Daylighting reduces demand on installation and use of lighting fixtures resulting in energy use. To full realize the energy benefits, contorl electrical lighting with daylight sensors.
Commissioning of energy-efficient building systems helps realize he operational benefits of the design.
Onsite renewable energy contributes to prerequisite achievement if pursuing energy modeling under Option 1.
The computer model developed for EAp2 – Option 1 is used in the M&V plan.
Do you know which LEED credits have the most LEED Interpretations and addenda, and which have none? The Missing Manual does. Check here first to see where you need to update yourself, and share the link with your team.
LEEDuser members get it free >
LEEDuser is produced by BuildingGreen, Inc., with YR&G authoring most of the original content. LEEDuser enjoys ongoing collaboration with USGBC. Read more about our team
Copyright 2015 – BuildingGreen, Inc.